- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 30 Dec 2021
Water source heat pumps
The fluid ‘absorbs’ this heat and boils, even at temperatures below 0° C (although the coefficient of performance (COP) decreases with lower temperature). The resulting gas is then compressed, which further increases its temperature. The gas is passed into heat exchanger coils, where it condenses, releasing its latent heat. The process then repeats.
Heat pumps can be used to provide hot water, space heating (either by providing hot water for under-floor heating or radiators, or supplying hot air) or other applications such as heating swimming pools.
In the UK, heat pumps are most commonly air-source or ground-source heat pumps. However, the temperature of ground water sources in the UK tends to be fairly constant for most of the year, at between 8 and 12°c. This makes water a more efficient heat source than the outside air, and the heat transfer rate with water is higher than that of air or the ground. In addition, unlike ground-source heat pumps, water-source heat pumps do not require trenches for coils to be laid in, although open loop systems often require filtration.
Closed-loop systems pipe a mixture of water and anti-freeze to a water source such as a lake where it flows through coils or heat exchange panels in the water to exchange heat with it. The heated mixture is then piped to the heat pump and heat exchanged with the refrigerant.
In open-loop systems, water from the source is extracted and piped direct to the heat pump. Heat is then exchanged with the refrigerant and the water then returned to the source. As this involves extraction from and discharge to a water source, it is likely to require an extraction licence and a discharge license from the Environment Agency.
Closed-loop systems can be less efficient than open-loop systems, because of the losses caused by transferring heat between the water source and the fluid in the closed loop. However, they are less restrictive in terms of the danger of freezing, the water quality that can be used, the need for filtration or other forms of water treatment, the possibility of needing to use a corrosion resistant system and the need for licenses. Open-loop systems can also require more pumping.
Water source heat pumps are generally quiet, unobtrusive and have low maintenance requirements. However, care must be taken to ensure that the water supply is consistent and sufficient throughout the year.
Water-source heat pumps are eligible for payments under the government’s Renewable Heat Incentive (RHI) scheme. Domestic schemes may also be eligible for financing through the green deal, however, there has been very poor uptake of the Green Deal, and it is generally considered that better financial deals are available elsewhere.
- Absorption heat pump.
- Air source heat pumps.
- BSRIA domestic hot water heat pumps testing.
- BSRIA global heat pump market 2019.
- Coefficient of Performance CoP.
- Exhaust air heat pump.
- Geothermal pile foundations.
- Green Deal.
- Ground energy options.
- Ground source heat pumps
- Heat pump.
- Hybrid heat pump electric panel heating.
- Mechanical ventilation with heat recovery.
- Renewable energy sources: how they work and what they deliver: Part 3: Electrically driven heat pumps DG 532 3.
- Renewable Heat Incentive.
- Room-based heat pumps.
- Solar-assisted heat pump.
- Solar thermal heating.
- Thermal labyrinths.
- Water source heat map.
 External references
Featured articles and news
Temperature in buildings, explained on DB
Main barrier to entering the profession, new study reveals.
On Levelling-Up and Regeneration Bill.
Over 70 managers and organisations shortlisted for the 14 awards.
From biometric to electrical current, chemical and more.
Changes are due to come into force on 1st October 2022.
Heed advice and insight of this report IPA tells the government.
From the Commonwealth Association of Architects.
For the Levelling Up, Housing & Communities Committee.
BSRIA's Technical Director reflects on recent weather patterns.
A national valuation to fund old-age pensions.
The world’s largest Commonwealth memorial to the missing.
Long after the end of the defects liability period.
Occupant satisfaction and wellbeing in buildings.
From the simple to the complex.
And the UK Government guidelines.
Commitment agreed to by major built environment bodies.
Electrical skills, low carbon, high-tech and the building services revolution.
Ultra-deep drilling with millimeter-wave beam technology.
Looking at the built environment from space.
BSI standards 8671, 8672 and 8673.
Bringing life to burial grounds.
From failed modernism to twenty-minute neighbourhoods.
The gates process and change control.