- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 17 Oct 2014
Variable air volume VAV
Ventilation is necessary in buildings to remove ‘stale’ air and replace it with ‘fresh’ air:
- Helping to moderate internal temperatures.
- Replenishing oxygen.
- Reducing the accumulation of moisture, odours, bacteria, dust, carbon dioxide, smoke and other contaminants that can build up during occupied periods.
- Creating air movement, which improves the comfort of occupants.
Very broadly, ventilation in buildings can be classified as ‘natural’ or ‘mechanical’. Mechanical ventilation systems can also include heating, cooling, humidity control and air filtration. These functions are often described collectively as HVAC (Heating Ventilation and Air Conditioning).
- Variable air volume (VAV), in which the temperature of the supply air remains constant, but the volume varies (also known as variable volume, constant temperature VV-CT).
- Constant air volume (CAV) in which the volume of air supply remains constant, but the temperature varies (also known as constant volume, variable temperature CV-VT).
- Variable volume, variable temperature (VV-VT sometimes referred to as variable volume and temperature - VVT).
In more complex systems, where spaces have different heating or cooling demands, there may be additional local control of the amount of air that enters each space. Typically, cool air is supplied by an air handling unit, and thermostatically controlled dampers regulate the amount of air that enters each space. The damper must always remain partially open to allow some ‘fresh’ air into the space.
The fans in the air handling unit are adjusted (variable frequency drive VFD) to control the air pressure in the ductwork. Refrigerant flow is also adjusted to ensure that the air temperature remains constant. VAV terminal units may include fans that re-circulate a proportion of internal air along with the ‘fresh’ supply air to reduce the cooling load.
Where variations between spaces mean that some local heating is required in to maintain constant temperatures throughout a building, VAV terminal units may re-heat the supply air. Despite the apparent waste of re-heating previously cooled air, this can be more economic that providing a warm air supply from the air handling unit when there is only limited heating demand. Heat may be provided in VAV terminal units by electrical elements or by hot water coils.
In dual duct systems, both cool air and warm air ducts are provided.
 Related articles on Designing Buildings Wiki
Featured articles and news
EIRs define what is needed from the employer's internal team and suppliers for project development.
The full keynote speech by Sir James Bevan, Environment Agency CEO, on the future of flood protection.
After 6 years, the Metropolitan Police admit they supplied information to the construction workers blacklist.
It's nearly two years since level 2 BIM was made a minimum requirement on certain public projects. But what actually is it?
Renowned water expert Prof. Martin van Veelen challenges political leaders to do more on safe and clean water supplies.
Inquiry criticises PwC for "milking the Carillion cow dry".
A recent roundtable discussed the future of transport in the UK – including the role of connected and autonomous vehicles.
Architects report cancelled projects and uncertainty concerns in a new RIBA survey on Brexit.
Quality helps eliminate defects, but it can also drive improvement and increase profit.
PII provides insurance cover against negligence claims and is widely used where services are being provided.
Rogers Stirk Harbour + Partners release first images of their planned new addition to the Toronto skyline.