Fan coil unit
Air handling units (AHU, sometimes referred to as ‘air handlers’) form part of the heating, ventilating and air conditioning system (HVAC) that supplies, circulates and extracts air from buildings. Generally, they are connected to the ductwork that supplies air to and extracts air from the interior and can provide ventilation, heating, cooling, humidity control and filtration. For more information see Air handling unit.
Fan coil units (FCU) consist of only a fan and a heating or cooling element, are located within the space they are serving, and are generally not connected to ductwork. They may either just recirculate internal air, in which case a separate ventilation system is required, or may introduce s proportion of ‘fresh’ air that is mixed with the recirculated air.
Fan coil units can be wall-mounted, freestanding or ceiling-mounted and may be concealed in ceiling voids. They may be controlled by local thermostats or by a building management system (BMS).
Due to their simplicity, fan coil units are more economical to install than ducted air handling units. However, they can be noisy and can create vibrations because the fan is in the occupied space.
Where fan coil units are supplied with chilled water and hot water from central boilers and chillers they are generally referred to as two pipe (either heating or cooling) or four pipe (both heating and cooling) units.
Where the heating and cooling is provided locally, they may be referred to as variable refrigerant volume (VRV) or variable refrigerant flow (VRF) systems. Here, refrigerant is circulated between one or more fan coil units and is connected to an external heat exchanger. These systems may be more prone to refrigerant leakage than units that are connected to hermetically-sealed central chillers.
Fan coin units are relatively compact and straightforward to install. However, they require regular maintenance to ensure continued efficient operation.
When a fan coil unit cools air, it will generally cause condensation which must be collected and drained or pumped away.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air handling unit.
- Building services.
- Building services engineer.
- Chilled beam.
- Chiller unit.
- Constant air volume.
- Mechanical ventilation.
- Mechanical and electrical (M&E).
- Natural ventilation.
- Thermal comfort.
- Variable air volume.
- Variable refrigerant flow.
 External references.
Featured articles and news
Government publishes details of £500bn investment pipeline in infrastructure, described as the 'most comprehensive ever'.
Top of new skyscraper trimmed down by 30m to avoid interfering with City Airport flights.
A new concept unveiled to tackle the lack of sports facilities in inner cities.
'Open hand' designs revealed for a new entertainment complex in China.
Modernist architecture and its many international variations explained.
BRE support Europe-wide strategic heating plans for local and national authorities.
Work set to begin on 'one of America's greatest parks', which will be 10 times bigger than Central Park.
One of our most popular articles - RSHP's Mike Davies writes about the concept design process.
As Cuba mourn the death of Castro, major renovation of this symbolic landmark may be a reflection of the country's fresh start.
How cannabis plants are used to create an alternative building material with plenty of advantages.