- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 16 Oct 2020
Variable air volume VAV
- Helping to moderate internal temperatures.
- Replenishing oxygen.
- Reducing the accumulation of moisture, odours, bacteria, dust, carbon dioxide, smoke and other contaminants that can build up during occupied periods.
- Creating air movement, which improves the comfort of occupants.
Very broadly, ventilation in buildings can be classified as ‘natural’ or ‘mechanical’. Mechanical ventilation systems can also include heating, cooling, humidity control and air filtration. These functions are often described collectively as HVAC (Heating Ventilation and Air Conditioning).
- Variable air volume (VAV), in which the temperature of the supply air remains constant, but the volume varies (also known as variable volume, constant temperature VV-CT).
- Constant air volume (CAV) in which the volume of air supply remains constant, but the temperature varies (also known as constant volume, variable temperature CV-VT).
- Variable volume, variable temperature (VV-VT sometimes referred to as variable volume and temperature - VVT).
In more complex systems, where spaces have different heating or cooling demands, there may be additional local control of the amount of air that enters each space. Typically, cool air is supplied by an air handling unit, and thermostatically controlled dampers regulate the amount of air that enters each space. The damper must always remain partially open to allow some ‘fresh’ air into the space.
The fans in the air handling unit are adjusted (variable frequency drive VFD) to control the air pressure in the ductwork. Refrigerant flow is also adjusted to ensure that the air temperature remains constant. VAV terminal units may include fans that re-circulate a proportion of internal air along with the ‘fresh’ supply air to reduce the cooling load.
Where variations between spaces mean that some local heating is required in to maintain constant temperatures throughout a building, VAV terminal units may re-heat the supply air. Despite the apparent waste of re-heating previously cooled air, this can be more economic that providing a warm air supply from the air handling unit when there is only limited heating demand. Heat may be provided in VAV terminal units by electrical elements or by hot water coils.
 Find out more
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Building services.
- Chiller unit.
- Computational fluid dynamics.
- Constant air volume.
- Cross ventilation.
- Dew point.
- Interstitial condensation.
- Mechanical ventilation.
- Natural ventilation.
- Passive building design.
- Solar chimney.
- Stack effect.
- Thermal comfort.
Featured articles and news
An overview of the current state of the market.
Organisation offers best practices for construction and modification.
Heritage on the edge?
Prioritising tax considerations.
The four D creative process: discover, define, develop and deliver.
National Cyber Security Centre initiative is announced.
Reviewing trends and projections.
Legislation will establish initiatives to move towards net zero.
How to document contractor employment status.
Tech tools to help manage people and space post-pandemic.
A style that ranges from mock Tudor to arts and crafts to the 'Wrenaissance'.
Free guide from Secured by Design.
BREEAM strategy for sustainability and the circular economy.
Free tool to improve the construction programming process.