Protected escape route
To help develop this article, click ‘Edit this article’ above.
‘...that part of the means of escape from any point in a building to a final exit’, where a final exit is, ‘The termination of an escape route from a building giving direct access to a street, passageway, walkway or open space and sited to ensure the rapid dispersal of persons from the vicinity of a building so that they are no longer in danger from fire and/or smoke.’
Escape routes can be protected or unprotected, where an unprotected escape routes is the unprotected part of an escape route, ‘…which a person has to traverse before reaching either the safety of a final exit or the comparative safety of a protected escape route, i.e. a protected corridor or protected stairway.'
A protected stairways is, ‘...designed to provide virtually ‘fire sterile’ areas which lead to places of safety outside the building. Once inside a protected stairway, a person can be considered to be safe from immediate danger from flame and smoke. They can then proceed to a place of safety at their own pace. To enable this to be done, flames, smoke and gases must be excluded from these escape routes, as far as is reasonably possible, by fire-resisting structures or by an appropriate smoke control system, or by a combination of both these methods. This does not preclude the use of unprotected stairs for day-to-day circulation, but they can only play a very limited role in terms of means of escape due to their vulnerability in fire situations.'
- A protected entrance hall/landing is, ‘A circulation area consisting of a hall or space in a flat, enclosed with fire-resisting construction (other than any part which is an external wall of a building).
- A protected shaft is, ‘A shaft which enables persons, air or objects to pass from one compartment to another and which is enclosed with fire-resisting construction.’
 Related articles on Designing Buildings Wiki
- Automatic release mechanism.
- Escape route.
- Fire compartment.
- Fire detection and alarm systems.
- Fire door.
- Fire Door Inspection Scheme.
- Fire protection engineering.
- Fire resistance.
- Firefighting lift.
- Firefighting route.
- Firefighting shaft.
- Inner room.
- Installing fire doors and doorsets (GG 86).
- Protected stairway.
- Separating floor.
- The Regulatory Reform (Fire Safety) Order 2005.
- Unprotected escape route.
- Visual alarm devices - their effectiveness in warning of fire.
Featured articles and news
Have a look at some of the most impressive concert stage designs of all time, including Pink Floyd, U2, Rolling Stones, and more...
What is the Home Quality Mark? Find out how it can help you when buying/renting a new home.
Business Secretary launches £246m Faraday Challenge to establish UK as world leader in battery technology.
Government announces new plans for regulations to improve safety and security awareness of drone users.
Read our introductory article to the various different types of fuel.
IHBC book review: Charles Barry’s monumental struggle to rebuild the Houses of Parliament.
Read about RSHP's British Museum extension which has been shortlisted for the 2017 Stirling Prize.
Read our introductory article to building a house extension.
More updates from DCMS about the large-scale testing of cladding systems and the number of buildings affected.
UandI secure resolution to grant planning consent for major new regeneration project.
IHBC article considers how heritage is dealt with when infrastructure schemes are authorised.
It was the tallest structure in the world for 3,800 years, but to this day the exact construction techniques are a mystery.
Shortlist for the industry's most coveted award announced.