- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 16 Sep 2016
To help develop this article, click ‘Edit this article’ above.
Typically, heat exchangers are used to allow heat from liquids or gases to pass to other liquids or gases, without the two coming into direct contact. Essentially they transfer the heat without transferring the fluid that carries the heat.
Heat exchange devices can be used in a number of processes, including:
- Air conditioning systems.
- Heat pumps.
- Heat recovery ventilation.
- Waste water treatment.
- Nuclear and power plants.
- Machinery and engines.
- Specialist energy-saving devices such as energy-efficient showers.
The two most common types of heat exchangers are the 'shell and tube' and 'plate' or 'fin':
- In shell and tube heat exchangers, one fluid flows through a series of metal tubes within a sealed unit while another fluid passes between the tubes. The two fluids can flow in the same direction which is called parallel flow, in opposite directions, known as counter flow or counter current, or they can flow at right angles, known as cross flow.
- Plate or fin heat exchangers consist of metal fins with large surface areas that air passes around. This more open construction can allow easier inspection, cleaning and disassembly. This system is often used for chilled beams or integrated service modules.
Earth-to-air heat exchangers draw ventilation supply air through buried ducts or tubes. As the temperature of the ground below 3m is practically constant, it substantially reduces ambient air temperature fluctuations and can provide space conditioning throughout the year, with the incoming air being heated in the winter and cooled in the summer.
The appropriate heat exchanger can be selected by consideration of:
- Space availability.
- The heat carrying mediums.
- Fluid flow capacity.
- Pressure limits.
- Temperature ranges.
- Thermal performance requirements.
- Requirements for maintenance and repair.
 Find out more
 Related articles on Designing Buildings Wiki
- Absorption heat pump.
- Air conditioning.
- Air source heat pumps.
- Chilled beams.
- Coefficient of Performance CoP.
- Earth-to-air heat exchangers.
- Geothermal pile foundations.
- Ground energy options.
- Ground source heat pumps.
- Heat pump.
- Heat recovery.
- Integrated service module.
- Thermal labyrinths.
- Water source heat pumps.
Featured articles and news
The London Build Expo is hosting a Diversity in Construction panel and networking session on October 24.
Analysis can help develop a specification, but must not lead to inappropriate specifications being accepted.
Dos and don'ts for creating a smart home.
New ICE publication recommends pay-as-you-go tax to fund roads and other financing options.
BSRIA launches a White Paper on wearable technology and wellbeing in buildings.
Have the pressures of the market shredded the core values of professionalism?
Lead times are a measure of the amount of time that elapses between initiating and completing a construction process.
Government releases first tranche of funding for removal of unsafe high-rise cladding.
How to ensure UK transport infrastructure copes with severe winter weather.