- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 18 Nov 2017
Visual alarm devices - their effectiveness in warning of fire
Research by BRE looked at the effectiveness of visual alarm devices in warning building occupants of fire.
The research compared the responses of a group of participants to flashing Xenon and LED devices of varying pulse durations. One Xenon device, three cool white LED devices (of 40, 20 and 10 millisecond (ms) pulse durations) and two warm white LED devices (of 40 and 20ms pulse durations) were used.
The flashing signals were presented individually to 96 participants who were seated in front of a screen and occupied with a written task. The tests were performed in high and low ambient light level conditions. The devices were flashed one at a time, and from a distance of 19m were gradually brought closer to the screen until the subjects responded. The response data was processed to identify the effective illumination levels required to alert people to the flashing signals from the six devices.
Analysis of this data revealed that as the pulse durations of LED devices shorten, the attention drawing effectiveness increases. It also demonstrated no significant difference in responses between warm white LED devices and cool white LED devices. The Xenon and 10ms cool white LED device had similar responses; however, a cool white LED device with a pulse duration of 5ms may out-perform a Xenon device.
 Related articles on Designing Buildings Wiki
- Automatic fire detection and alarm systems, an introductory guide to components and systems BR 510.
- Carbon monoxide detector.
- Combustion appliance.
- Evacuating vulnerable and dependent people from buildings in an emergency FB 52.
- Fire and rescue service.
- Fire dampers.
- Fire detection and alarm system.
- Fire detector.
- Fire performance of external thermal insulation for walls of multistorey buildings, third edition (BR 135).
- Fire protection engineering.
- Fire safety design.
- Heat alarm.
- Intelligent building management systems IBMS.
- Ionisation smoke alarms.
- Optical smoke alarm.
- Personal protection watermist systems in the homes of vulnerable people.
- Smoke detector.
- The causes of false fire alarms in buildings.
- Understanding the factors affecting flashover of a fire in modern buildings.
Featured articles and news
Land which is, or was, occupied by a permanent structure; brownfield sites can have significant development potential.
The 3-day IHBC 2018 School will focus on; Our Shared heritage: Communication - Negotiation – Transformation.
An innovative 'green bench' is installed in London that absorbs as much pollution as 275 trees.
Book review – a series of essays about architecture and urbanism in the British Empire.
The complex situation where events occur at the same time.
How can Latin America and the Caribbean unlock the digital potential of their new and existing built environment?
CIOB publish a new code of estimating practice.
These relate to a programme where each activity is allocated a price and interim payments made against completion.
Police testing finds that flat door could only withstand fire for half its designed time.
Have a look at these images from a new photography book of buildings being reclaimed by nature.
What does the phrase 'demised premises' mean? Find out here in our introductory article.