Variable air volume VAV
Ventilation is necessary in buildings to remove ‘stale’ air and replace it with ‘fresh’ air:
- Helping to moderate internal temperatures.
- Replenishing oxygen.
- Reducing the accumulation of moisture, odours, bacteria, dust, carbon dioxide, smoke and other contaminants that can build up during occupied periods.
- Creating air movement, which improves the comfort of occupants.
Very broadly, ventilation in buildings can be classified as ‘natural’ or ‘mechanical’. Mechanical ventilation systems can also include heating, cooling, humidity control and air filtration. These functions are often described collectively as HVAC (Heating Ventilation and Air Conditioning).
- Variable air volume (VAV), in which the temperature of the supply air remains constant, but the volume varies (also known as variable volume, constant temperature VV-CT).
- Constant air volume (CAV) in which the volume of air supply remains constant, but the temperature varies (also known as constant volume, variable temperature CV-VT).
- Variable volume, variable temperature (VV-VT sometimes referred to as variable volume and temperature - VVT).
In more complex systems, where spaces have different heating or cooling demands, there may be additional local control of the amount of air that enters each space. Typically, cool air is supplied by an air handling unit, and thermostatically controlled dampers regulate the amount of air that enters each space. The damper must always remain partially open to allow some ‘fresh’ air into the space.
The fans in the air handling unit are adjusted (variable frequency drive VFD) to control the air pressure in the ductwork. Refrigerant flow is also adjusted to ensure that the air temperature remains constant. VAV terminal units may include fans that re-circulate a proportion of internal air along with the ‘fresh’ supply air to reduce the cooling load.
Where variations between spaces mean that some local heating is required in to maintain constant temperatures throughout a building, VAV terminal units may re-heat the supply air. Despite the apparent waste of re-heating previously cooled air, this can be more economic that providing a warm air supply from the air handling unit when there is only limited heating demand. Heat may be provided in VAV terminal units by electrical elements or by hot water coils.
In dual duct systems, both cool air and warm air ducts are provided.
 Related articles on Designing Buildings Wiki
Featured articles and news
This unique Brutalist-era car park just off Oxford Street is soon to be demolished.
How to utilise technology in construction projects and what benefits will it bring?
Have a look at Thomas Heatherwick's new building, one he calls 'the tubiest in the world'.
Artificial intelligence will have a significant impact on the built environment, according to a new survey by ICE.
Construction is often seen as too traditional, lacking innovation and collaboration. But are these perceptions fair?
Designing Buildings Wiki attended CIAT's Architectural Technology Awards 2017. Find out the winners here.
BSI make revisions to BS 5839-1 for fire detection and fire alarm systems in commercial buildings.
An introductory article to the change control procedure for building design and construction.
Only weeks after his Garden Bridge is scrapped, Thomas Heatherwick's plan for Pier 55 in New York is abandoned.
British Land are given planning permission for their £300m extension of Meadowhall shopping centre.
30 years ago, Walter Segal's radical self-builders completed Walters Way. We talked to the author of a new book about the project, and its influence on self-build today.
This article has a look at the top 10 most expensive construction projects in the world.