Cooling systems for buildings
To help develop this article, click ‘Edit this article’ above.
It can be necessary to provide cooling to buildings during warm weather, or where there are significant thermal gains (such as solar gain, people and equipment). This cooling is sometimes referred to as comfort cooling. Cooling may also be necessary for refrigeration or for some industrial processes.
Passive or 'natural' cooling can be provided by:
- Natural ventilation, which removes warm internal air and replaces it with cooler external air. See natural ventilation for more information.
- Thermal mass, which can be used to even out variations in internal and external conditions, absorbing heat as temperatures rise and releasing it as they fall. See thermal mass for more information
- Evaporative cooling, such as moisture evaporating from the surface of a building, or the inclusion of water features such as ponds. See evaporative cooling for more information.
- Devices such as shading, reflective surfaces, insulation, green roofs and so on, which whilst they do not in themselves provide cooling, do reduce thermal gains.
Active cooling can be provided by:
- Earth-to-air heat exchanger (ground coupling), which draws ventilation supply air through buried ducts or tubes (sometimes referred to as earth tubes). As the temperature of the ground below 3m is practically constant, it can be use to substantially reduce ambient air temperature fluctuations, with the incoming air being heated in the winter and cooled in the summer. See Earth-to-air heat exchanger for more information.
- Open or closed loop water to air heat exchangers, which exploit the relatively stable temperature of the earth to provide water that can cool in the summer and heat in the winter. See Ground energy options for more information.
- Mechanical, or forced ventilation, driven by fans. This might be cooled below outside air temperature by the use of refrigerants, or by thermal mass, such as thermal labyrinths, or by night time purging. See mechanical ventilation for more information.
- Chilled water. Chilled water is typically provided by chiller units using absorption refrigeration or compression refrigeration. It can then be used to provide cool air, in air handling units (to be ducted around the building), chilled beams, chilled ceilings and so on. Chiller units use a refrigerant that boils at a low temperature and pressure, removing heat from the chilled water, and then condenses to release that heat, which is rejected to the outside (or recovered). See Refrigerants for more information. NB The use of chilled water to cool the building fabric itself is sometimes described as 'active thermal mass'.
- Refrigerants can be used to provide cooling directly to spaces in variable refrigerant flow (VRF) systems. This is based on the flow of refrigerant between an external condensing unit and multiple internal evaporators (typically fan coil units). See variable refrigerant flow for more information.
- Evaporative cooling can be provided by simple systems, such as misting fans and by spraying water over the roof of a building, or by more complex packaged units that draw hot, dry air through a continually dampened pad and supply cool, humid air to the building. Indirect evaporative cooling can be provided by the incorporation of heat exchangers, by the use of cooling towers, or by spraying water over the cooling coils of conventional chiller units. Typically, evaporative cooling is best suited to hot, dry climates. See evaporative cooling for more information.
- Ice can be used as an effective means of thermal storage, storing ‘coolth’ in colder parts of the day to provide cooling during warmer parts of the day. See Thermal storage for cooling for more information.
Active cooling might be provided as part of a heating, ventilation and air conditioning system (HVAC) which may also include air filtration and humidity control. The cooling process itself can result in dehumidification, as cool air is less able to ‘hold’ moisture than warm air. The term air conditioning is sometimes take to mean control over air temperature and humidity, rather than just temperature control in the case of comfort cooling.
NB Direct evaporative cooling results in humidification of air.
NB Night time purging, and ground coupling are sometimes considered to be passive, rather than active systems.
 Related articles on Designing Buildings Wiki
- Absorption refrigeration.
- Air conditioning.
- Air handling unit.
- Chiller unit.
- Chilled water.
- Cooling degree days.
- Cooling tower.
- Cooling tower design and construction.
- Corrosion in heating and cooling systems.
- Data centre cooling.
- Evaporative cooling.
- Mechanical, electrical and plumbing MEP.
- Mechanical ventilation.
- Night-time purging.
- Passive building design.
- Passive ventilation.
- Thermal labyrinth.
- Thermal storage for cooling.
Featured articles and news
UK-GBC green paper proposes more powers for cities on new-build housing.
The Pompidou Centre – not a monument but an event.
The Chartered Institute of Building restructures and launches 29 new local hubs.
Designing Buildings Wiki talks to the founder of the world's first indoor biophilic gym, now open in London.
£1.3bn Swansea Bay project to be backed as a 'pathfinder' for other tidal lagoon projects.
Designs released for a proposed Las Vegas stadium to entice the Oakland Raiders.
Have a look at these award-winning concept designs for a thermal bath in Latvia.
Flagship project no longer "a going concern" according to the Garden Bridge Trust as funding slows.
How the work of 20th century urbanist Jane Jacobs continues to resonate in light of the government's garden village plans.
New landmark for the Ecuadorean capital of Quito utilises a sinuous facade mold system.
Have a look at this glass piano and violin building in China.