- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 06 Oct 2019
Visual alarm devices - their effectiveness in warning of fire
The research compared the responses of a group of participants to flashing Xenon and LED devices of varying pulse durations. One Xenon device, three cool white LED devices (of 40, 20 and 10 millisecond (ms) pulse durations) and two warm white LED devices (of 40 and 20ms pulse durations) were used.
The flashing signals were presented individually to 96 participants who were seated in front of a screen and occupied with a written task. The tests were performed in high and low ambient light level conditions. The devices were flashed one at a time, and from a distance of 19m were gradually brought closer to the screen until the subjects responded. The response data was processed to identify the effective illumination levels required to alert people to the flashing signals from the six devices.
Analysis of this data revealed that as the pulse durations of LED devices shorten, the attention drawing effectiveness increases. It also demonstrated no significant difference in responses between warm white LED devices and cool white LED devices. The Xenon and 10ms cool white LED device had similar responses; however, a cool white LED device with a pulse duration of 5ms may out-perform a Xenon device.
 Related articles on Designing Buildings Wiki
- Automatic fire detection and alarm systems, an introductory guide to components and systems BR 510.
- Carbon monoxide detector.
- Combustion appliance.
- Evacuating vulnerable and dependent people from buildings in an emergency FB 52.
- Fire and rescue service.
- Fire dampers.
- Fire detection and alarm system.
- Fire detector.
- Fire performance of external thermal insulation for walls of multistorey buildings, third edition (BR 135).
- Fire protection engineering.
- Fire safety design.
- Heat alarm.
- Intelligent building management systems IBMS.
- Ionisation smoke alarms.
- Optical smoke alarm.
- Personal protection watermist systems in the homes of vulnerable people.
- Smoke detector.
- The causes of false fire alarms in buildings.
- Understanding the factors affecting flashover of a fire in modern buildings.
- Visual alarm devices for fire: An introduction and guide to BS EN 54-23.
Featured articles and news
The admissibility of evidence.
How many can you name? 37 anyone?
CIOB respond to the points-based system.
When is the weather considered 'exceptionally adverse'?
ECA backs call for a rolling programme of rail electrification.
What does 'curtilage' mean and why does it matter?
Our duty to prevent harm and protect each other.
A quality perspective.
If buildings were people, they would be just starting to walk on two legs.
Air filtration and clean air standards.
The Dukes of Normandy and the second world war.