- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 26 Feb 2019
- Prevents the rapid spread of fire which could trap the occupants of a building.
- Reduces the likelihood of fires growing and creating a danger to occupants, fire and rescue services, and people in the vicinity of the building.
- Limits the damage caused to a building and its contents.
Compartment floors are required to provide a minimum degree of fire resistance as set out in Appendix A of Approved document B2 and Appendix A of Approved document B1 (for dwellinghouses). This fire resistance is generally expressed in terms of the number of minutes of resistance that must be provided. Methods for testing fire resistance are set out in BS 476 Fire tests.
Joints between compartment floors should be fire-stopped to maintain the continuity of resistance; and openings for timber beams, joists, purlins and rafters, and pipes, ducts, conduits or cables that pass through any part of a compartment floor should be kept as few in number as possible, kept as small as practicable; and should be fire-stopped. See Fire stopping for more information.
 Related articles on Designing Buildings Wiki
Featured articles and news
New editor covered facilities management, operations and construction in the US.
Exclusive log cabins on the North Antrim coastline.
Proactive forestry for strategic water management.
CIOB urges construction to share PPE with healthcare providers.
Why not write that article you've always meant to?
One of the seven man-made wonders of Arizona.
A more flexible approach is needed.
A quick step-by-step introduction to the BREEAM process.
First pioneered in the USA and then France.
The European BACS market has been showing signs of growth.
Free ICE publication for World Water Day.