- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 29 Oct 2014
Fan coil unit
Air handling units (AHU, sometimes referred to as ‘air handlers’) form part of the heating, ventilating and air conditioning system (HVAC) that supplies, circulates and extracts air from buildings. Generally, they are connected to the ductwork that supplies air to and extracts air from the interior and can provide ventilation, heating, cooling, humidity control and filtration. For more information see Air handling unit.
Fan coil units (FCU) consist of only a fan and a heating or cooling element, are located within the space they are serving, and are generally not connected to ductwork. They may either just recirculate internal air, in which case a separate ventilation system is required, or may introduce s proportion of ‘fresh’ air that is mixed with the recirculated air.
Where fan coil units are supplied with chilled water and hot water from central boilers and chillers they are generally referred to as two pipe (either heating or cooling) or four pipe (both heating and cooling) units.
Where the heating and cooling is provided locally, they may be referred to as variable refrigerant volume (VRV) or variable refrigerant flow (VRF) systems. Here, refrigerant is circulated between one or more fan coil units and is connected to an external heat exchanger. These systems may be more prone to refrigerant leakage than units that are connected to hermetically-sealed central chillers.
Fan coin units are relatively compact and straightforward to install. However, they require regular maintenance to ensure continued efficient operation.
When a fan coil unit cools air, it will generally cause condensation which must be collected and drained or pumped away.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air handling unit.
- Building services.
- Building services engineer.
- Chilled beam.
- Chiller unit.
- Constant air volume.
- Mechanical ventilation.
- Mechanical and electrical (M&E).
- Natural ventilation.
- Thermal comfort.
- Variable air volume.
- Variable refrigerant flow.
 External references.
Featured articles and news
Gustavo Giovannoni’s role in integrating modern planning requirements into historic town centres.
Against Hackitt's recommendations, the government are to consult on combustible cladding ban.
People or density - can we create urban liveability at ever-increasing densities?
3D printing is the computer-controlled sequential layering of materials to create 3D shapes.
Hackitt review calls for a radical rethink of the whole system and how it works.
Life cycle assessment is used to total up the environmental impact of a product’s supply chain. But why building LCA?
The government warns building owners of a performance issue with Grenfell fire doors.
Ramboll discusses how digitisation is contributing to how they design, engineer and construct in new and different ways.
'Carillion could happen again, and soon' is the stark warning from the heavily critical final report into Carillion's collapse.
In the wake of British architect Will Alsop's death, read about one of his most distinctive buildings.