- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 03 Oct 2017
Watermist systems for fire protection in domestic and residential buildings DG 534
Watermist systems for fire protection in domestic and residential buildings: An introduction (DG 534) was published by BRE on 10 September 2014. It was written by Corinne Williams.
A form of watermist was first used for the protection of assets from fire in industrial applications in the 1930’s. More recently they have been used for the protection of spaces on board ships and for industrial and commercial applications. Watermist fire protection systems are now being considered for installation as fire protection measures in domestic and residential buildings in the UK. They can be considered a ’green’ alternative to automatic sprinkler systems because of their potential to reduce water consumption, although they are seen as a novel technology in the market.
Watermist fire protection systems are sensitive to small design changes and so successful implementation requires in-depth knowledge of the system and its intended application from watermist suppliers and approving bodies.
This 12 page digest provides an introduction to watermist systems in domestic and residential buildings for designers, specifiers, authorities such as building control bodies, fire safety officers and insurers, clients, developers, fire safety managers and non-specialists. It covers the general background, reasons for choosing watermist systems, current UK standards, how watermist systems work, issues to be considered during specification, design, installation and ongoing maintenance, the use of independent third-party approved suppliers, and products.
The contents of the digest include:
- Description of domestic and residential watermist systems and how they work.
- System fire performance tests.
- Planning and specification.
- Design, installation and commissioning.
- Ongoing maintenance, system continuity and documentation.
- Alternative suppression systems.
- Use of independent third-party approved suppliers and products.
- Further information.
 Related articles on Designing Buildings Wiki
- Automatic fire sprinkler systems: A good practice guide.
- BRE articles on Designing Buildings Wiki.
- BRE Buzz articles on Designing Buildings Wiki.
- BRE Buzz.
- Building Research Establishment.
- Design benefits of automatic sprinkler systems granted under approved document B.
- Evaluation of cooling effects: outdoor watermist fan.
- Fire in buildings.
- Fire protection engineering.
- Fire safety design.
- Personal protection watermist systems in the homes of vulnerable people.
- Sprinkler systems explained: A guide to sprinkler installation standards and rules.
- The impact of automatic sprinklers on building design.
Featured articles and news
Gustavo Giovannoni’s role in integrating modern planning requirements into historic town centres.
Against Hackitt's recommendations, the government are to consult on combustible cladding ban.
People or density - can we create urban liveability at ever-increasing densities?
3D printing is the computer-controlled sequential layering of materials to create 3D shapes.
Hackitt review calls for a radical rethink of the whole system and how it works.
Life cycle assessment is used to total up the environmental impact of a product’s supply chain. But why building LCA?
The government warns building owners of a performance issue with Grenfell fire doors.
Ramboll discusses how digitisation is contributing to how they design, engineer and construct in new and different ways.
'Carillion could happen again, and soon' is the stark warning from the heavily critical final report into Carillion's collapse.
In the wake of British architect Will Alsop's death, read about one of his most distinctive buildings.