Variable refrigerant flow VRF
It was first developed by Daikin Industries in Japan, under the trade name ‘variable refrigerant volume’ (VRV), but is now widely used throughout the world under the generic name ‘variable refrigerant flow’ (VRF). VRF systems are becoming increasingly popular as they can be more efficient, more compact and offer greater flexibility than other HVAC systems.
VRF systems are based on the flow of refrigerant between an external condensing unit and multiple internal evaporators (typically fan coil units). Each internal evaporator serves a different thermal zone within the building, and the flow of refrigerant to each evaporator is adjusted depending on the local requirement. This gives a great deal of flexibility, and as the output of the outdoor condenser adjusts to match the total internal demand, it allows the systems as a whole to operate at optimum efficiency.
Very broadly, VRF systems can be two-pipe or three pipe systems:
- Two pipe systems can provide either cooling or heating (heat pump systems) to all of the zones.
- Three pipe systems, can provide heating and cooling simultaneously, heating some zones and cooling others, with heat recovery enabling heat from zones requiring cooling to be used to heat zones that require heating. Whilst this has a greater capital cost, the heat recovery allows very efficient operation and so lower operating costs.
VRF systems are best suited to buildings with multiple spaces, varying heating and cooling demand and the need for good local control, such as hotels, where some rooms may be unoccupied whilst others have a very high thermal demand. Because of their limited space requirements (depending on how ventilation is provided) compared to some other systems, they may also be suited to retrofitting older buildings.
They may be less suited to large uniform spaces such as gymnasiums or theatres.
 Related articles on Designing Buildings Wiki
Featured articles and news
IHBC book review: Charles Barry’s monumental struggle to rebuild the Houses of Parliament.
Read about RSHP's British Museum extension which has been shortlisted for the 2017 Stirling Prize.
Read our introductory article to building a house extension.
More updates from DCMS about the large-scale testing of cladding systems and the number of buildings affected.
UandI secure resolution to grant planning consent for major new regeneration project.
IHBC article considers how heritage is dealt with when infrastructure schemes are authorised.
It was the tallest structure in the world for 3,800 years, but to this day the exact construction techniques are a mystery.
Shortlist for the industry's most coveted award announced.
Government responds to Mark Farmer's review of industry, rejecting the call for a levy on clients.
Peter Hansford to examine what wider lessons can be learned from the fire.
Every project is subject to uncertainty. How can construction better understand uncertainty for performance improvement?
MAD Architects reveal their designs for a futuristic campus for electric car manufacturer.
Homebuyers could borrow more with better forecasting of energy bills, according to industry consortium's new report.