Fire detection and alarm system
Most fire detection and alarm systems operate on the same basic principles. If a fire is detected, then an alarm is triggered. This warns building managers and occupants that there may be a fire and that evacuation may be necessary. Some systems include remote signalling equipment which can alert the fire brigade or a remote monitoring centre.
Fire can be detected by; heat detectors, flame detectors, smoke detectors, carbon monoxide detectors and multi sensor detectors, or an alarm can be triggered at manual call points. Alarms may consist of bells, sirens, horns, lights or a combination these. Two power supplies are required, generally a mains supply and batteries providing 24 hours back up.
It is important that a thorough assessment of need is undertaken before a fire detection and alarm system is designed or purchased.
- L, (L1 to L5): automatic systems intended for the protection of life.
- M: manual systems, fitted with sounders and call points.
- P, (P1 and P2): automatic systems intended for the protection of property.
Fire detection and alarm systems can be divided into a number of general types:
- Conventional systems.
- Addressable systems.
- Analogue addressable systems.
- Wireless systems.
- Self-contained units.
Conventional systems generally consist of a series of detectors and call points wired to a control panel which drives the detectors and a minimum of two sounder circuits, includes LED indicators and allows de-activation and resetting. Typically, separate circuits will be provided for each fire 'zone' (usually a floor of a building or a fire compartment). This separation into zones means that the approximate location of the fire is known and so the appropriate response can be instigated. It also allows for easier diagnosis of faults.
Addressable systems are similar to conventional systems, but the central control panel can identify exactly which detector or call point triggered the alarm (rather than just a zone), or whether communication has been lost with a detector. In this system the circuit is wired in a loop, with a number of detectors or call points on each loop. The loop can be powered from both ends, so that it continues to function even if there is a break in the loop (separate loops may still be provided for each zone). The control panel can be programmed to show specific information, or trigger specific responses for different detectors within the system. Addressable systems are generally used for larger or more complex installations because of the benefits of more accurate detection, and so fault finding, and the reduced wiring requirement.
Analogue addressable systems, or intelligent systems can include an analytical capability in each detector which can assess local parameters to determine whether there is a fire, a fault or a maintenance requirement. This can be useful in preventing the occurrence of false alarms. A pre-alarm warning may be indicated if a detector is approaching a trigger condition.
Wireless fire alarm systems connect detectors and call-points to the control panel using wireless signals.
NB, The 2014 BRE briefing paper, The causes of false fire alarms in buildings, found that; 'False alarms generated from remotely monitored fire detection and fire alarm systems cost businesses and Fire and Rescue Service (FRS) authorities an estimated £1 billion a year in the UK. In the period 2011-2012 a total of 584,500 fire and false alarms were reported in Britain, 53.4% of these were not fires and therefore considered “False alarms”. This is a considerable drain on FRS authorities as well as causing business disruptions leading to a loss of productivity and reducing the confidence of the general public.'
The paper proposed that education could contribute significantly to reducing false alarms and that the increased use of multi-sensor detectors is a cost effective way of averting false alarms from common causes such as cooking fumes and steam.
 Related articles on Designing Buildings Wiki
- Access control.
- Automatic fire detection and alarm systems, an introductory guide to components and systems BR 510.
- Commercial security systems.
- External fire spread, Supplementary guidance to BR 187 incorporating probabilistic and time-based approaches.
- Fire and rescue service.
- Fire dampers.
- Fire detector.
- Fire door inspection scheme.
- Fire protection engineering.
- Fire safety design.
- Global overview analysis of fire and security.
- Heat alarm.
- Intruder alarm.
- Ionisation smoke alarm.
- Joint fire code.
- Multi-sensor alarm.
- Optical smoke alarm.
- Perimeter security.
- Security and the built environment.
- The causes of false fire alarms in buildings.
- The Regulatory Reform (Fire Safety) Order 2005.
- The role of codes, standards and approvals in delivering fire safety.
- Wet riser.
Featured articles and news
We review a book aiming to unpick the complexities of building physics.
An introduction to the categories, procedures and types of listed buildings.
This Australian robotics firm have developed a bricklaying machine capable of building a house in 3 days.
20bn devices will be online by 2020, generating huge volumes of information. Is society making the most of this rich data?
Built over a period of 632 years, Cologne Cathedral is considered one of the world's finest examples of Gothic architecture.
UandI adds £1.5bn to development pipeline.
Here are 5 things leaders can do to create a truly circular economy.
Find out about the different types of delays on construction projects.
Researchers at Wien university have developed new system to create an inflatable concrete structure.
Take a look at this newly-opened tower in Chicago with a remarkable 20:1 height-to-base ratio.
The principles, practice and formwork of one of the most important components of modern architecture.