- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 13 Nov 2020
Integrated service module
Integrated service modules (ISM), sometimes referred to as multi-service chilled beams (MSCB), are a form of factory assembled modular chilled beam that incorporates other services in addition to cooling.
Chilled beams are supplied with chilled water pumped through copper cooling coils bonded to aluminium fins that cool air, primarily by convection. They are generally distributed regularly across the ceiling of a space. They can be active or passive. Passive chilled beams rely on buoyancy to circulate internal air through the beam whereas active chilled beams have ‘fresh’ outside air injected into the beam through nozzles which induce air circulation from the room below. See chilled beams for more information.
- Direct and indirect lighting.
- Speakers and public address systems.
- Voice and data cabling.
- Passive Infrared (PIR) sensors.
Because integrated service modules are fabricated off site, they tend to produce less waste, have a better build quality, have fewer defects and are faster to install. This can also mean that fewer trades and less storage is needed on site.
They can be delivered to site pre-tested and ready to ‘plug and play’. They can be selected from a range of standard modules, but are commonly custom designed to suit particular needs. They can be installed flush with a suspended ceiling but are often fixed to or suspended from an exposed soffit.
Integrated service modules can allow the thermal mass of the floor slab to be exposed, moderating peaks in thermal conditions. However, this can mean that additional acoustic absorption measures are required to compensate for the exposed mass, and this might only be possible on walls and floors.
Integrated service modules can permit reduced floor to floor heights, and so can be suitable for spaces with limited height, such as refurbishment projects, where they allow more free space and also give a better perception of space than a full suspended ceiling.
 Find out more
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air handling unit.
- Building services.
- Building services engineer.
- Chilled beam.
- Chiller unit.
- CIBSE Case Study Angel Building Refurbishment.
- Fan coil unit.
- Mechanical ventilation.
- Natural ventilation.
- Phase change materials.
- Suspended ceiling.
- Thermal comfort.
- Thermal mass.
 External references
Featured articles and news
A brief description of time in the sun.
Given by ICE President Ed McCann.
Two new research reports published by APM.
50% off APM Associate membership for Designing Buildings users.
A commentary from the insurance perspective.
In brief with further links.
A definitive book on a pioneer of green architecture.
Using heritage as a catalyst for reviving historic centres.
Declaration prioritising sustainable urbanisation adopted.
Some brief words about the actuator.
After 34 years at the Institute.
To support the next generation of engineers.
CIAT reporting from the Competition and Markets Authority.
Making sustainable construction number one priority.
Interview with ECA CEO.
Many provisions came into force on June 28, 2022.
With room to expand.
Refurbishment, Energy Efficiency, Indoor air and process.
Aluminium Composite Panels (ACP) is one example.
Write about something you know, help us build and grow !