To help develop this article, click 'Edit this article' above.
Fire dampers are devices designed to impede the spread of fire through walls, floors and partitions. The term 'fire damper' is defined by Approved document B, Fire Safety, Volume 2, Buildings other than dwellinghouses, as a:
'Mechanical or intumescent device within a duct or ventilation opening which is operated automatically and is designed to prevent the passage of fire and which is capable of achieving an integrity E classification and/or an ES classification to BS EN13501-3:2005 when tested to BS EN1366-2:1999. Intumescent fire dampers may be tested to ISO 10294-5.'
Fire dampers are installed in the ducts of heating, ventilation and air conditioning systems which penetrate fire-resistant constructions and will automatically close on the detection of heat. Typically, a thermal element will melt and allow springs to close the damper, which will stop the fire from migrating into an adjoining compartment (ref AMCA 2011).
Smoke dampers are designed to prevent the flow of smoke and products of combustion, and fire and smoke dampers combine both functions. Smoke dampers and combined dampers are generally resettable, and are operated electronically by smoke and fire detectors, as smoke may be present even where temperatures are not elevated.
From 1 July 2013 it became a requirement under the Construction Products Regulation for all new fire and smoke dampers used in UK buildings to be CE-marked to indicate product compliance (ref CIBSE Journal). This recognises the testing standard BS EN 1366 – Fire resistance tests for service installations, which contains test procedures which ensure dampers are installed appropriately.
 Types of fire dampers
There are three main types of fire dampers:
- Curtain fire dampers which include a folded curtain held at the top by a thermal element.
- Intumescent fire dampers which contain elements that expand when heated.
- Single and multi-blade fire dampers which pivot when released.
 Managing the installation
Ensuring effective fire damping requires careful design, specification and installation, with care taken to ensure penetrations are properly formed and dampers are properly sealed. Systems should be inspected and tested regularly and this requires that proper access is provided in the building design.
The principal designer and principal contractor have a role in ensuring the proper design and installation of fire dampers, and installations will be subject to approval under the Building Regulations.
 Related articles on Designing Buildings Wiki
- Approved Documents.
- Building Regulations.
- CDM Regulations.
- CE marking.
- Construction Products Regulation.
- Dry riser.
- Fire and rescue service.
- Fire detection and alarm systems.
- Fire protection engineering.
- Fire resistance.
- Fire safety design.
- Joint fire code.
- Smoke detector.
- Wet riser.
 External references
Featured articles and news
We've analysed 6 million pieces of data to reveal that the knowledge framework underpinning the construction industry is no longer fit for purpose.
ICE examine just how close we are to providing subsidy-free low carbon electricity.
Have a look at MAD Architects' design proposal for renovating Montparnasse Tower into a concave mirror.
This article examines the legal issues behind off-site goods and materials.
Read about how technology is changing the real estate industry.
BRE Global introduce the first registration scheme for Suitably Qualified Security Specialists.
An introductory article to the different types of building foundations.
This unique Brutalist-era car park just off Oxford Street is soon to be demolished.
How to utilise technology in construction projects and what benefits will it bring?
Have a look at Thomas Heatherwick's new building, one he calls 'the tubiest in the world'.
Artificial intelligence will have a significant impact on the built environment, according to a new survey by ICE.
Construction is often seen as too traditional, lacking innovation and collaboration. But are these perceptions fair?