- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 26 Feb 2019
- Prevents the rapid spread of fire which could trap the occupants of a building.
- Reduces the likelihood of fires growing and creating a danger to occupants, fire and rescue services, and people in the vicinity of the building.
- Limits the damage caused to a building and its contents.
Compartment floors are required to provide a minimum degree of fire resistance as set out in Appendix A of Approved document B2 and Appendix A of Approved document B1 (for dwellinghouses). This fire resistance is generally expressed in terms of the number of minutes of resistance that must be provided. Methods for testing fire resistance are set out in BS 476 Fire tests.
Joints between compartment floors should be fire-stopped to maintain the continuity of resistance; and openings for timber beams, joists, purlins and rafters, and pipes, ducts, conduits or cables that pass through any part of a compartment floor should be kept as few in number as possible, kept as small as practicable; and should be fire-stopped. See Fire stopping for more information.
 Related articles on Designing Buildings Wiki
Featured articles and news
The initiative to enhance the environment continues.
Could underused community spaces offer an alternative to working from home?
Keeping workers and workplaces safe in the United States.
A history lesson in geographic information systems.
A low tech, easy to use method of extinguishing small fires.
How can these valued spaces be reused?
Partnership avoids the need for listed building consent.
Connecting building design from inception to completion to operations.
Gregor Harvie predicts interoperability will be construction’s Uber moment.
Expert commentary and insight.
Guidance offered for stained glass window maintenance.
Define need before determining viability.