Variable air volume VAV
Ventilation is necessary in buildings to remove ‘stale’ air and replace it with ‘fresh’ air:
- Helping to moderate internal temperatures.
- Replenishing oxygen.
- Reducing the accumulation of moisture, odours, bacteria, dust, carbon dioxide, smoke and other contaminants that can build up during occupied periods.
- Creating air movement, which improves the comfort of occupants.
Very broadly, ventilation in buildings can be classified as ‘natural’ or ‘mechanical’. Mechanical ventilation systems can also include heating, cooling, humidity control and air filtration. These functions are often described collectively as HVAC (Heating Ventilation and Air Conditioning).
- Variable air volume (VAV), in which the temperature of the supply air remains constant, but the volume varies (also known as variable volume, constant temperature VV-CT).
- Constant air volume (CAV) in which the volume of air supply remains constant, but the temperature varies (also known as constant volume, variable temperature CV-VT).
- Variable volume, variable temperature (VV-VT sometimes referred to as variable volume and temperature - VVT).
VAV systems tend to provide closer control of air temperature than CAV systems and require lower fan speeds, as a result of which they can use less energy and generate less noise.
In more complex systems, where spaces have different heating or cooling demands, there may be additional local control of the amount of air that enters each space. Typically, cool air is supplied by an air handling unit, and thermostatically controlled dampers regulate the amount of air that enters each space. The damper must always remain partially open to allow some ‘fresh’ air into the space.
The fans in the air handling unit are adjusted (variable frequency drive VFD) to control the air pressure in the ductwork. Refrigerant flow is also adjusted to ensure that the air temperature remains constant. VAV terminal units may include fans that re-circulate a proportion of internal air along with the ‘fresh’ supply air to reduce the cooling load.
Where variations between spaces mean that some local heating is required in to maintain constant temperatures throughout a building, VAV terminal units may re-heat the supply air. Despite the apparent waste of re-heating previously cooled air, this can be more economic that providing a warm air supply from the air handling unit when there is only limited heating demand. Heat may be provided in VAV terminal units by electrical elements or by hot water coils.
In dual duct systems, both cool air and warm air ducts are provided.
 Related articles on Designing Buildings Wiki
Featured articles and news
The Tempe Municipal Building is a steel-and-glass inverted pyramid.
What is systems thinking and how could it help infrastructure professionals deliver better results?
Read about the newly-completed fourth tallest building in the world.
Read Designing Buildings Wiki's review of Imagine Moscow - an exhibition looking at the utopian projects of the early-USSR.
What are the various different types of alternative dispute resolution for construction?
3-point plan released for how government can safeguard infrastructure post-Brexit.
Thomas Heatherwick's Pier 55 is halted due to judge ruling on wildlife protection.
Have a look at our article explaining contract claims in construction.
Studio Libeskind reveal designs for a new skyscraper with a living facade in Toulouse.
A mega-dome, a cenotaph for Newton, a bubble over New York - some of the most famous projects that were never realised.
One of the oldest and finest examples of Byzantine and Islamic architecture, the Dome of the Rock.