- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 12 Nov 2020
Air admittance valve
Drainage systems in buildings must be vented to allow the escape of gases and odours, to allow the release of pressure in front of flowing waste and to allow air to re-enter the system following the passage of waste.
This can be achieved by connecting waste pipes to a soil vent stack (SVP). SVPs are often seen running vertically on the outside of domestic properties, and have an open vent above eaves level allowing air into and out of the system without odours or gases causing nuisance. For more information see: Soil vent stack.
This may be necessary for example when new appliances are installed in an existing building and there is no clear route to the SVP, to close washing machine standpipes, for island units, to reduce the amount of pipework penetrating the roof or walls of a building and so on.
Air admittance valves open to allow air into the system when there is negative pressure, and close under positive pressure preventing gasses from entering the building. This maintains trap seals and siphons within the system, but does not relieve positive pressure.
- They comply with BS EN 12380:2002: Air admittance valves for drainage systems. Requirements, test methods and valuation of conformity.
- They do not adversely affect the amount of ventilation necessary for below ground sewers.
- They are located in areas with adequate ventilation.
- They have clear access for maintenance and for the removal of blockages.
- They are not used outside or in dust laden atmospheres.
- Where there is no open vent on the system or connected drains, alternative arrangements are made to relieve positive pressures (as air admittance valves only relieve negative pressure, not positive pressure).
NB When installing drainage and ventilation pipework in high-rise buildings, traditional design standards dictate that a secondary ventilation stack is used to overcome air pressure changes. However, products such as the Polypipe Terrain P.A.P.A® and Pleura valves are a proven alternative. The P.A.P.A® (positive air pressure attenuation) valve is designed to react to and attenuate positive pressure transience within the drainage stack of high-rise developments providing a suitable venting solution for any multi-storey building.
 Related articles on Designing Buildings Wiki
Featured articles and news
Six technologies guiding O&M into the future.
Homes carved from sandstone cliffs in England.
A review of the HES pilot project.
Organisation alerts membership to findings of IHBC research.
Four outstanding professionals recognised.
Sustainable flooring from super strong grass.
Organisation presents reactions from industry leaders.
New infrastructure bank to be based in the North of England.
Fairer, faster, greener. A summary of the key points.
Strategies to help provide safer working conditions.
Protecting flora, fauna and the other natural features of Scotland.
Architecture considered somewhere between 'sublime and beautiful'.
Polish piano factory revived through an energy-oriented tune up.