- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 22 Dec 2017
Water source heat pumps
The fluid ‘absorbs’ this heat and boils, even at temperatures below 0° C (although the coefficient of performance (COP) decreases with lower temperature). The resulting gas is then compressed, which further increases its temperature. The gas is passed into heat exchanger coils, where it condenses, releasing its latent heat. The process then repeats.
Heat pumps can be used to provide hot water, space heating (either by providing hot water for under-floor heating or radiators, or supplying hot air) or other applications such as heating swimming pools.
In the UK, heat pumps are most commonly air-source or ground-source heat pumps. However, the temperature of ground water sources in the UK tends to be fairly constant for most of the year, at between 8 and 12°c. This makes water a more efficient heat source than the outside air, and the heat transfer rate with water is higher than that of air or the ground. In addition, unlike ground-source heat pumps, water-source heat pumps do not require trenches for coils to be laid in, although open loop systems often require filtration.
Closed-loop systems pipe a mixture of water and anti-freeze to a water source such as a lake where it flows through coils or heat exchange panels in the water to exchange heat with it. The heated mixture is then piped to the heat pump and heat exchanged with the refrigerant.
In open-loop systems, water from the source is extracted and piped direct to the heat pump. Heat is then exchanged with the refrigerant and the water then returned to the source. As this involves extraction from and discharge to a water source, it is likely to require an extraction licence and a discharge license from the Environment Agency.
Closed-loop systems can be less efficient than open-loop systems, because of the losses caused by transferring heat between the water source and the fluid in the closed loop. However, they are less restrictive in terms of the danger of freezing, the water quality that can be used, the need for filtration or other forms of water treatment, the possibility of needing to use a corrosion resistant system and the need for licenses. Open-loop systems can also require more pumping.
Care must be taken with closed-loop systems to avoid the potential for the coils or heat exchange panels to be damaged by boats or other activities in or on the water.
Water source heat pumps are generally quiet, unobtrusive and have low maintenance requirements. However, care must be taken to ensure that the water supply is consistent and sufficient throughout the year.
Water-source heat pumps are eligible for payments under the government’s Renewable Heat Incentive (RHI) scheme. Domestic schemes may also be eligible for financing through the green deal, however, there has been very poor uptake of the Green Deal, and it is generally considered that better financial deals are available elsewhere.
 Related articles on Designing Buildings Wiki:
- Absorption heat pump.
- Air source heat pumps.
- Coefficient of Performance CoP.
- Exhaust air heat pump.
- Geothermal pile foundations.
- Green Deal.
- Ground energy options.
- Ground source heat pumps
- Heat pump.
- Mechanical ventilation with heat recovery.
- Renewable Heat Incentive.
- Solar-assisted heat pump.
- Solar thermal heating.
- Thermal labyrinths.
- Water source heat map.
 External references
- YouGen, Heat pumps.
- DECC, Green Deal, Energy Saving Home Improvements.
- DECC,Which energy efficiency improvements qualify for Green Deal Finance? June 2012.
Featured articles and news
This article examines the changing policy commitments and evolving definitions of the zero carbon home.
Researchers believe they may have created a 'game-changing' new form of concrete using graphene.
Grouting refers to the injection of materials into a soil or rock formation to change its physical characteristics.
Part of Designing Buildings Wiki, BREEAM Wiki will advance knowledge sharing for the BRE family of sustainability tools.
From the decorative to the utilitarian, and from the photographed to the forgotten.
New BRE book considers the progression from project-based knowledge creation to whole-life urban knowledge management.
This CIOB article explores the concept of value in building design and construction.
BREEAM and Measurabl announce integration to improve the financial performance of commercial real estate.
Rogers Stirk Harbour + Partners' release new images of soon-to-open 3WTC tower in New York.
A document can be called a bond or a guarantee. Does the name matter and what is the difference between them?
New briefing note is launched focusing on increasing knowledge of housing that promotes health and wellbeing.
Arbitration is a private, contractual form of dispute resolution used in the construction industry.