- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 08 Jul 2019
Drainage is the artificial removal of water, both surface and sub-surface. Drainage is often a major element of civil engineering and construction projects and is necessary to avoid flooding and other damage.
This is effluent contaminated by domestic or trade waste. Foul (or waste) water relates to effluent from sinks and basins which does not contain excreta. Soil water relates to effluent from water closets, toilets and urinals which does.
Subsoil and surface water are considered to be clean and can be discharged into an approved watercourse (e.g. river or lake), or soakaway without treatment. Permission is required from the relevant authority or owner before discharging. Foul and soil water must be conveyed by sewer to a treatment plant before being discharged into a watercourse.
Subsoil drainage can be used to improve ground stability, to lower the moisture content of a site, to enhance horticultural properties for landscaping and so on. It can be required to drain the whole site or to protect a particular part.
According to the Approved Document C of the Building Regulations, subsoil drainage should be provided to avoid the passage of ground moisture into a building’s interior or to prevent damage being caused to the building’s fabric.
Subsoil drainage is generally involves the use of pipes that are porous to allow subsoil water to pass through the pipe body, or pipes that are perforated with a series of holes in the lower half to allow subsoil water to rise into the pipe. Both types are generally laid dry jointed in a trench filled with rubble. A pervious membrane is generally placed on top of the rubble as a filter mat, then covered with normal backfill and topped with 150 mm of topsoil.
This type of groundwater control is only feasible up to a depth of 1.5 m, and any further lowering of the water table should be achieved by other methods. For more information, see Groundwater control in urban areas.
 Surface water drainage
It is a requirement of Building Regulation’s Approved Document H that adequate provision is made for rainwater to be carried from the roof of buildings. To achieve this, roofs must be designed with a suitable fall towards either a surface water collection channel or gutter that conveys surface water to vertical rainwater pipes, which in turn connect the discharge to the drainage system.
 Rainwater installation
Drainage from roofs is generally provided by internal rainwater outlets and downpipes, or by external guttering systems or hoppers. It is recommended that there are at least two drainage points, even if the roof is small, to mitigate against one of them becoming blocked.
Drainage must be arranged so as to avoid causing dampness or damage to the building. If the rainwater pipe is fitted internally it must have leak proof joints. If external, the roofing should prevent water being blown into the eaves by extending into and below the top of the gutter.
- Directly connected to a drain discharging into a soakaway.
- Directly connected to a drain discharging into a surface water sewer.
- Indirectly connected to a drain via a trapped gully if the drain discharges into a combined sewer.
Traditionally, domestic eaves gutters and rainwater pipes were made using cast iron, although uPVC systems are increasingly common due to ease of installation and low maintenance requirements. As long as adequate size, strength and durability can be assured, they can also be made of aluminium alloy, galvanised steel, stainless steel and so on.
 Yard gully collection
A paved area near a building is laid to falls of 1:60 towards a gully. The type of area being drained and the shape of the paved area will determine the size and number of gullies. The maximum paved area per gully should be 400 sq. m. If it is connected to a combined sewer, the yard gully should be trapped with a minimum 50 mm water seal.
 Channel connection
- Half-round glazed clayware channel: Either open or with a grating cover.
- Precast concrete channel blocks: With a continuous slot down the centre of the top.
- Precast or in situ concrete box channel: With a cast iron square mesh grating.
The construction of roads affects the natural surface and subsurface drainage pattern of watersheds or hill-slopes. The provision of adequate drainage is important to prevent the accumulation of excess water or moisture on or within road constructions that can adversely affect their material properties, compromise overall stability and affect driver safety. Drainage must cope with water from the carriageways, hard shoulders, foot/cycle paths, verges, and adjacent catchment areas.
For more information, see Highway drainage.
Sustainable urban drainage systems (SUDS) can provide an alternative to, or addition to, traditional drainage systems. They mimic 'natural' drainage by adopting techniques to deal with surface water runoff locally, through collection, storage, and cleaning before allowing it to be released slowly back into the environment.
For more information, see Sustainable urban drainage systems.
 Related articles on Designing Buildings Wiki
- Air admittance valve.
- Approved Document H.
- BSRIA launches Offsite Construction for Building Services topic guide.
- Difference between drains and sewers.
- Drainage stack.
- Fabricated drainage stacks.
- Grease management.
- Groundwater control in urban areas.
- Highway drainage.
- Private sewer.
- Public sewer.
- Pumps and dewatering equipment.
- Rain gutter.
- Rainwater downpipe.
- Rainwater harvesting.
- Safe working in drains and sewers.
- Secondary ventilation stacks in tall buildings.
- Septic tank.
- Sewer construction.
- Soil vent pipe.
- SuDS - is there light at the end of the tunnel?
- Sustainable urban drainage systems SUDS.
- Waste water.
- Water engineering.
- Water transfers and interconnections.
 External resources
Featured articles and news
The Ocean Cleanup project
The various types of bond and when they are used.
It's vital the industry responds to proposals for reform of the safety regulatory system.
RSHP's Merano wins RIBA accolade.
How to differentiate between partial possession and early use.
Ofwat proposes £12 billion additional investment and £50 bill reductions.
Avoiding 'winner's curse' and other useful info.
Developing test methods for video flame/smoke detectors
Waiting for a new deal ...but will funding materialise?
Our servers have reached another milestone. Why not write an article and be seen by our 6.5 million users.
RSHP celebrates competition win in Paris.
All about approved inspectors.