- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 21 Oct 2020
It can be necessary to provide cooling to buildings during warm weather, or where there are significant thermal gains (such as solar gain, people and equipment). This cooling is sometimes referred to as comfort cooling. Cooling may also be necessary for refrigeration or for some industrial processes.
Evaporative cooling is one of the methods that can be used to provide cooling. When water evaporates, it absorbs significant amounts of heat energy (latent heat, expressed in J/kg). The water itself does not change temperature, as the energy is consumed by the physical process of changing its state from liquid to gas. This produces a cooling effect in its surroundings. So when water evaporates from the surface of a building, or when sweat evaporates from the skin, this has a cooling effect. Conversely, when water condenses it releases heat.
Cooling towers reject heat through the evaporation of water in a moving air stream within the cooling tower. The temperature and humidity of the air stream increases through contact with the warm water, and this air is then discharged. The cooled water is collected at the bottom of the tower. This process can achieve lower temperatures than air-cooled heat rejection systems.
Cooling towers, can be small-scale roof-top installations, medium-sized packaged units, or very large hyperboloid structures sometimes associated with industrial processes or power stations with their characteristic plume of water vapour in the exhaust air.
Cooling towers can be open or closed circuit. Closed circuit cooling towers (or fluid coolers) feed the ‘warm’ water over a 'fill' through which the air is flowing. The cool water is collected, and the humid air discharged remotely to prevent recirculation. This closed process relies entirely on the rejection of heat through the air. The flow of air through the fill can be horizontal (crossflow) or vertical (counterflow).
In open-circuit cooling towers (or wet cooling towers), the hot humid air is discharged direct to the atmosphere. This can be more straight forward, however, there is a risk of contamination as the cooling tower is open, and the proportion of water that evaporates must be replaced resulting in the progressive concentration of the water. The build up of minerals and other solids in the water must then be regulated.
The water flow can be gravity driven or can be a pressurised spray.
In HVAC systems, the cooling tower is used to reject heat from chiller units which supply chilled water for comfort cooling systems. These will typically cool air in air handling units that is then ducted to the internal spaces of the building. Water-cooled chillers can be more efficient than air-cooled chillers, but more infrastructure (and so space) is required.
NB: Wet cooling towers have the potential for legionella growth. The Health and Safety Executive (HSE) require that appropriate measures are taken to prevent or control the risk of legionella. These must be at least as effective as the measures described in Legionnaires’ disease: The control of Legionella bacteria in water systems.
 Related articles on Designing Buildings Wiki
- Absorption refrigeration.
- Air handling unit.
- Cooling tower design and construction.
- Evaporative cooling.
- Health and Safety Executive.
- HSG 274 Legionnaires' disease, Technical guidance.
- Legionnaires' disease.
 External references.
Featured articles and news
A look at the Government's strategic approach.
Steps to help reduce the spread of infection inside buildings.
This social media-centred hobby can be both dangerous and illegal.
Millwork wall treatment with a long and illustrious history.
HSE introduces cumulative exposure calculator.
The Edwardians and their houses.
Cut off from civilian life for over 900 years.
Gaining green support from the carbon giants.
Medieval passageways with spiritual, transport and economic purposes.
Organisation receives accreditation from Investors in People.
Click the button to subscribe.
Communicating the right information at the right time.
Materials can take on different properties to control heat and glare.
Challenges in the construction sector and beyond.