- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 23 Aug 2017
Ground source heat pumps
- Internal heat of the Earth
- Heat from the sun and stored in the ground
 Internal heat of the earth
The Earth’s internal heat was originally produced during accretion. Since then heat has been produced by the radioactive decay of elements such as uranium, thorium and potassium. Due to its high enthalpy, this type of heat is often harvested in volcanic areas for electricity production and large district heating.
 Heat from the sun and stored in the ground
The majority of heat stored right in the Earth’s surface comes from the sun. This heat is widely available, and because of its low enthalpy, it is often harvested for local heat pump applications.
There are two types of systems for utilising heat from the sun stored in the ground by a ground source heat pump:
- Open loop
- Closed loop
 Ground source heat pumps
Ground source heat pumps can pump heat from the ground into a building to provide space heating and domestic hot water. For every unit of electricity used to pump the heat, 3-4 units of heat can be produced.
Example of a ground source heat pump system.
 Ground source heat pump system design
There are three important elements to a ground source heat pump system:
- Ground loop. This comprises of lengths of plastic pipe buried in the ground, either in a borehole or a horizontal trench. The pipe is a closed circuit and is filled with a mixture of water and antifreeze, which is pumped round the pipe absorbing heat from the ground.
- Heat pump. Heat pumps are very familiar to us in fridges and air conditioners. A heat pump works by using the evaporation and condensing of a refrigerant to move heat from one place to another. In this case, the evaporator (analogous to the squiggly loop in the cold part of the fridge) takes heat from the water in the ground loop; the condenser (analogous to the hot loop on the back of the fridge) gives up heat to a hot water tank which feeds the distribution system.
- A compressor. This uses electricity, (this is what makes the noise in a fridge) to move the refrigerant around the heat pump. It also compresses the gaseous refrigerant to increase the temperature at which it condenses to that needed for the distribution circuit.
- Heat distribution system. This consists of under floor heating or radiators for space heating and water storage for hot water supply. Some systems can also be used for cooling in the summer.
 Ground loop options
Three options are available for the ground loop:
- Straight horizontal
- Spiral horizontal (or 'slinky')
Each has different characteristics appropriate for different types of property. Horizontal trenches can cost less than boreholes, but require greater land area. For 'slinky' coils, a trench of about 10m length will provide approximately 1kW of heating load.
 Utilising ground energy
The efficiency of a ground source heat pump system is measured by the Coefficient of Performance (CoP). This is the ratio of the number of units of heat output for each unit of electricity input used to drive the compressor and pump for the ground loop. Typical CoPs range between 2.5-4.The higher end of this range relates to under floor heating, because it works at a lower temperature (30-35°C) than radiators. Based on current fuel prices, assuming a CoP of 3-4, a ground source heat pump can be a cheaper form of space heating than oil, LPG and electric storage heaters. It is however more expensive than mains gas. If grid electricity is used for the compressor and pump, then an economy 7 tariff usually gives the lowest running costs.
 Environmental impacts
The main environmental impacts are:
- Pollution from using grid electricity generated through fossil fuel. Measures can be taken to reduce these impacts - for example, purchasing dual tariff 'green' electricity. However, even if ordinary grid electricity is used to run the compressor, the system will still produce less CO2 emissions than the most efficient condensing gas or oil boiler with the same output.
- Use of refrigerants in the system. Refrigerants are present in ground source heat pump systems and can pose a threat to the environment as they can be toxic, flammable or have a high global warming potential. However, new types and blends of refrigerants with minimal negative impacts are being developed. A correctly fitted system will also greatly reduce the potential for leakage, which is why using a professional installer is highly recommended.
This article was created by --Buro Happold, 17 March 2013.
 Related articles on Designing Buildings Wiki
- Absorption heat pump.
- Air source heat pumps.
- Coefficient of Performance CoP.
- Dynamic thermal modelling of closed loop geothermal heat pump systems.
- Earth-to-air heat exchangers.
- Exhaust air heat pump.
- Geothermal energy
- Geothermal pile foundations.
- Ground energy options.
- Ground preconditioning of supply air.
- Heat pump.
- Mains gas.
- Mechanical ventilation with heat recovery.
- Water-source heat pumps.
 External references
Featured articles and news
This article examines the changing policy commitments and evolving definitions of the zero carbon home.
Researchers believe they may have created a 'game-changing' new form of concrete using graphene.
Grouting refers to the injection of materials into a soil or rock formation to change its physical characteristics.
Part of Designing Buildings Wiki, BREEAM Wiki will advance knowledge sharing for the BRE family of sustainability tools.
From the decorative to the utilitarian, and from the photographed to the forgotten.
New BRE book considers the progression from project-based knowledge creation to whole-life urban knowledge management.
This CIOB article explores the concept of value in building design and construction.
BREEAM and Measurabl announce integration to improve the financial performance of commercial real estate.
Rogers Stirk Harbour + Partners' release new images of soon-to-open 3WTC tower in New York.
A document can be called a bond or a guarantee. Does the name matter and what is the difference between them?
New briefing note is launched focusing on increasing knowledge of housing that promotes health and wellbeing.
Arbitration is a private, contractual form of dispute resolution used in the construction industry.