- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 03 Aug 2021
Variable refrigerant flow VRF
It was first developed by Daikin Industries in Japan, under the trade name ‘variable refrigerant volume’ (VRV), but is now widely used throughout the world under the generic name ‘variable refrigerant flow’ (VRF). VRF systems are becoming increasingly popular as they can be more efficient, more compact and offer greater flexibility than other HVAC systems.
VRF systems are based on the flow of refrigerant between an external condensing unit and multiple internal evaporators (typically fan coil units). Each internal evaporator serves a different thermal zone within the building, and the flow of refrigerant to each evaporator is adjusted depending on the local requirement. This gives a great deal of flexibility, and as the output of the outdoor condenser adjusts to match the total internal demand, it allows the systems as a whole to operate at optimum efficiency.
- Two pipe systems can provide either cooling or heating (heat pump systems) to all of the zones.
- Three pipe systems, can provide heating and cooling simultaneously, heating some zones and cooling others, with heat recovery enabling heat from zones requiring cooling to be used to heat zones that require heating. Whilst this has a greater capital cost, the heat recovery allows very efficient operation and so lower operating costs.
VRF systems are best suited to buildings with multiple spaces, varying heating and cooling demand and the need for good local control, such as hotels, where some rooms may be unoccupied whilst others have a very high thermal demand. Because of their limited space requirements (depending on how ventilation is provided) compared to some other systems, they may also be suited to retrofitting older buildings.
They may be less suited to large uniform spaces such as gymnasiums or theatres.
 Related articles on Designing Buildings Wiki
- 2021 UK HVAC trends: winners and losers.
- Air conditioning.
- Air handling unit.
- Building services.
- Chilled beam.
- Chiller unit.
- Cooling systems for buildings.
- Constant air volume.
- COVID-19 and the US HVAC sector.
- Cross ventilation.
- Fan coil unit.
- Heat pump.
- Mechanical ventilation.
- Natural ventilation.
- Thermal comfort.
- US among top 2020 global variable refrigerant flow markets.
- Variable air volume.
Featured articles and news
Temperature in buildings, explained on DB
Main barrier to entering the profession, new study reveals.
On Levelling-Up and Regeneration Bill.
Over 70 managers and organisations shortlisted for the 14 awards.
From biometric to electrical current, chemical and more.
Changes are due to come into force on 1st October 2022.
Heed advice and insight of this report IPA tells the government.
From the Commonwealth Association of Architects.
For the Levelling Up, Housing & Communities Committee.
BSRIA's Technical Director reflects on recent weather patterns.
A national valuation to fund old-age pensions.
The world’s largest Commonwealth memorial to the missing.
Long after the end of the defects liability period.
Occupant satisfaction and wellbeing in buildings.
From the simple to the complex.
And the UK Government guidelines.
Commitment agreed to by major built environment bodies.
Electrical skills, low carbon, high-tech and the building services revolution.
Ultra-deep drilling with millimeter-wave beam technology.
Looking at the built environment from space.
BSI standards 8671, 8672 and 8673.
Bringing life to burial grounds.
From failed modernism to twenty-minute neighbourhoods.
The gates process and change control.