- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 30 Dec 2021
Ground source heat pumps
The Earth’s internal heat was originally produced during accretion. Since then heat has been produced by the radioactive decay of elements such as uranium, thorium and potassium. Due to its high enthalpy, this type of heat is often harvested in volcanic areas for electricity production and large district heating.
- Open loop
- Closed loop
 Ground source heat pumps
Ground source heat pumps can pump heat from the ground into a building to provide space heating and domestic hot water. For every unit of electricity used to pump the heat, 3-4 units of heat can be produced.
Example of a ground source heat pump system.
There are three important elements to a ground source heat pump system:
- Ground loop. This comprises of lengths of plastic pipe buried in the ground, either in a borehole or a horizontal trench. The pipe is a closed circuit and is filled with a mixture of water and antifreeze, which is pumped round the pipe absorbing heat from the ground.
- Heat pump. Heat pumps are very familiar to us in fridges and air conditioners. A heat pump works by using the evaporation and condensing of a refrigerant to move heat from one place to another. In this case, the evaporator (analogous to the squiggly loop in the cold part of the fridge) takes heat from the water in the ground loop; the condenser (analogous to the hot loop on the back of the fridge) gives up heat to a hot water tank which feeds the distribution system.
- A compressor. This uses electricity, (this is what makes the noise in a fridge) to move the refrigerant around the heat pump. It also compresses the gaseous refrigerant to increase the temperature at which it condenses to that needed for the distribution circuit.
- Heat distribution system. This consists of under floor heating or radiators for space heating and water storage for hot water supply. Some systems can also be used for cooling in the summer.
 Ground source heat pump system efficiency
Alternatively, the Coefficient of Performance (COP) can be calculated by dividing the useful heat output by the electrical energy input. This ratio usually ranges between 3 and 4, making ground source heat pumps extremely convenient for buyers.
Three options are available for the ground loop:
- Straight horizontal
- Spiral horizontal (or 'slinky')
Each has different characteristics appropriate for different types of property. Horizontal trenches can cost less than boreholes, but require greater land area. For 'slinky' coils, a trench of about 10m length will provide approximately 1kW of heating load.
The efficiency of a ground source heat pump system is measured by the Coefficient of Performance (CoP). This is the ratio of the number of units of heat output for each unit of electricity input used to drive the compressor and pump for the ground loop. Typical CoPs range between 2.5-4.The higher end of this range relates to under floor heating, because it works at a lower temperature (30-35°C) than radiators. Based on current fuel prices, assuming a CoP of 3-4, a ground source heat pump can be a cheaper form of space heating than oil, LPG and electric storage heaters. It is however more expensive than mains gas. If grid electricity is used for the compressor and pump, then an economy 7 tariff usually gives the lowest running costs.
The main environmental impacts are:
- Pollution from using grid electricity generated through fossil fuel. Measures can be taken to reduce these impacts - for example, purchasing dual tariff 'green' electricity. However, even if ordinary grid electricity is used to run the compressor, the system will still produce less CO2 emissions than the most efficient condensing gas or oil boiler with the same output.
- Use of refrigerants in the system. Refrigerants are present in ground source heat pump systems and can pose a threat to the environment as they can be toxic, flammable or have a high global warming potential. However, new types and blends of refrigerants with minimal negative impacts are being developed. A correctly fitted system will also greatly reduce the potential for leakage, which is why using a professional installer is highly recommended.
- Absorption heat pump.
- Air source heat pumps.
- BSRIA Compressor Study September 2020 - The Americas and China
- BSRIA domestic hot water heat pumps testing.
- BSRIA global heat pump market 2019.
- Coefficient of Performance CoP.
- Dynamic thermal modelling of closed loop geothermal heat pump systems.
- Earth-to-air heat exchangers.
- EMEA compressor market 2020 - 2023.
- Exhaust air heat pump.
- Geothermal energy
- Geothermal pile foundations.
- Ground energy options.
- Ground preconditioning of supply air.
- Heat pump.
- Mechanical ventilation with heat recovery.
- Renewable energy sources: how they work and what they deliver: Part 3: Electrically driven heat pumps DG 532 3.
- Room-based heat pumps.
- Water-source heat pumps.
- What is diversity in HVAC systems?
 External references
Featured articles and news
Two new research reports published by APM.
50% off APM Associate membership for Designing Buildings users.
A commentary from the insurance perspective.
In brief with further links.
A definitive book on a pioneer of green architecture.
Using heritage as a catalyst for reviving historic centres.
Declaration prioritising sustainable urbanisation adopted.
Some brief words about the actuator.
After 34 years at the Institute.
To support the next generation of engineers.
CIAT reporting from the Competition and Markets Authority.
Making sustainable construction number one priority.
Interview with ECA CEO.
Many provisions came into force on June 28, 2022.
With room to expand.
Refurbishment, Energy Efficiency, Indoor air and process.
Why building acoustic considerations must be non-negotiable.
Aluminium Composite Panels (ACP) is one example.
Inventors and innovators at ICE.
Life, death and art at the Stuart court. Book review.
Real estate, place adaptation and innovation.
Review and comment on the revised draft before July 11.
Write about something you know, help us build and grow !
A blended event and triumphant return.
Mark Reynolds succeeds Andy Mitchell as Co-Chair of CLC