- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 17 Oct 2018
Air handling unit AHU
To help develop this article, click 'Edit this article' above.
Air handling units can be supplied in a range of sizes, and with a variety of capabilities, but typically they comprise an insulated box that forms the housing for; filter racks or chambers, a fan (or blower), and sometimes heating elements, cooling elements, sound attenuators and dampers (that can be operated manually or automatically to regulate or prevent specific air flows). In some situations, such as in swimming pools, air handling units might include dehumidification.
Generally, air handling units will be connected to the ductwork within the building that supplies air to and extracts air from the interior, but they can be used to supply and extract air direct to a space, or they may be located on a roof (rooftop units or RTU).
Air handling units can be used to re-circulate a proportion of ‘stale’ air within a building, mixing this with fresh air to reduce the amount of air conditioning that is required. They can also include heat recovery, recovering heat from return air and using it to warm the supply air.
Fans may be single speed, may have a range of set speeds, or may be variable frequency drive. Flow rates may also be controlled by inlet vanes or outlet dampers.
Air handling units generate noise (and vibration) which can be disruptive, and this can be compounded where ductwork passes between acoustically separate spaces. In this case, acoustic attenuators might be used. In addition, vibration can be generated. This vibration can be isolated by inserting flexible sections between the unit and ductwork and by isolating the unit from the building structure.
Where air handling units are located outside buildings, they can be the source of complaints by neighbours because of the noise and vibration they generate and sometimes because of odours they expel (typically where they are serving kitchens). It is important that these units are properly designed, installed and maintained to minimise this disturbance.
‘Wet’ systems, that include water evaporative cooling, can present a hazard to health. Businesses using such systems are required to carry out a risk assessment and put in place procedures to ensure there is no risk to public health.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air conditioning inspection.
- Chiller unit.
- Chilled water.
- CIBSE Case Study London Olympic Aquatics Centre.
- Cooling systems for buildings.
- Cooling tower design and construction.
- Constant air volume.
- Evaporative cooling.
- Face velocity.
- Fan coil unit.
- Mechanical ventilation.
- Natural ventilation.
- Thermal comfort.
- Underfloor air distribution.
- Variable air volume VAV.
- Variable refrigerant flow VRF.
 External references
Featured articles and news
A form of procurement where the contractor provides a single point of contact for a supply chain.
A month after the devastating fire, emergency reconstruction works are underway.
The London Build Expo is hosting a Diversity in Construction panel and networking session on October 24.
Analysis can help develop a specification, but must not lead to inappropriate specifications being accepted.
Dos and don'ts for creating a smart home.
New ICE publication recommends pay-as-you-go tax to fund roads and other financing options.
BSRIA launches a White Paper on wearable technology and wellbeing in buildings.
Have the pressures of the market shredded the core values of professionalism?
Lead times are a measure of the amount of time that elapses between initiating and completing a construction process.