- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 08 Aug 2018
The spread of fire can be restricted by sub-dividing buildings into a number of discrete compartments. These fire compartments are separated from one another by compartment walls and compartment floors made of a fire-resisting construction which hinders the spread of fire.
Approved document J, Combustion appliances and fuel storage systems, defines a fire compartment as:
‘… a building or part of a building comprising one or more rooms, spaces or storeys constructed to prevent the spread of fire to or from another part of the same building or an adjoining building. (A roof-space above the top storey of a fire compartment is included in that fire compartment.) A separated part of a building is a form of compartmentation in which part of a building is separated from another part of the same building by a compartment wall. Such walls run the full height of the part and are in one vertical plane.’
- Prevents the immediate spread of fire which could trap the occupants of a building.
- Reduces the chance of fires growing and creating a danger to occupants, fire and rescue services, and people in the vicinity of the building.
- Limits the damage caused to a building and its contents.
The degree of sub-division that should be provided by fire compartmentation will be dependent on:
- The use of the building.
- The fire load in the building.
- The height of the building.
- The availability of a sprinkler system.
The maximum permissible dimensions of fire compartments (for buildings other than dwellings) are set out in Table 12 of Approved document B2, Fire Safety, Buildings other than dwellinghouses.
Compartment walls and compartment floors form a complete barrier between fire compartments and are required to provide a minimum degree of fire resistance as set out in Appendix A of Approved document B2 and Appendix A of Approved document B1 (for dwellinghouses). This fire resistance is generally expressed in terms of the number of minutes of resistance that must be provided by different parts of a building. Methods for testing fire resistance are set out in BS 476 Fire tests.
Joints between fire-separating elements such as compartment walls or floors, should be fire-stopped to maintain the continuity of resistance; and openings for timber beams, joists, purlins and rafters, and pipes, ducts, conduits or cables that pass through any part of a fire-separating element should be kept as few in number as possible, kept as small as practicable; and should be fire-stopped.
Approved document B, defines a fire stop as: ‘A seal provided to close an imperfection of fit or design tolerance between elements or components, to restrict the passage of fire and smoke.' See Fire stopping for more information.
Fire dampers are installed in the ducts of heating, ventilation and air conditioning systems which penetrate fire-resistant constructions and will automatically close on the detection of heat. See Fire damper for more information.
There are a number of additional requirements depending on the type of building, for example:
- Parts of a building that are occupied for different purposes should generally be separated from one another by compartment walls and compartment floors.
- Walls common to two or more buildings should be constructed as compartment walls.
- Compartment walls in the top storey beneath a roof should be continued through the roof space.
- Walls separating semi-detached houses or terraced houses must be compartment walls.
- Garages should be separated from attached houses by compartment walls and compartment floors.
- There are additional requirements for; flats, institutional buildings, other residential buildings and non-residential buildings.
 Find out more
 Related articles on Designing Buildings Wiki
- Approved Document J.
- Cavity barrier.
- Compartment floor.
- Dry riser.
- Escape route.
- External fire spread, Supplementary guidance to BR 187 incorporating probabilistic and time-based approaches.
- Fire and rescue service.
- Fire damper.
- Fire detection and alarm systems.
- Fire resistance.
- Fire risk assessments and historic buildings.
- Fire safety design.
- Fire-separating element.
- Firefighting lift.
- Firefighting route.
- Installing fire doors and doorsets (GG 86).
- Joint fire code.
- Means of escape.
- Protected escape route.
- Protected stairway.
- Thermal zone.
- Unprotected escape route.
- Wet riser.
Featured articles and news
When is there a right to light, and what happens if it is obstructed?
What would the nationalisation of economic infrastructure mean for GB?
A new guide to improving value by reducing design error.
We've reached 80,000 page views a day and 10,000 registered users. Why not join them?
A masterplan is a framework within which a location is encouraged to develop or change. Read our introductory article.
New consultation announced on a specialist Housing Court to settle landlord-tenant disputes.
ICE responds to a transport consultation advising the government to make decisions enabling more inclusive cities.
BRE and Loughborough University complete first phase refurbishment of demonstration home.
How the risk of collapse of fibrous plaster ceilings is being addressed in theatres.
If you’re a great writer and have practical experience of the construction industry, it could be you.
Frustrated by long documents or technical jargon? Put off by sign-up forms or costs? Take this 5 min survey to help improve construction knowledge.