- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 23 Feb 2015
To help develop this article, click ‘Edit this article’ above.
Chillers are used in buildings to provide cooling. This is typically for heating, ventilation and air conditioning (HVAC) systems providing thermal comfort for occupants, but they can also be used to provide cooling for industrial processes.
- In compression systems, a liquid refrigerant with a low boiling point absorbs heat from water returning from the building and boils in an evaporator to form a gas. The gas is then compressed, which increases its temperature further. The gas is then condensed, releasing its latent heat which is rejected to the outside. The process then repeats.
- Absorption refrigeration works on a similar basis, with a refrigerant that boils at low temperature and pressure, however, in this case, the refrigerant gas is then absorbed in a solution which is then heated in a ‘generator’ so that the refrigerant evaporates again, but this time at a higher pressure and temperature. The gas is then condensed, releasing its latent heat which is rejected to the outside. The process then repeats.
The rejection of heat from chiller units can be achieved by:
- Air cooling, which rejects heat to the outside air by circulating it through the condenser.
- Evaporative cooing, which uses the addition of a water mist to the air to enhance the cooing effect.
- Water cooling, which is generally suited to large systems and requires connection to cooling towers.
The exact opposite of the refrigeration process can be achieved by a heat pump, which reverses the cycle so that heat is supplied to the building rather than cooling. Some systems are reversible, able to supple either heat or cooling. See Heat pump for more information.
Typically in heating, ventilation and air conditioning systems, chiller units produce chilled water that is piped to air handling units (or fan coil units) where it is used to cool the air that ventilates the building. The ‘warmed’ water is then returned to the chiller unit to be re-cooled. The process of cooling ventilation air will also reduce its humidity.
Air handling units may also include a heating coil for times when heating rather than cooling is required. In some situations, air that has already been cooled will be re-heated (typically in simple, single duct constant air voume (VAC) systems). Whilst this may seem wasteful, in buildings where there are some minor local variations in thermal demand it can be more economic than it would be to provide two separate air ducting networks.
An alternative system supplies the refrigerant itself (rather than chilled water) to terminal units supplying different thermal zones. Variable refrigerant flow (VRF) systems use a single external condensing unit and multiple internal evaporators and can be more efficient, more compact and offer greater flexibility than other HVAC systems. See Variable refrigerant flow for more information.
Some refrigerants have both ozone depletion potential (ODP) and global warming potential (GWP), and as a consequence refrigerants such as CFC’s (chlorofluorocarbons) are banned. New equipment using HCFCs ((hydrochlorofluorocarbons such as R22 and R408A) was banned in 2001 (2004 for small systems), and the use of virgin HCFC's was banned in 2010, when it also became illegal to manufacture HCFC refrigerants or for suppliers to keep them in stock. From January 1st 2015 the use of HCFC’s was prohibited in any form, even for maintenance. The use of HFC's (hydrofluorocarbons, including 417A, 422A, 422D, 424A, 427A, 428A and 434A) continues to be permitted. Other refrigerants include, ammonia (common in absorption refrigeration), carbon dioxide and non-halogenated hydrocarbons.
It is important that the design of HVAC systems is considered as a part of the overall design process for the building, and not seen as an add on at the end. It is also important that HVAC systems are regularly maintained to ensure optimum performance and occupant comfort.
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
Rebuilding could take 20 to 40 years.
RSHP’s high-rise residential towers win a tall buildings award for excellence.
BSRIA study reveals strong growth in 2018.
Dame Judith Hackitt confirmed as keynote speaker – one year on from the Hackitt Report.
Save £100 on tickets.
Modern slavery in the construction sector.
What to bear in mind when claiming damages in construction.
How do we achieve sustainable clean-water infrastructure for all?
What you should know when appointing an architect.
A brief history plus some new developments.
How computational fluid dynamics (CFD) helps building design.
The Hong Kong Harbour Area Treatment Scheme (HATS).
'Expressions of interest' for construction contracts.