Air source heat pumps
Air source heat pumps (ASHPs) use the external air as a heat source to provide heat for buildings.
They work by running a low-temperature, lower pressure refrigerant fluid in heat exchanger coils through the external air. The fluid ‘absorbs’ heat from the air and boils, even at temperatures below 0° C (although the coefficient of performance (COP) decreases with lower temperature). The gas is then compressed, which further increases its temperature. The gas is passed into heat exchanger coils, where it condenses, releasing its latent heat. The process then repeats.
Air source heat pumps can be air-to-water systems (providing hot water for direct use or to supply radiators or underfloor heating systems), or air-to-air systems (providing hot air, either directly into an internal space, or to be distributed by fans throughout a building).
Air source heat pumps can reduce energy consumption, fuel bills and carbon emissions, particularly where there is no mains gas supply, and so alternative heating systems would consume electricity, liquid petroleum gas (LPG), oil, or coal.
They require the siting of one or more units, similar to an air conditioning units, outside the building. This may require planning permission, although in some areas, some installations may be considered to be ‘permitted developments’. Siting is important, as units can generate noise, and an electricity supply is required.
Air-to-water systems are most effective when providing lower-temperature hot water, over a longer period of time, than might be supplied by a conventional boiler. This lower-temperature hot water is appropriate for underfloor heating, or for large radiators. The coefficient of performance drops at higher sink temperatures (the temperature of the supplied water) required for smaller radiators, or for providing hot water. Higher temperature hot water might be better provided by other low-carbon systems such as solar thermal heating.
Because they provide lower-temperature hot water over long durations, they are generally most suitable for highly-insulated, air-tight buildings.
Air source heat pumps are generally low-maintenance and can be cheaper and easier to install and less disruptive than ground source heat pumps although their efficiency may be lower. Ground source heat pumps use a similar process but absorb heat from the ground, by circulating fluid through buried pipes. See ground source heat pump for more information.
Other benefits include; long life, low maintenance requirements, they are not polluting and unlike conventional heating systems they do not use combustible fuels or require flues. However, care must be taken over the selection of refrigerant, and leaks must be prevented.
Air to water heat pumps are be eligible for payments under the government’s Renewable Heat Incentive (RHI) scheme. They were eligible for funding under the Renewable Heat Premium Payment scheme, but this scheme closed on 31 March 2014 when the domestic Renewable Heat Incentive scheme was introduced. It might also be possible to obtain help with domestic installation costs through the Green Deal, however, there has been very poor uptake of the Green Deal, and it is generally considered that better financial deals are available elsewhere.
 Related articles on Designing Buildings Wiki
- Absorption heat pump.
- Coefficient of Performance CoP.
- Combined heat and power CHP.
- Earth-to-air heat exchangers.
- Exhaust air heat pump.
- Geothermal piles.
- Green Deal.
- Ground energy options.
- Ground pre-conditioning of supply air.
- Ground source heat pumps.
- Heat pump.
- Renewable energy.
- Renewable Heat Incentive.
- Solar thermal systems.
- Thermal labyrinths.
- Water-source heat pumps.
- Zero Bills Home.
- Zero carbon homes.
- Zero carbon non-domestic buildings.
 External references
- BSRIA Air-source heat pumps - pros, cons and considerations for specifiers. January 2009.
Featured articles and news
Read about RSHP's British Museum extension which has been shortlisted for the 2017 Stirling Prize.
Read our introductory article to building a house extension.
More updates from DCMS about the large-scale testing of cladding systems and the number of buildings affected.
UandI secure resolution to grant planning consent for major new regeneration project.
IHBC article considers how heritage is dealt with when infrastructure schemes are authorised.
It was the tallest structure in the world for 3,800 years, but to this day the exact construction techniques are a mystery.
Shortlist for the industry's most coveted award announced.
Government responds to Mark Farmer's review of industry, rejecting the call for a levy on clients.
Peter Hansford to examine what wider lessons can be learned from the fire.
Every project is subject to uncertainty. How can construction better understand uncertainty for performance improvement?
MAD Architects reveal their designs for a futuristic campus for electric car manufacturer.
Homebuyers could borrow more with better forecasting of energy bills, according to industry consortium's new report.
Read our introductory article on carbon capture and storage.