Fan coil unit
Air handling units (AHU, sometimes referred to as ‘air handlers’) form part of the heating, ventilating and air conditioning system (HVAC) that supplies, circulates and extracts air from buildings. Generally, they are connected to the ductwork that supplies air to and extracts air from the interior and can provide ventilation, heating, cooling, humidity control and filtration. For more information see Air handling unit.
Fan coil units (FCU) consist of only a fan and a heating or cooling element, are located within the space they are serving, and are generally not connected to ductwork. They may either just recirculate internal air, in which case a separate ventilation system is required, or may introduce s proportion of ‘fresh’ air that is mixed with the recirculated air.
Fan coil units can be wall-mounted, freestanding or ceiling-mounted and may be concealed in ceiling voids. They may be controlled by local thermostats or by a building management system (BMS).
Where fan coil units are supplied with chilled water and hot water from central boilers and chillers they are generally referred to as two pipe (either heating or cooling) or four pipe (both heating and cooling) units.
Where the heating and cooling is provided locally, they may be referred to as variable refrigerant volume (VRV) or variable refrigerant flow (VRF) systems. Here, refrigerant is circulated between one or more fan coil units and is connected to an external heat exchanger. These systems may be more prone to refrigerant leakage than units that are connected to hermetically-sealed central chillers.
Fan coin units are relatively compact and straightforward to install. However, they require regular maintenance to ensure continued efficient operation.
When a fan coil unit cools air, it will generally cause condensation which must be collected and drained or pumped away.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air handling unit.
- Building services.
- Building services engineer.
- Chilled beam.
- Chiller unit.
- Constant air volume.
- Mechanical ventilation.
- Mechanical and electrical (M&E).
- Natural ventilation.
- Thermal comfort.
- Variable air volume.
- Variable refrigerant flow.
 External references.
Featured articles and news
CEOs and high-level executives explain who they expect to be the most successful players in the future of construction.
What are package contracts and how are they broken down? Find out in our introductory article.
Identifying sustainable shoreline protection solutions in the face of rising sea levels and storms in the US.
Budget documents state modern methods of construction will be favoured for public infrastructure schemes from 2019.
A walk-through exhibition of an emergency humanitarian shelter is officially opened at BRE's Innovation Park.
How to work safely on a construction site during winter.
Housing is the big winner in Chancellor Philip Hammond's Autumn Budget.
The winner of our BSRIA competition, Tomorrow's challenges in today's buildings, is.... Bob Hendrikx. A big thank you to everyone that took part.
Committee of MPs accuses government of dealing billpayers a 'bad hand' over the guaranteed power price.
In 1992, the Joint Fire Code was first published. What influence does it still have on construction sites today?
"Companies will have to adapt or go out of business" - how are virtual reality and big data disrupting digital construction?
International Well Building Institute and BRE collaborate on multiple levels to advance human health through better buildings.
"The industry has tried moving away from prescriptivism to focus on performance, but maybe that’s no longer working".