- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 17 Oct 2014
Variable air volume VAV
- Helping to moderate internal temperatures.
- Replenishing oxygen.
- Reducing the accumulation of moisture, odours, bacteria, dust, carbon dioxide, smoke and other contaminants that can build up during occupied periods.
- Creating air movement, which improves the comfort of occupants.
Very broadly, ventilation in buildings can be classified as ‘natural’ or ‘mechanical’. Mechanical ventilation systems can also include heating, cooling, humidity control and air filtration. These functions are often described collectively as HVAC (Heating Ventilation and Air Conditioning).
- Variable air volume (VAV), in which the temperature of the supply air remains constant, but the volume varies (also known as variable volume, constant temperature VV-CT).
- Constant air volume (CAV) in which the volume of air supply remains constant, but the temperature varies (also known as constant volume, variable temperature CV-VT).
- Variable volume, variable temperature (VV-VT sometimes referred to as variable volume and temperature - VVT).
In more complex systems, where spaces have different heating or cooling demands, there may be additional local control of the amount of air that enters each space. Typically, cool air is supplied by an air handling unit, and thermostatically controlled dampers regulate the amount of air that enters each space. The damper must always remain partially open to allow some ‘fresh’ air into the space.
The fans in the air handling unit are adjusted (variable frequency drive VFD) to control the air pressure in the ductwork. Refrigerant flow is also adjusted to ensure that the air temperature remains constant. VAV terminal units may include fans that re-circulate a proportion of internal air along with the ‘fresh’ supply air to reduce the cooling load.
Where variations between spaces mean that some local heating is required in to maintain constant temperatures throughout a building, VAV terminal units may re-heat the supply air. Despite the apparent waste of re-heating previously cooled air, this can be more economic that providing a warm air supply from the air handling unit when there is only limited heating demand. Heat may be provided in VAV terminal units by electrical elements or by hot water coils.
In dual duct systems, both cool air and warm air ducts are provided.
 Related articles on Designing Buildings Wiki
Featured articles and news
How to deliver a five-fold multiplier effect from investment in water infrastructure.
RSHP's Leadenhall building is named a 2018 RIBA National Award winner.
Gary Neville's controversial Manchester tower gets the green light to go ahead.
Health and safety is everyone’s responsibility.
BSRIA guide to energy storage in buildings - a technology overview.
The UK’s largest Passivhaus accredited affordable housing scheme.
ICE set out 5 recommendations for the Government Construction Strategy 2018 update.
Balfour Beatty fined £500,000 for exposing workers to hand-arm vibration.
James Brokenshire launches a consultation on banning combustible cladding.
A year after Grenfell, we have a collection of 30 articles telling you everything you need to know.
Detailed guidance about construction waste management.