- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 23 Sep 2017
Personal protection watermist systems in the homes of vulnerable people
In November 2015, London Fire Brigade and BRE published Personal Protection Systems (PPS), Guidance on the use, deployment and limitations of Personal Protection Watermist Systems in the homes of vulnerable people.
Vulnerable people and the elderly are at greater risk from fire in the home, in particular if they live on their own. This can be because of their lifestyle and mental capacity, and because their physical and/or mental health impairments mean they may be unable to easily escape without assistance.
A Personal Protection System is an automatic fire suppression device, designed specifically for a domestic environment. It activates over a bed or chair that is the seat of a fire, protecting individuals who may be unable to escape without assistance. PPS systems have also been used as risk reduction measures in other types of applications, for example where a home is at risk from an arson attack.
PPS units are portable risk reduction measures, that can be quickly installed, moved or re-used. A typical PPS is self-contained and consists of a water container connected to an open watermist nozzle. An internal control panel automatically activates the system when a fire is detected causing watermist to be sprayed from the nozzle onto the risk area. Because PPS are designed to activate at an earlier stage of fire development than traditional sprinkler systems, they have a faster response to a fire and this can help to prevent significant heat and smoke development.
The guidance includes tools for identifying likely candidates for a PPS. A typical risk profile would be a person who, because of mental and/or physical health issues, spends the majority of their time in a bed or chair and who would be unable to easily escape in the event of a fire. A vulnerable person who is mobile and so has the potential to be affected by a fire anywhere in their home would usually require a suppression system that covers all risk areas
Having identified that an individual is vulnerable from fire it is necessary to carry out a specific assessment of the level of risk and the benefits of a range of potential control measures. This step will often follow a more general risk assessment carried out by a care or housing provider or a home fire safety check carried out by the fire and rescue service.
 Find out more
 Related articles on Designing Buildings Wiki
- BRE articles on Designing Buildings Wiki.
- Carbon monoxide detector.
- Changing lifestyles.
- False alarms.
- Fire and rescue service.
- Fire and rescue service.
- Fire dampers.
- Fire detection and alarm system.
- Fire detector.
- Fire protection engineering.
- Fire safety design.
- Homes and ageing in England.
- Inclusive design.
- Older people.
- People with disabilities.
- Smoke detector.
- Watermist systems for fire protection in domestic and residential buildings DG 534.
Featured articles and news
What should be evaluated to assess building performance?
BIM standards BS 1192:2007+A2:2016 and PAS 1192-2:2013 have been superceded.
What is biophilic design and how can it increase wellbeing?
80 experts come up with the top 7 mistakes the industry makes with BREEAM.
Compliance cannot be verified by inspection on delivery.
Some electric cars have batteries that give a range of over 350 miles.
Assembling, curating, caring for, and designing the future.
A sensitive approach to renovating a building of historic stature.
UK energy policy uncertainty as Welsh project put on hold
What collaborative working achieves and how it can be put in place.
BSRIA publishes the 2019 edition of its small but concise annual databook.
Using QSAND to measure the performance of disaster response.
What U-values are, why they matter and how they are calculated.