- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 08 Feb 2018
A refrigerant fluid is run through the lower temperature source. The fluid ‘absorbs’ heat and boils, even at temperatures below 0°C (although the coefficient of performance (COP) decreases with lower temperature). The resulting gas is then compressed, which further increases its temperature. The gas is passed into heat exchanger coils, where it condenses, releasing its latent heat. The process then repeats.
This is the same process that is used to extract heat from a fridge.
Heat pumps can be used domestically or commercially to provide hot water, space heating (either by providing hot water for under-floor heating or radiators, or supplying hot air) or other applications such as heating swimming pools.
In the UK, heat pumps are most commonly air-source or ground-source heat pumps. However, the temperature of ground water sources in the UK tends to be fairly constant for most of the year, at between 8 and 12°C, and so water source heat pumps can be more efficient.
- Air source heat pumps absorb heat from the outside air. Air-to-water systems provide hot water for direct use or to supply radiators or underfloor heating systems. Air-to-air systems provide hot air, either directly into an internal space, or to be distributed by fans throughout a building. See Air source heat pumps for more information.
- Ground source heat pumps use lengths of plastic pipe buried in the ground, either in a borehole or a horizontal trench. See Air source heat pumps for more information.
- Water source heat pumps absorb heat from a suitable local water source, such as a lake, river, well, borehole and so on. They can be ‘open-loop’ or ‘closed-loop’ systems. See Air source heat pumps for more information.
Heat pumps may be eligible for payments under the government’s Renewable Heat Incentive (RHI) scheme. Domestic schemes may also be eligible for financing through the green deal, however, there has been very poor uptake of the Green Deal, and it is generally considered that better financial deals are available elsewhere.
Refrigeration units also use heat pumps, as do chiller units that provide chilled water (CHW) for space cooling, for example in air handling units, fan coil units, chilled beams and so on. In this case, the system is reversed, absorbing heat from the interior and releasing it to the outside.
Heat pumps generally use electricity to power the compressor. However, in absorption heat pumps, the refrigerant (typically ammonia) is absorbed into water, then is released again by being heated. The heat source is generally gas fuelled (Gas Absorption Heat Pumps GAHP) but other heat sources can be used, such as solar heated water.
 Related articles on Designing Buildings Wiki:
- Absorption heat pump.
- Air source heat pumps.
- Coefficient of Performance CoP.
- Domestic heat pumps and the electricity supply system.
- Dynamic thermal modelling of closed loop geothermal heat pump systems.
- Earth-to-air heat exchangers.
- Exhaust air heat pump.
- Geothermal pile foundations.
- Green Deal.
- Ground energy options.
- Ground source heat pumps.
- Heat exchanger.
- Heat recovery.
- Mechanical ventilation with heat recovery.
- Phase change.
- Renewable Heat Incentive.
- Residential heat pump installations: the role of vocational education and training.
- Solar-assisted heat pump.
- Solar thermal heating.
- Thermal labyrinths.
- Types of domestic boiler.
- Types of heating system.
- Underfloor heating.
- Water source heat pumps.
Featured articles and news
Whole-life costs consider all costs associated with the life of a building, from inception to disposal. Find out more here.
Reports emerge of injuries caused by Apple employees colliding with the campus' glazed walls.
The winners of NIC's ideas competition on transforming the Cambridge to Oxford arc discuss their concept.
Create new habitats and improve air quality and wellbeing.
New report provides 12 key actions which could close the structural talent gap in the construction industry.
These can be used to find out whether a proposed development is likely to be approved. Read more here.
Studying a built environment degree? Check out our helpful student resources section.
New BRE research paper explores how blockchain technology can benefit the built environment industry.
Timber is a natural carbon sink, but it must not end up in landfill at the end of its useful life.
BSRIA has collaborated with the Department of Health on research into air permeability in isolation rooms.