- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 18 Aug 2017
Combined heat and power CHP
Combined heat and power (CHP), sometimes referred to as cogeneration, is a process in which the heat that is created as a by-product of power generation is captured and used rather than simply being wasted.
According to the Combined Heat and Power Association, “In today’s coal and gas fired power stations, up to two thirds of the overall energy consumed is lost in this way, often seen as a cloud of steam rising from cooling towers.”
Whilst there are a range of different forms of CHP, typically, a gas-powered turbine or reciprocating engine is used to produce electricity, and the heat recovered is used for local water or space heating, or to support an industrial process. Increasingly absorption cooling can use the heat recovered to produce cooling. Sometimes this process is referred to as trigeneration or combined cooling, heat and power (CCHP).
Very broadly, CHP is appropriate in circumstances where there is a continuous local demand for heat and power, such as district heating schemes, hotels and leisure centres, industrial applications that require heat for manufacturing processes and so on. If excess electricity is generated, this can be exported back to the national grid.
- An efficiency of over 80%, compared to 38% for a coal-fired power station.
- Up to 30% savings on energy bills.
- Up to 30% reduction in carbon emissions.
- Reduced transmission and distribution losses.
- Increased fuel supply security.
CHP can be a very significant investment and requires careful consideration. However, where they are certified as Good Quality (GQ)CHP, they are exempt from the Climate Change Levy for fuel inputs and electricity outputs. They may also qualify as Enhanced Capital Allowances (ECA) and be eligible for business rates exemption.
CHP plant can be manufactured as packaged units or can be custom designed and built. Increasingly, micro CHP units can be used to supply small-scale and domestic needs. In effect, these replace conventional boilers. Heat is the primary output of micro CHP, with the ratio of heat to electricity for domestic appliances typically around 6:1, generating up to 1kW of electricity. As with larger CHP plant, if excess electricity is generated, this can be exported back to the national grid. This may be eligible for Feed-in Tariffs in England and Wales and is considered an ‘eligible measure’ suitable for funding under the Green Deal.
 Find out more
 Related articles on Designing Buildings Wiki.
- BSRIA guide to heat interface units.
- Capital allowances.
- Carbon capture and storage.
- Coefficient of Performance CoP.
- Community energy network.
- District energy.
- Fuel cell.
- Future of electricity in domestic buildings.
- Green Deal.
- Heat Networks Investment Project HNIP.
- Liquefied petroleum gas (LPG).
- Low Carbon Energy Centre, London.
- Low carbon heating and cooling.
- On-site generation of heat and power.
 External references
Featured articles and news
The London Build Expo is hosting a Diversity in Construction panel and networking session on October 24.
Analysis can help develop a specification, but must not lead to inappropriate specifications being accepted.
Dos and don'ts for creating a smart home.
New ICE publication recommends pay-as-you-go tax to fund roads and other financing options.
BSRIA launches a White Paper on wearable technology and wellbeing in buildings.
Have the pressures of the market shredded the core values of professionalism?
Lead times are a measure of the amount of time that elapses between initiating and completing a construction process.
Government releases first tranche of funding for removal of unsafe high-rise cladding.
How to ensure UK transport infrastructure copes with severe winter weather.