- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 13 Sep 2018
Cooling systems for buildings
To help develop this article, click ‘Edit this article’ above.
It can be necessary to provide cooling to buildings during warm weather, or where there are significant thermal gains (such as solar gain, people and equipment). This cooling is sometimes referred to as comfort cooling. Cooling may also be necessary for refrigeration or for some industrial processes.
Passive or 'natural' cooling can be provided by:
Removes warm internal air and replaces it with cooler external air. See Natural ventilation for more information.
Active cooling can be provided by:
 Earth-to-air heat exchanger (ground coupling)
This draws ventilation supply air through buried ducts or tubes (sometimes referred to as earth tubes). As the temperature of the ground below 3 m is practically constant, it can be use to substantially reduce ambient air temperature fluctuations, with the incoming air being heated in the winter and cooled in the summer.
See Earth-to-air heat exchanger for more information.
 Open or closed loop water-to-air heat exchanger
See Ground energy options for more information.
 Mechanical, or forced ventilation, driven by fans
See Mechanical ventilation for more information.
Chilled water is typically provided by chiller units using absorption refrigeration or compression refrigeration. It can then be used to provide cool air, in air handling units (to be ducted around the building), chilled beams, chilled ceilings, and so on. Chiller units use a refrigerant that boils at a low temperature and pressure, removing heat from the chilled water, and then condenses to release that heat, which is rejected to the outside (or recovered).
See Refrigerants for more information.
Refrigerants can be used to provide cooling directly to spaces in variable refrigerant flow (VRF) systems. This is based on the flow of refrigerant between an external condensing unit and multiple internal evaporators (typically fan coil units).
See Variable refrigerant flow for more information.
This can be provided by simple systems, such as misting fans and by spraying water over the roof of a building, or by more complex packaged units that draw hot, dry air through a continually dampened pad and supply cool, humid air to the building.
Indirect evaporative cooling can be provided by the incorporation of heat exchangers, by the use of cooling towers, or by spraying water over the cooling coils of conventional chiller units. Typically, evaporative cooling is best suited to hot, dry climates.
See Evaporative cooling for more information.
See Thermal storage for cooling for more information.
Active cooling might be provided as part of a heating, ventilation and air conditioning system (HVAC) which may also include air filtration and humidity control. The cooling process itself can result in dehumidification, as cool air is less able to ‘hold’ moisture than warm air. The term air conditioning is sometimes taken to mean control over air temperature and humidity, rather than just temperature control in the case of comfort cooling.
NB: Direct evaporative cooling results in humidification of air.
 Find out more
 Related articles on Designing Buildings Wiki
- Absorption refrigeration.
- Air conditioning.
- Air handling unit.
- BREEAM Impact of refrigerants.
- Chiller unit.
- Chilled water.
- Cooling degree days.
- Cooling tower.
- Cooling tower design and construction.
- Corrosion in heating and cooling systems.
- Data centre cooling.
- Evaporative cooling.
- Night-time purging.
- Passive building design.
- Passive ventilation.
- Thermal labyrinth.
- Thermal storage for cooling.
Featured articles and news
Do you understand the different types of stone and which ones you should use where?
Why a wellbeing strategy is vital for property managers.
An ECA briefing for members about the commercial implications of leaving the EU.
A crucial moment on any project - and fraught with danger.
The performance gap from a Northern Ireland perspective.
Book review: Buildings of protestant nonconformity.
Design and testing for health and wellbeing - free download from BRE.
Retention in construction contracts.
Campaign for the reform of cash retentions.
The key points for the construction industry and BSRIA's response.
How to make roads safer: the debate continues.