- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 17 Dec 2020
Ionisation smoke alarm
Ionisation smoke alarms are more sensitive to smoke containing small particles such as rapidly burning flaming fires but are less sensitive to steam. As a result of this, they are recommended for use in hallways and stairwells adjacent to bathrooms or shower rooms to reduce the number of unwanted false alarms.
Ionisation smoke alarms should conform to BS EN 14604: 2005 - Smoke Alarm Devices.
Characterising smoke from modern materials and evaluating smoke detectors was written by Raman Chagger and published by BRE in 2014 states that:
|Ionisation detectors use a small radioactive source (americium-241) inside an ionisation chamber that contains charged electrodes. The chamber is arranged to allow a flow of air from outside. As the air enters it becomes ionized, generating an electric current between the charged electrodes. When smoke particles pass into the chamber the ions become attached to them and are carried away, leading to a reduction in the current. More ions are stripped away when there are many small particles, such as those generated during flaming fires. When a material is smouldering it tends to produce fewer but larger particles than it does when in flames. As these cause less current reduction, ionisation detectors are inherently less responsive to the large smoke particles generated during smouldering fires.|
 Related articles on Designing Buildings Wiki
- Carbon monoxide.
- Carbon monoxide detector.
- Characterising smoke from modern materials and evaluating smoke detectors.
- Domestic smoke alarms DG525.
- Fire detection and alarm system.
- Fire detector.
- Fire fatalities in Scotland.
- Heat alarm.
- Multi-sensor alarm.
- New requirements for fire detection and alarm network systems IP 12 13.
- Optical smoke alarm.
- Over £1 billion lost every year due to false alarms.
- Smoke detection in high ceiling spaces.
- Smoke detector.
- The causes of false fire alarms in buildings.
Featured articles and news
Interview with historic built environment surveyor.
Upgraded membership category now requires assessment.
Temperature in buildings, explained on DB
Main barrier to entering the profession, new study reveals.
On Levelling-Up and Regeneration Bill.
Over 70 managers and organisations shortlisted for the 14 awards.
From biometric to electrical current, chemical and more.
Changes are due to come into force on 1st October 2022.
Heed advice and insight of this report IPA tells the government.
From the Commonwealth Association of Architects.