- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 09 Apr 2018
To help develop this article, click ‘Edit this article’ above.
They were first used in the Shell headquarters in London in the 1960’s, but have only recently become popular as energy efficiency has become more important and buildings services have been better integrated into the early stages of the design process.
Very broadly, chilled beams can be passive or active.
 Passive chilled beams
Passive chilled beams rely on buoyancy to create air movement through the beam. As air in the space heats up, it rises to the ceiling level, where it is cooled by the chilled beam and descends back into the occupied space. This requires a greater open area for air circulation than active chilled beams, and care must be taken to avoid creating draughts.
Separate systems are required to provide ventilation, heating and if required humidity control. Passive chilled beams are not effective at heating as the hot air will rise rather than falling into the occupied space.
 Active chilled beams
Active chilled beams are an integral part of a building’s mechanical ventilation system. ‘Fresh’ air is supplied to the beam, either through ductwork or a plenum, and injected into the beam through nozzles which induce air flow from the room below. This mixed (or diluted) air is cooled by passing through the beam fins and then discharged into the space below.
Active chilled beams may also include a heating coil so that the supply air can be heated when required. They can also include other services. Multi-service chilled beams (MSCB), or Integrated Service Modules (ISM) can include lighting, speakers, sprinklers, cables, PIR detectors, and so on. See integrated service module for more information.
 Radiant chilled beams
Radiant chilled beams work on a similar principal, but the chilled fins remain exposed, and so provide additional radiant cooling. Radiant chilled beams can be visually concealed behind perforated panels, or may be exposed. The addition of a radiant component to the cooling process can reduce the reliance convection and so reduce the risk of draughts.
 Radiant chilled ceilings.
Radiant chilled ceilings typically incorporate a network of chilled water coils in ceiling panels with insulation above. In some systems, pipework may be incorporated into plasterboard, but this is less efficient as plaster is an insulator. The ceiling surface then cools the occupied space by both radiation and convection. This provides even temperatures throughout the space and avoids draughts.
Very little space is required for chilled ceilings, which may be installed with a depth of just 100mm. In some systems, small bore cooling coils can be embedded in plaster ceiling finishes themselves.
Chilled beams and chilled ceilings are generally considered to be more energy efficient that conventional heating ventilation and air conditioning (HVAC) systems. They include fewer (or no) moving parts and so tend to be quiet and require little maintenance. They are generally space efficient, allowing lower floor to floor heights and flexibility of layout below.
If properly designed, they can be aesthetically pleasing and can create an even, draught-free thermal environment.
 Find out more
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air handling unit.
- Building services.
- Building services engineer.
- Chiller unit.
- Chilled water.
- CIBSE Case Study Angel Building Refurbishment.
- Fan coil unit.
- Integrated service module.
- Mechanical ventilation.
- Natural ventilation.
- Phase change materials.
- Suspended ceiling.
- Thermal comfort.
- Thermal mass.
- Types of beam.
- Types of ceiling.
 External references
Featured articles and news
What benefits does BIM bring to construction projects?
New Wiki site is set to make BIM mainstream.
And the award winners for 2019 are...
Articles of agreement
Guidance for local authorities and consultancies setting planning conditions.
A real deal – at last?
How does anastylosis help in the reconstructing of ancient monuments?
More than just aesthetic and historic values and meanings.
An exciting and novel collaboration between the RIBA and the SPAB.
Republic of Ireland updates to planning and development.
The different types of pile foundation.
Achieving a net-zero carbon UK by 2050.