Fan coil unit
Air handling units (AHU, sometimes referred to as ‘air handlers’) form part of the heating, ventilating and air conditioning system (HVAC) that supplies, circulates and extracts air from buildings. Generally, they are connected to the ductwork that supplies air to and extracts air from the interior and can provide ventilation, heating, cooling, humidity control and filtration. For more information see Air handling unit.
Fan coil units (FCU) consist of only a fan and a heating or cooling element, are located within the space they are serving, and are generally not connected to ductwork. They may either just recirculate internal air, in which case a separate ventilation system is required, or may introduce s proportion of ‘fresh’ air that is mixed with the recirculated air.
Fan coil units can be wall-mounted, freestanding or ceiling-mounted and may be concealed in ceiling voids. They may be controlled by local thermostats or by a building management system (BMS).
Due to their simplicity, fan coil units are more economical to install than ducted air handling units. However, they can be noisy and can create vibrations because the fan is in the occupied space.
Where fan coil units are supplied with chilled water and hot water from central boilers and chillers they are generally referred to as two pipe (either heating or cooling) or four pipe (both heating and cooling) units.
Where the heating and cooling is provided locally, they may be referred to as variable refrigerant volume (VRV) or variable refrigerant flow (VRF) systems. Here, refrigerant is circulated between one or more fan coil units and is connected to an external heat exchanger. These systems may be more prone to refrigerant leakage than units that are connected to hermetically-sealed central chillers.
Fan coin units are relatively compact and straightforward to install. However, they require regular maintenance to ensure continued efficient operation.
When a fan coil unit cools air, it will generally cause condensation which must be collected and drained or pumped away.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air handling unit.
- Building services.
- Building services engineer.
- Chilled beam.
- Chiller unit.
- Constant air volume.
- Mechanical ventilation.
- Mechanical and electrical (M&E).
- Natural ventilation.
- Thermal comfort.
- Variable air volume.
- Variable refrigerant flow.
 External references.
Featured articles and news
ICE look at what engineers can do to help ensure the UN's Sustainable Development Goals can be achieved.
Rogers Stirk Harbour and Partners win RIBA National Award for their British Museum extension.
The story so far.
Here is our list of the top 25 buildings in London. Do you agree with our selection?
A blueprint for the construction industry from Canada's west coast.
China's elaborate idea for a mass-transport system has been abandoned.
Read this article about the theories that characterise life in the hyperreal post-modern city.
Polyisocyanurate (PIR) insulation and how it was tested.
"We can’t sustain low density suburbs, density isn't a choice, it's a necessity." - Read our interview with the award-winning social housing architect Peter Barber.
Conservation area designation can be crucial, but treatment of individual parks varies considerably.
ICE publish new NEC4 Design, Build and Operate contract.
Report states $2 trillion is needed over the next 10 years to fix American roads.
What is the client's strategic brief for construction projects?
Read the story behind the world's most iconic festival stage, Glastonbury's Pyramid Stage.
Read the story of Ronan Point, another disastrous event which had profound consequences for the construction industry.