- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 15 Apr 2020
Relative humidity (RH) is a measure of the water vapour density of air compared to the water vapour density for saturated air at the same temperature and pressure (that is, the maximum amount of moisture that air can 'hold' at that temperature and pressure). It is expressed as a percentage.
When air cools, it is less able to “hold” moisture, that is, the saturation water vapour density falls, and so relative humidity rises. When the relative humidity reaches 100%, the air will be saturated. This is described as the dew point. If the air continues to cool, moisture will begin to condense.
Humidity influences thermal comfort. The higher the relative humidity, the less heat a person is able to lose heat through the evaporation of moisture on the skin, and so the hotter they will feel. Conversely, air that is too dry can cause problems such as dry eyes, nose, ears and throat. Typically, a relative humidity of 40 to 60% is appropriate in many buildings.
Humidity also affects the performance of buildings, causing condensation, mould growth, mildew, staining, slip hazards, damage to equipment and the corrosion and decay of the building fabric as well as poor performance of insulation. Condensation can occur on surfaces, or can be interstitial condensation, occurring between the layers of the building envelope, typically as a result of air diffusing from the warm interior of the building to the cool exterior and reaching its dew point within the building fabric.
Humidity can be measured using a hygrometer. Typically these are electronic moisture detectors, or devices such as a sling psychrometer which measures dry-bulb temperature and wet-bulb temperature, allowing relative humidity to be calculated or read from charts.
Humidity can be controlled by limiting sources of moisture (including reverse condensation, where moisture evaporates from damp materials), increasing temperatures, humidification or dehumidification, and by ventilation. Condensation can be further avoided by increasing surface temperatures (such as by the inclusion of insulation or by improving glazing).
In particular, it is necessary to avoid cold bridges, situations in a building where there is a direct connection between the inside and outside through one or more elements that are more thermally conductive than the rest of the building envelope, resulting in lower localised temperatures.
Humidity and condensation in buildings is regulated by Approved Document C (Site preparation and resistance to contaminates and moisture) and Approved Document F (Ventilation) and further guidance is available in BS 5250 Code of practice for the control of condensation in buildings.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Approved Document F.
- Cold bridge.
- Damp proofing.
- Dew point.
- Diagnosing the causes of dampness (GR 5 revised).
- Draught proofing.
- Dry-bulb temperature.
- HVAC balancing.
- Interstitial condensation.
- Methodology for moisture investigations in traditional buildings.
- Moisture content.
- Mould growth.
- Preventing overheating.
- Psychometric chart.
- Rising damp.
- Sling psychrometer.
- Thermal comfort.
- Thermal indices.
- Water vapour.
- Wet-bulb temperature.
Featured articles and news
A memorial to a forgotten academic and political economist.
Three different approaches to building quality homes in urban settings.
Leaving suburbia for exurbia.
Hilton Tallinn Park in Estonia completes sustainable renovation.
Sleeper walls support many projects.
Discover the hidden history of pocket doors.
PwC reports on post-pandemic predictions from executives.
Insight for those entering the field of engineering.
A tool borrowed from statistics and applied to construction procurement.
Reports and factsheets for 2018, 2019 released.
Finding the right landscape maintenance contractor.