Types of domestic boiler
Domestic boilers heat water that can be used to supply a central heating system, or hot water for taps, or both. Boilers are generally fuelled by mains gas, however if a mains gas supply is not available, they may use an alternative fuel such:
- Liquid petroleum gas (LPG).
According to the Energy Saving Trust, boilers account for approximately 60% of domestic CO2 emissions. Since 2005, most new gas-fuelled boilers have had to be condensing boilers, and since 2007, this has also applied to oil-fired boilers. Condensing boilers are boilers that recover heat from flue gases to be re-used. This makes them more efficient than non-condensing boilers. However, condensing boilers need connection to drainage which can be problematic in some older properties depending on the location of the boiler.
On 26th September 2015 the Energy Related Products directive (ErP) came into force. This included requirements for ‘ecodesign’ and energy labelling. The eco-design element sets minimum permissible efficiencies for boilers with an output of up to 400kW. Energy labelling is required for boilers with an output of up to 70kW, indicating how efficient a boiler is on a scale from A+++ to G. A+ ratings and above apply to renewable products such as heat pumps.
There are a number of different types of domestic boiler.
Conventional boilers (sometimes referred to as traditional, heat only or open vent boilers) can supply central heating and hot water for sinks, baths and showers. They require a cold water supply tank and a hot water storage cylinder. Cold water supplied from the tank is heated by the boiler and then stored in the cylinder until required.
Because there is a ‘reservoir’ of stored hot water, they can supply more than one use at the same time. For example a shower and a sink. However, once the hot water in the cylinder has been used, it can take quite a long time for it to be replaced by the boiler. They also required space for the tank and cylinder.
Because hot water is supplied ‘instantaneously’ rather than being stored and then used, they can provide unlimited hot water on demand, and are useful where there is limited space availability. This can be a more efficient type of boiler, as the hot water is used immediately, rather than being stored.
However, as there is no reservoir of how water, when there are multiple simultaneous uses, the pressure may drop. This may make them best suited to smaller, lower-occupancy properties.
System boilers, or ‘sealed system’ boilers have a hot water cylinder but no water tank. This requires less space than a conventional boiler, but means that more than one use can be supplied at the same time. However, the hot water supply is limited to the size of the cylinder.
Micro-CHP is becoming more common in domestic buildings, where it can be installed as direct replacement for gas-fired boilers as micro-CHP units (sometimes referred to as CHP boilers) are similar in size and shape to conventional domestic boilers and can be floor standing or wall hung.
See CHP boilers for more information.
Biomass boilers run on renewable fuels such as wood pellets. The emissions produced by biomass boilers are much lower than emissions from fossil fuels and traditional boiler types. This is because the carbon dioxide emitted is the same amount that was absorbed while the plant was growing. The price of fuel types for biomass boilers is often cheaper than other heating options and can be locally sourced. Financial support from the government is also available under the Renewable Heat Incentive, which can help to further reduce overall costs.
One disadvantage of biomass boilers however is the space needed, as they are larger than standard boilers. They also need space to keep the fuel. If there is not a local supplier who can deliver fuel, then the price of fuel deliveries can increase. You may also need planning permission to install a biomass boiler system, depending on where it and its components are located.
See Biomass boiler for more information.
 Related articles on Designing Buildings Wiki
- Balanced flue appliance.
- Biomass boiler.
- Boiler efficiency.
- Carbon monoxide detector.
- CHP boiler.
- Coefficient of Performance CoP.
- Combustion appliance.
- Condensing boiler.
- Domestic micro-generation.
- Energy related products regulations.
- Gross calorific value.
- Heat interface units.
- Heat pump.
- What are electric fires?
Featured articles and news
What is the Home Quality Mark? Find out how it can help you when buying/renting a new home.
Business Secretary launches £246m Faraday Challenge to establish UK as world leader in battery technology.
Government announces new plans for regulations to improve safety and security awareness of drone users.
Read our introductory article to the various different types of fuel.
IHBC book review: Charles Barry’s monumental struggle to rebuild the Houses of Parliament.
Read about RSHP's British Museum extension which has been shortlisted for the 2017 Stirling Prize.
Read our introductory article to building a house extension.
More updates from DCMS about the large-scale testing of cladding systems and the number of buildings affected.
UandI secure resolution to grant planning consent for major new regeneration project.
IHBC article considers how heritage is dealt with when infrastructure schemes are authorised.
It was the tallest structure in the world for 3,800 years, but to this day the exact construction techniques are a mystery.
Shortlist for the industry's most coveted award announced.
Government responds to Mark Farmer's review of industry, rejecting the call for a levy on clients.