Visual alarm devices - their effectiveness in warning of fire
Research by BRE looked at the effectiveness of visual alarm devices in warning building occupants of fire.
The research compared the responses of a group of participants to flashing Xenon and LED devices of varying pulse durations. One Xenon device, three cool white LED devices (of 40, 20 and 10 millisecond (ms) pulse durations) and two warm white LED devices (of 40 and 20ms pulse durations) were used.
The flashing signals were presented individually to 96 participants who were seated in front of a screen and occupied with a written task. The tests were performed in high and low ambient light level conditions. The devices were flashed one at a time, and from a distance of 19m were gradually brought closer to the screen until the subjects responded. The response data was processed to identify the effective illumination levels required to alert people to the flashing signals from the six devices.
Analysis of this data revealed that as the pulse durations of LED devices shorten, the attention drawing effectiveness increases. It also demonstrated no significant difference in responses between warm white LED devices and cool white LED devices. The Xenon and 10ms cool white LED device had similar responses; however, a cool white LED device with a pulse duration of 5ms may out-perform a Xenon device.
 Related articles on Designing Buildings Wiki
- Automatic fire detection and alarm systems, an introductory guide to components and systems BR 510.
- Carbon monoxide detector.
- Combustion appliance.
- Evacuating vulnerable and dependent people from buildings in an emergency FB 52.
- Fire and rescue service.
- Fire dampers.
- Fire detection and alarm system.
- Fire detector.
- Fire performance of external thermal insulation for walls of multistorey buildings, third edition (BR 135).
- Fire protection engineering.
- Fire safety design.
- Heat alarm.
- Intelligent building management systems IBMS.
- Ionisation smoke alarms.
- Optical smoke alarm.
- Personal protection watermist systems in the homes of vulnerable people.
- Smoke detector.
- The causes of false fire alarms in buildings.
- Understanding the factors affecting flashover of a fire in modern buildings.
Featured articles and news
RSHP unveil their involvement in a boundary crossing which will provide a new entry point into Hong Kong.
With PFI currently under the spotlight due to Carillion, this introductory article explains what they are.
Estimates suggest that up to 30,000 small firms could be at risk of non-payment as a result of Carillion's collapse.
Sir Oliver Letwin to lead an independent review into the delays in the delivery of housing.
As Carillion collapses, read our article explaining insolvency in the construction industry.
43,000 jobs at risk as Carillion declares insolvency..
1961 saw the publication of three important books about urban design that remain relevant today.
Next week the planning fee increases by 20% and new fees are introduced.
How the transformative power of BIM and other digital technologies can be used to gain a competitive edge.
Relevant events and relevant matters are terms used in some contracts, but knowing the differences is important.
Government release statistics showing how many people are now on the property ladder due to Help to Buy schemes.