- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 11 Aug 2019
Carbon monoxide detector
Carbon monoxide (CO) is a colourless, tasteless and odourless gas that is highly poisonous. It can cause serious damage to health if inhaled over a long period, and can quickly cause neurological damage, paralysis or death.
Carbon monoxide is produced when a combustion appliance such as a boiler, heater, oven, and so on, does not completely burn a carbon-based fuel. This might include fuels such as; gas, oil, paraffin, coal, wood or charcoal. Typically, fuel might not be completely burned if an appliance has been incorrectly installed or maintained or if vents, chimneys or flues are blocked. It may also enter a property through shared chimneys or flues.
If a building is powered entirely by electricity, a carbon monoxide detector is not necessary, but there should be one in every room in a building where there is a fuel-burning boiler, fire, or stove.
Because carbon monoxide is colourless, tasteless and odourless, people may not notice it, but it can be detected by a carbon monoxide detector. Typically, an audible alarm is sounded if carbon monoxide is detected.
There are several different types of carbon monoxide detectors/alarms:
- A standalone unit
- A combined unit that also operates as a smoke detector.
- Sealed battery: Batteries are sealed inside the detector and an alarm sounds when they run out.
- Replaceable battery: Batteries will need replacing every 2-3 years.
- Smart detector: Alerts the occupant via their smartphone as well as triggering the alarm.
- Patch: This is a cheaper option which changes colour if there is carbon monoxide in the atmosphere, however, this is less safe as it does not sound an alarm.
Detectors should have a EN 50291 mark and a British Standards' Kitemark (or equivalent European mark). They should be installed in accordance with manufacturers’ instructions, typically at head height in each room with a combustion appliance. They should be tested regularly, and batteries replaced as required.
In 2015, the government introduced new regulations requiring private rented sector landlords in England to instal a carbon monoxide alarm in any room used as living accommodation where solid fuel is used. Detectors must be tested at the start of each tenancy, and penalties for failure to comply can be up to £5,000.
In April 2018, the government announced it was undertaking a review of rules that require carbon monoxide alarms to be fitted in homes across England when solid fuel appliances such as wood burning stoves and boilers are installed. The review will examine the regulations to establish whether they remain fit for purpose and will consider new research into the number of carbon monoxide poisonings and whether the rate of installation is being affected by the cost of alarms. (Ref. https://www.gov.uk/government/news/government-to-launch-review-into-carbon-monoxide-alarms)
 Related articles on Designing Buildings Wiki
Featured articles and news
Technology informs procurement and planning practices.
BSRIA releases market sector growth projections.
Designing for durability and resilience.
Do plans to connect infrastructure and housing stack up?
1 minute review of CAMRA’s guide to historic drinking dens.
Their complex heritage remains largely unknown.
New editor covered facilities management, operations and construction in the US.
Exclusive log cabins on the North Antrim coastline.
Proactive forestry for strategic water management.
CIOB urges construction to share PPE with healthcare providers.
Why not write that article you've always meant to?