Variable air volume VAV
Ventilation is necessary in buildings to remove ‘stale’ air and replace it with ‘fresh’ air:
- Helping to moderate internal temperatures.
- Replenishing oxygen.
- Reducing the accumulation of moisture, odours, bacteria, dust, carbon dioxide, smoke and other contaminants that can build up during occupied periods.
- Creating air movement, which improves the comfort of occupants.
Very broadly, ventilation in buildings can be classified as ‘natural’ or ‘mechanical’. Mechanical ventilation systems can also include heating, cooling, humidity control and air filtration. These functions are often described collectively as HVAC (Heating Ventilation and Air Conditioning).
- Variable air volume (VAV), in which the temperature of the supply air remains constant, but the volume varies (also known as variable volume, constant temperature VV-CT).
- Constant air volume (CAV) in which the volume of air supply remains constant, but the temperature varies (also known as constant volume, variable temperature CV-VT).
- Variable volume, variable temperature (VV-VT sometimes referred to as variable volume and temperature - VVT).
VAV systems tend to provide closer control of air temperature than CAV systems and require lower fan speeds, as a result of which they can use less energy and generate less noise.
In more complex systems, where spaces have different heating or cooling demands, there may be additional local control of the amount of air that enters each space. Typically, cool air is supplied by an air handling unit, and thermostatically controlled dampers regulate the amount of air that enters each space. The damper must always remain partially open to allow some ‘fresh’ air into the space.
The fans in the air handling unit are adjusted (variable frequency drive VFD) to control the air pressure in the ductwork. Refrigerant flow is also adjusted to ensure that the air temperature remains constant. VAV terminal units may include fans that re-circulate a proportion of internal air along with the ‘fresh’ supply air to reduce the cooling load.
Where variations between spaces mean that some local heating is required in to maintain constant temperatures throughout a building, VAV terminal units may re-heat the supply air. Despite the apparent waste of re-heating previously cooled air, this can be more economic that providing a warm air supply from the air handling unit when there is only limited heating demand. Heat may be provided in VAV terminal units by electrical elements or by hot water coils.
In dual duct systems, both cool air and warm air ducts are provided.
 Related articles on Designing Buildings Wiki
Featured articles and news
Here is our list of the top 25 buildings in London. Do you agree with our selection?
A blueprint for the construction industry from Canada's west coast.
China's elaborate idea for a mass-transport system has been abandoned.
Read this article about the theories that characterise life in the hyperreal post-modern city.
Polyisocyanurate (PIR) insulation and how it was tested.
"We can’t sustain low density suburbs, density isn't a choice, it's a necessity." - Read our interview with the award-winning social housing architect Peter Barber.
Conservation area designation can be crucial, but treatment of individual parks varies considerably.
ICE publish new NEC4 Design, Build and Operate contract.
Report states $2 trillion is needed over the next 10 years to fix American roads.
What is the client's strategic brief for construction projects?
Read the story behind the world's most iconic festival stage, Glastonbury's Pyramid Stage.
First ever BREEAM Communities innovation credit is claimed by Temple Farm Development.
Read the story of Ronan Point, another disastrous event which had profound consequences for the construction industry.
CIOB to help conservation specialists gain recognition for their expertise with launch of new Certification Scheme.
What is ACM cladding, what is it used for, and is it banned?