Integrated service module
Integrated service modules (ISM), sometimes referred to as multi-service chilled beams (MSCB), are a form of factory assembled modular chilled beam that incorporates other services in addition to cooling.
Chilled beams are supplied with chilled water pumped through copper cooling coils bonded to aluminium fins that cool air, primarily by convection. They are generally distributed regularly across the ceiling of a space. They can be active or passive. Passive chilled beams rely on buoyancy to circulate internal air through the beam whereas active chilled beams have ‘fresh’ outside air injected into the beam through nozzles which induce air circulation from the room below. See chilled beams for more information.
Integrated service modules can also include services such as;
- Direct and indirect lighting.
- Speakers and public address systems.
- Voice and data cabling.
- Passive Infrared (PIR) sensors.
Because integrated service modules are fabricated off site, they tend to produce less waste, have a better build quality, have fewer defects and are faster to install. This can also mean that fewer trades and less storage is needed on site.
They can be delivered to site pre-tested and ready to ‘plug and play’. They can be selected from a range of standard modules, but are commonly custom designed to suit particular needs. They can be installed flush with a suspended ceiling but are often fixed to or suspended from an exposed soffit.
Integrated service modules can allow the thermal mass of the floor slab to be exposed, moderating peaks in thermal conditions. However, this can mean that additional acoustic absorption measures are required to compensate for the exposed mass, and this might only be possible on walls and floors.
Integrated service modules can permit reduced floor to floor heights, and so can be suitable for spaces with limited height, such as refurbishment projects, where they allow more free space and also give a better perception of space than a full suspended ceiling.
However, their distribution can place some restrictions on the flexibility of layout in the spaces that they serve.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air handling unit.
- Building services.
- Building services engineer.
- Chilled beam.
- Chiller unit.
- CIBSE Case Study Angel Building Refurbishment.
- Fan coil unit.
- Mechanical ventilation.
- Natural ventilation.
- Phase change materials.
- Suspended ceiling.
- Thermal comfort.
- Thermal mass.
 External references
Featured articles and news
What will the General Data Protection Regulations (GDPR) mean for you when they come into force in May?
Business Secretary chairs a new taskforce to monitor and advise on mitigating the impacts of Carillion’s liquidation.
Sir John Armitt is appointed the new chair of the National Infrastructure Commission.
High quality and high density homes - is it what we need or is it storing up trouble?
Government announces its intention to strengthen planning rules to protect music venues and neighbours.
National Audit Office reports that there is little evidence that PFI offers better value than other forms of contracting.
What is liquidation and how does it apply to contractors in the construction industry?
Scrutiny is placed on Carillion's controversial 2013 decision to extend subcontractor payment terms to 120 days.
RSHP unveil their involvement in a boundary crossing which will provide a new entry point into Hong Kong.
With PFI currently under the spotlight due to Carillion, this introductory article explains what they are.
Estimates suggest that up to 30,000 small firms could be at risk of non-payment as a result of Carillion's collapse.