- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 03 Mar 2021
Waste heat is a by-product of other applications. It can sometimes be collected (recovered) from those applications and re-used for heating and other purposes as a means to save energy and reduce both running costs and carbon emissions. Without this recovery, the heat energy is simply wasted.
In the urban environment, electrical generators, industrial processes and heat lost through building envelopes are the biggest sources of waste heat. The burning of transport fuels is also a major contributor.
Typical applications which generate waste heat and from which recovery is possible include:
- Boiler combustion gases;
- Domestic, commercial and industrial extract air;
- Hot water discharge (domestic, commercial and industrial);
- Refrigeration plant;
- Power generating plant;
- Lighting systems;
- Combustion engines;
The uses to which recovered heat can be put include:
- Space heating;
- Water heating;
- Pre-heating of combustion air for boilers;
- Ovens and furnaces;
- Pre-heating fresh air in building ventilation systems;
- Drying processes;
- Power generation;
- Heating greenhouses in colder climates.
 Recovering waste heat
In order to reclaim waste heat energy, it has to pass through a lower temperature heat sink, i.e some sort of physical collector which will absorb as much heat as possible from the recovery source and from which the waste energy can be taken. An example is waste heat from air conditioning units stored in a buffer tank to be used for night-time heating.
Ideally, the waste heat source and the sink into which it can be stored temporarily are physically in close proximity. If this is not the case, there are some systems that can be used at a different location or at a different time.
More than half of the input energy used in almost all industrial processes becomes waste heat. Some of this may be converted into electrical energy by a range of methods, one of which involves the use of a thermoelectric device: this works when a change in temperature across a semi-conductor material creates a voltage that causes a flow of electricity.
- QH = QL + W
So, for example, in a gas boiler:
- QH is the heat input to the system (e.g that which may be derived from burning gas)
- W is the useful heat (or work) produced by the system, and
- QL is the useful waste heat.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air handling unit.
- Chiller unit.
- Coefficient of Performance CoP.
- District energy.
- Exhaust air heat pump.
- Geothermal pile foundations.
- Gross calorific value.
- Heat exchanger.
- Heat pump.
- Heat recovery ventilation.
- Mechanical ventilation.
- Types of heating system.
- Variable refrigerant flow.
- Zero Bills Home.
 External references
Featured articles and news
Helping communities preserve and enhance historic environments.
Creating comfortable climates despite extreme temperatures.
Study examines how adjustable arrangements can succeed.
Government announces plans to improve accessibility.
Resource addresses pandemic-related NEC4 contract issues.
Incorporating EDI into the provision of fair access.
Government announces global innovation strategy.
An architectural biography. Book review.
The house where the future king of France lived.
The teacher, architectural technologist and mum offers her insights.
Careful planning needed as supply chain issues continue.
The sensitive conversion of a neglected Cornwall structure.