- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 26 Feb 2019
- Prevents the rapid spread of fire which could trap the occupants of a building.
- Reduces the likelihood of fires growing and creating a danger to occupants, fire and rescue services, and people in the vicinity of the building.
- Limits the damage caused to a building and its contents.
Compartment floors are required to provide a minimum degree of fire resistance as set out in Appendix A of Approved document B2 and Appendix A of Approved document B1 (for dwellinghouses). This fire resistance is generally expressed in terms of the number of minutes of resistance that must be provided. Methods for testing fire resistance are set out in BS 476 Fire tests.
Joints between compartment floors should be fire-stopped to maintain the continuity of resistance; and openings for timber beams, joists, purlins and rafters, and pipes, ducts, conduits or cables that pass through any part of a compartment floor should be kept as few in number as possible, kept as small as practicable; and should be fire-stopped. See Fire stopping for more information.
 Related articles on Designing Buildings Wiki
Featured articles and news
Five things to consider before installing solar panels.
New conservation building for the Louvre completed.
A balance between character and climate.
Bamboo pavilion built at London South Bank Uni.
Bringing in an expert.
Why the lowest price isn't sustainable.
The Most Economically Advantageous Tender.
Pipe dream or possibility?
The New Rules of Measurement.
Prioritising Sustainable Development Goals on projects.