- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 20 Jun 2022
This effect can be used to naturally ventilate buildings. Cooler outside air is drawn into buildings at a lower level, it is warmed by sources of heat within the building (such as people, equipment, heating and solar gain), and then rises through the building to vent out at a higher level.
A positive pressure area is created at the top of a building and negative pressure area at the bottom. This process can take place without mechanical assistance, simply by introducing openings at the bottom and the top of buildings. It is known as the stack effect or stack ventilation.
Stack ventilation can be particularly effective as a means of naturally ventilating tall buildings that include vertical spaces which rise throughout their height, for example buildings with central atriums. This can be useful in deep buildings, where cross ventilation may not be sufficient to penetrate to spaces in the heart of the building.
- The effective area of openings.
- The height of the stack.
- The temperature difference between the bottom and the top of the stack.
- Pressure differences outside the building.
The stack effect is a relatively weak force in many buildings (although it can be strong enough to fly a kite in large buildings) and so it may be necessary to have large openings with minimal resistance.
The pressure will vary through the height of the building, with the outside pressure being higher than the inside pressure at the bottom of the building, but the inside pressure being higher at the top. As a consequence, there will be a neutral plane, which is the level at which the internal and external pressure are equal. Above the neutral plane the internal air pressure will be positive and so air will tend to exhaust to the outside. Below the neutral plane, the internal air pressure will be negative and air will tend to be drawn into the building. This requires careful design to ensure that the neutral plane is above the spaces that need to be ventilated from the outside.
Stack ventilation is not appropriate for all building types, and as the stack effect requires that the internal temperature is higher than the outside temperature, it may not always provide a sufficient cooling effect by itself and additional mechanical cooling may be necessary. In particular, rooms adjoining the warmer part of the stack may experience poor ventilation and unwanted heat gains. In addition, there may be conflicts between the requirement for large unrestricted openings between the outside and the heart of the building, and requirements for security, privacy, noise control, fire compartmentation, and so on.
Designing natural ventilation can become extremely complex because of the interaction between cross ventilation and the stack effect as well as complex building geometries and complex distribution of openings. This can require computer analysis.
NB: Approved document F, Ventilation, defines 'passive stack ventilation' (PSV) as, ‘…a ventilation system using ducts from terminals in the ceiling of rooms to terminals on the roof that extract air to the outside by a combination of the natural stack effect and the pressure effects of wind passing over the roof of the building.’
NB: Stack ventilation can also refer to secondary ventilation stacks used to overcome air pressure changes in pipework in high-rise buildings. For more information see: Secondary ventilation stacks in tall buildings.
- Computational fluid dynamics.
- Cross ventilation.
- Dynamic thermal modelling of closed loop geothermal heat pump systems.
- Energy targets.
- Face velocity.
- Natural ventilation.
- Passive building design.
- Secondary ventilation stacks in tall buildings.
- Single-sided ventilation.
- Solar chimney.
- Thermal comfort.
- Types of ventilation.
- Natural ventilation.
- Warm roof.
Featured articles and news
Advancing sustainable and regenerative project management.
Promised to be pragmatic and practical guidance.
Whilst replacement maybe preferred, its not always possible.
Dealing with draughts and reducing heat loss.
Managing Partner at Onyx and third gen project manager.
Expectation types, management and performance gaps.
Appointments, re-appointments and six changes a year.
New ways to manage the housing crisis.
Consortium seeks signatories for open letter by February 29.
Meaning, understanding and implementation.
From climate to cost to cold bridges and design flexibility.
In a changing world at the APM PM SIG conference.
The glass product that opened up new possibilities.
Campaigning for buildings of all periods.
Get to know the new requirements and the new terms.
The ultimate companion for building services excellence.