- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 29 Jul 2022
Radiators are heat exchanging devices and are one of the oldest and most effective ways of heating buildings. Typically, they consist of hollow metal panels through which hot water is pumped. Convector fins may be welded to the panels to increase their effective surface area, allowing more air to come into contact with the metal.
According to British Standards, radiators should be placed on external walls, wherever possible under windows. This is because mounting is easier on external walls and these are usually the coldest parts of a room.
Radiators use the heat from hot water or sometimes steam to warm the surrounding air. The advantage of using steam is that it can flow through pipes under its own pressure without needing pumps. This is useful for large and tall buildings, however, steam is less efficient due to the higher temperatures at which steam systems operate.
Water hammer is a banging sound that can be made by steam pipes and radiators. It is due to some of the steam condensing into water in a horizontal section of the steam piping and pushing the water at high velocity into a pipe fitting.
 Types of radiator
These can be either single or double panels without convector fins, and now largely outdated. The panel refers to the long metal containers that run parallel to the wall. The longer the panel, the larger the heat-emitting surface area, so bigger radiators will emit more heat. A double panel radiator will emit more heat than a single panel radiator of the same length.
- Single panel single convector: One front steel panel and one convector fin.
- Double panel single convector: Two steel panels (front and back) and one convector fin.
- Double panel double convector: Two steel panels (front and back) and two convector fins.
Column radiators are made up of steel tubular columns welded to end pieces at the top and bottom. Column radiators can range from single to four columns in depth. Column radiators are popular for their more traditional appearance.
 LST radiator
An LST radiator has an efficient internal heat emitter in a robust steel enclosure to ensure safety and concealment of pipework and valves. This type of radiator is often found in places where safety concerns are important, such as hospitals, nurseries, schools, care homes, and so on. They do not have sharp corners and maintain a low, safe-to-touch surface temperature, while at the same time delivering the required heat output.
 Skirting board radiator
Radiators should be bled regularly to ensure the efficiency of the central heating system. It is possible to check whether bleeding is necessary by checking for cool spots, especially near the top of the radiator. Bleeding can be done using a bleeding key or flat-heated screwdriver to open a valve at one end of the radiator. This allows the release of the trapped air until liquid starts to escape, at which point the valve should be quickly closed.
- Boiler markets and the green recovery.
- Building heating systems.
- Building services.
- Fan convector.
- Hot water.
- Mechanical, electrical and plumbing MEP.
- Natural convector.
- Plumbing drawing.
- Thermal conduction in buildings.
- Types of heating system.
- Underfloor heating.
Featured articles and news
80 construction leaders and companies from across the UK.
A brief run through essential training tips from a user.
A comprehensive guide from a Cohesive BIM wiki user.
From the basics to the future from our Cohesive BIM wiki.
As electrical sector feels skills shortage bite.
CIOB Academy’s course take-up inked to external factors.
Q and A with self-representing artist, Hannah Shergold.
And publishes three-year strategic plan.
Introducing changes to make it more effective from 2024.
Shortlist announced for 2023 public choice award vote.
The last of the Victorians. Book review.
An exotic name that is shrouded in mystery.
Fropm practice to research and the business of materials.
Terms, histories, theories and practices.
Alteration and everything else before demolition.