To help develop this article, click ‘Edit this article’ above.
Chillers are used in buildings to provide cooling. This is typically for heating, ventilation and air conditioning (HVAC) systems providing thermal comfort for occupants, but they can also be used to provide cooling for industrial processes.
- In compression systems, a liquid refrigerant with a low boiling point absorbs heat from water returning from the building and boils in an evaporator to form a gas. The gas is then compressed, which increases its temperature further. The gas is then condensed, releasing its latent heat which is rejected to the outside. The process then repeats.
- Absorption refrigeration works on a similar basis, with a refrigerant that boils at low temperature and pressure, however, in this case, the refrigerant gas is then absorbed in a solution which is then heated in a ‘generator’ so that the refrigerant evaporates again, but this time at a higher pressure and temperature. The gas is then condensed, releasing its latent heat which is rejected to the outside. The process then repeats.
The rejection of heat from chiller units can be achieved by:
- Air cooling, which rejects heat to the outside air by circulating it through the condenser.
- Evaporative cooing, which uses the addition of a water mist to the air to enhance the cooing effect.
- Water cooling, which is generally suited to large systems and requires connection to cooling towers.
The exact opposite of the refrigeration process can be achieved by a heat pump, which reverses the cycle so that heat is supplied to the building rather than cooling. Some systems are reversible, able to supple either heat or cooling. See Heat pump for more information.
Typically in heating, ventilation and air conditioning systems, chiller units produce chilled water that is piped to air handling units (or fan coil units) where it is used to cool the air that ventilates the building. The ‘warmed’ water is then returned to the chiller unit to be re-cooled. The process of cooling ventilation air will also reduce its humidity.
Air handling units may also include a heating coil for times when heating rather than cooling is required. In some situations, air that has already been cooled will be re-heated (typically in simple, single duct constant air voume (VAC) systems). Whilst this may seem wasteful, in buildings where there are some minor local variations in thermal demand it can be more economic than it would be to provide two separate air ducting networks.
An alternative system supplies the refrigerant itself (rather than chilled water) to terminal units supplying different thermal zones. Variable refrigerant flow (VRF) systems use a single external condensing unit and multiple internal evaporators and can be more efficient, more compact and offer greater flexibility than other HVAC systems. See Variable refrigerant flow for more information.
Some refrigerants have both ozone depletion potential (ODP) and global warming potential (GWP), and as a consequence refrigerants such as CFC’s (chlorofluorocarbons) are banned. New equipment using HCFCs ((hydrochlorofluorocarbons such as R22 and R408A) was banned in 2001 (2004 for small systems), and the use of virgin HCFC's was banned in 2010, when it also became illegal to manufacture HCFC refrigerants or for suppliers to keep them in stock. From January 1st 2015 the use of HCFC’s was prohibited in any form, even for maintenance. The use of HFC's (hydrofluorocarbons, including 417A, 422A, 422D, 424A, 427A, 428A and 434A) continues to be permitted. Other refrigerants include, ammonia (common in absorption refrigeration), carbon dioxide and non-halogenated hydrocarbons.
It is important that the design of HVAC systems is considered as a part of the overall design process for the building, and not seen as an add on at the end. It is also important that HVAC systems are regularly maintained to ensure optimum performance and occupant comfort.
 Related articles on Designing Buildings Wiki
Featured articles and news
IHBC book review: Charles Barry’s monumental struggle to rebuild the Houses of Parliament.
Read about RSHP's British Museum extension which has been shortlisted for the 2017 Stirling Prize.
Read our introductory article to building a house extension.
More updates from DCMS about the large-scale testing of cladding systems and the number of buildings affected.
UandI secure resolution to grant planning consent for major new regeneration project.
IHBC article considers how heritage is dealt with when infrastructure schemes are authorised.
It was the tallest structure in the world for 3,800 years, but to this day the exact construction techniques are a mystery.
Shortlist for the industry's most coveted award announced.
Government responds to Mark Farmer's review of industry, rejecting the call for a levy on clients.
Peter Hansford to examine what wider lessons can be learned from the fire.
Every project is subject to uncertainty. How can construction better understand uncertainty for performance improvement?
MAD Architects reveal their designs for a futuristic campus for electric car manufacturer.
Homebuyers could borrow more with better forecasting of energy bills, according to industry consortium's new report.