Variable air volume VAV
Ventilation is necessary in buildings to remove ‘stale’ air and replace it with ‘fresh’ air:
- Helping to moderate internal temperatures.
- Replenishing oxygen.
- Reducing the accumulation of moisture, odours, bacteria, dust, carbon dioxide, smoke and other contaminants that can build up during occupied periods.
- Creating air movement, which improves the comfort of occupants.
Very broadly, ventilation in buildings can be classified as ‘natural’ or ‘mechanical’. Mechanical ventilation systems can also include heating, cooling, humidity control and air filtration. These functions are often described collectively as HVAC (Heating Ventilation and Air Conditioning).
- Variable air volume (VAV), in which the temperature of the supply air remains constant, but the volume varies (also known as variable volume, constant temperature VV-CT).
- Constant air volume (CAV) in which the volume of air supply remains constant, but the temperature varies (also known as constant volume, variable temperature CV-VT).
- Variable volume, variable temperature (VV-VT sometimes referred to as variable volume and temperature - VVT).
In more complex systems, where spaces have different heating or cooling demands, there may be additional local control of the amount of air that enters each space. Typically, cool air is supplied by an air handling unit, and thermostatically controlled dampers regulate the amount of air that enters each space. The damper must always remain partially open to allow some ‘fresh’ air into the space.
The fans in the air handling unit are adjusted (variable frequency drive VFD) to control the air pressure in the ductwork. Refrigerant flow is also adjusted to ensure that the air temperature remains constant. VAV terminal units may include fans that re-circulate a proportion of internal air along with the ‘fresh’ supply air to reduce the cooling load.
Where variations between spaces mean that some local heating is required in to maintain constant temperatures throughout a building, VAV terminal units may re-heat the supply air. Despite the apparent waste of re-heating previously cooled air, this can be more economic that providing a warm air supply from the air handling unit when there is only limited heating demand. Heat may be provided in VAV terminal units by electrical elements or by hot water coils.
In dual duct systems, both cool air and warm air ducts are provided.
 Related articles on Designing Buildings Wiki
Featured articles and news
Budget documents state modern methods of construction will be favoured for public infrastructure schemes from 2019.
A walk-through exhibition of an emergency humanitarian shelter is officially opened at BRE's Innovation Park.
How to work safely on a construction site during winter.
Housing is the big winner in Chancellor Philip Hammond's Autumn Budget.
The winner of our BSRIA competition, Tomorrow's challenges in today's buildings, is.... Bob Hendrikx. A big thank you to everyone that took part.
Committee of MPs accuses government of dealing billpayers a 'bad hand' over the guaranteed power price.
In 1992, the Joint Fire Code was first published. What influence does it still have on construction sites today?
"Companies will have to adapt or go out of business" - how are virtual reality and big data disrupting digital construction?
International Well Building Institute and BRE collaborate on multiple levels to advance human health through better buildings.
"The industry has tried moving away from prescriptivism to focus on performance, but maybe that’s no longer working".
Energy from waste and its key role in a low carbon economy.
Sir Ranulph Fiennes was guest speaker at the BSRIA Briefing - Tomorrow’s challenges in today’s buildings.
Read our introductory article to the Common Arrangement of Work Sections. What are they, what are the categories?