- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 05 Jul 2019
Air conditioning inspection
See Also: Air conditioning inspection procedure.
The EU Directive on the energy performance of buildings was adopted in 2002. It was intended to improve the energy efficiency of buildings, reduce carbon emissions and reduce the impact of climate change.
The requirements were originally introduced in England and Wales by the Energy Performance of Buildings (Certificates and Inspections) (England and Wales) Regulations 2007. Implementation in England and Wales was completed on 1 October 2008. Energy performance is a devolved matter in Scotland and Northern Ireland.
A recast of the Energy Performance of Buildings Directive was adopted in 2010 and on 9 January 2013, the Energy Performance of Buildings (England and Wales) Regulations 2012 took effect. This consolidated and revoked all previous regulations.
The regulations require that:
- Energy performance certificates (EPC's) are produced for certain dwellings and non dwellings.
- Display energy certificates (DEC's) are produced for large public buildings.
- Air conditioning systems above a certain size are inspected.
 Air conditioning inspections
The Department for Communities and Local Government (CLG) has set out how to apply the regulations requiring air conditioning inspections in, Improving the energy efficiency of our buildings, A guide to air conditioning inspections for buildings, December 2012.
An air conditioning system is defined in the guide as, ‘a combination of all components required to provide a form of air treatment in which the temperature is controlled, or can be lowered, and includes systems which combine such air treatment with the control of ventilation, humidity and air cleanliness’. This includes fixed, self-contained systems, such as split systems and centralised systems. Mechanical ventilation systems that provide no mechanical cooling, but serve spaces that are cooled by other means are included. Any components contained in air conditioning systems that are only intended to provide heating are excluded.
All air conditioning systems with an effective rated output of more than 12kw must be inspected by an energy assessor. This includes systems consisting of individual units which are less than 12kW but whose combined effective rated output is more than 12kW.
The purpose of inspecting air conditioning systems is to improve efficiency, reduce energy consumption, reduce operating costs and reduce carbon emissions. The energy assessor is also required to confirm that necessary checks have been undertaken to ensure there is no Legionella risk as required by the Health (Legionella) Regulations 2001.
An inspection report is prepared to provide the building owner or manager with information about the efficiency of the air conditioning systems, to provide advice on how to improve the energy efficiency of the system, to identify opportunities to save energy and to reduce operating costs. There is no legal requirement to act on the recommendations.
The air conditioning inspection report must be kept in a safe place. The guide suggests that the building log book is the most suitable place to keep records of air conditioning inspections, along with other inspection results such as fluorinated greenhouse gas (F gas) inspections.
Local weights and measures authorities are responsible for enforcing the requirements. The penalty for failing to having an air conditioning inspection report is £300. A further penalty of £200 can be issued for failure to provide a copy of the air conditioning inspection report when requested.
 Related articles on Designing Buildings Wiki
- Accredited energy assessor.
- Africa tops world AC growth forecasts.
- Air conditioning inspection procedure.
- Air conditioning.
- Air conditioning in non-domestic buildings.
- BREEAM Impact of refrigerants.
- Building log book.
- Display energy certificate.
- Energy performance certificate.
- Energy Performance of Buildings Directive.
- F gases.
- French air-conditioning market due to soar to new levels.
- Greenhouse gases.
- How to Use Your Air Conditioning Energy Assessments to Reduce Energy Costs.
- R22 phase out.
- Refrigerant selection.
Featured articles and news
Our servers have reached another milestone. Why not write an article and be seen by our 6.5 million users.
RSHP celebrates competition win in Paris.
All about approved inspectors.
Whilst apparently confusing, German conservation is actually not that different.
The rise and fall of council housing. Book review.
Drivers of change in global heating markets.
11 interesting facts about the use and nature of the material.
Will politicians ultimately fail to tackle Britain's structural challenges?
How self-certification can save time and money.
CIBSE updates Fire Safety Engineering guidance.
EA finds England's water companies are simply unacceptable.