- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 24 Sep 2020
A thermal labyrinth decouples thermal mass from the occupied space, usually by creating a high thermal mass concrete undercroft with a large surface area. Decoupling the thermal mass means it can be cooled to a lower temperature than if it was in the occupied space.
The labyrinth layout needs to balance optimum thermal storage with the air resistance of the system. Creating air turbulence, by increasing the roughness and incorporating bends, improves heat transfer. However, incorporating too many bends may increase the air resistance beyond the point where the system can be part of a passive or naturally ventilated scheme.
As labyrinths are often constructed directly beneath a building, only the sides and floor of the labyrinth are in contact with the earth and the top of the labyrinth is directly coupled with the building. This means that the labyrinth needs to be well insulated from the building to prevent heat transfer.
The earth contact of the labyrinth gives the benefit of steady ground temperatures, however, the undisturbed ground temperature cannot be used in calculations, as it will be affected by the presence of the building and the operation of the labyrinth. This means that optimisation of the design requires a complete thermal simulation of the system.
Regular inspection and cleaning of the labyrinth are recommended, although thermal labyrinths are generally virtually maintenance free. The major cost that can be incurred is when fan power is required to supply air through the labyrinth.
Thermal labyrinths can be integrated into a building's structure to provide free cooling in the summer and pre-heating of air in the winter. They can have high capital costs, but over the life of a building,
can yield substantial savings by reducing peak demand for cooling and heating.
This article was created by --Buro Happold, 17 March 2013, based on a 2008 article in 'Patterns'.
 Related articles on Designing Buildings Wiki
- Air source heat pumps.
- Dynamic thermal modelling of closed loop geothermal heat pump systems.
- Earth-to-air heat exchangers.
- Geothermal energy.
- Geothermal pile foundations.
- Ground energy options.
- Ground pre-conditioning of supply air.
- Ground source heat pumps.
- Thermal mass.
- Trombe wall.
 External references
- Ingenia, Going underground September 2006.
Featured articles and news
Revised guide to competition rules available.
Brick slip soffit systems and intricate brick features.
An innovative engineering approach could have had tragic consequence for NYC.
Some secrets behind how canals work.
Breaking down possible steps of pre-contract management.
ICE event includes comments from Welsh Government Minister Julie James.
How to write them and what they should include.
Designing Buildings Wiki becomes the world's first website to adopt the new knowledge standard.
Assessing the most beneficial design elements.
Exploring different types of vinyl flooring.
New Government task force will build beauty into reformed planning process.
Five outstanding aspects of the profession.