- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 16 Sep 2020
Passive design maximises the use of ‘natural’ sources of heating, cooling and ventilation to create comfortable conditions inside buildings. It harness environmental conditions such as solar radiation, cool night air and air pressure differences to drive the internal environment. Passive measures do not involve mechanical or electrical systems.
This is as opposed to ‘active’ design which makes use of active building services systems to create comfortable conditions, such as boilers and chillers, mechanical ventilation, electric lighting and so on. Buildings will generally include both active and passive measures.
Solar chimneys are generally tall, wide structures constructed, facing the sun, with a dark coloured, matt surface designed to absorb solar radiation. As the chimney becomes hot, so it heats the air inside it. The hot air rises up the chimney and is vented out of the top, and in so doing it draws more air in at the bottom of the chimney. This can be used to drive passive ventilation in buildings where cross ventilation or stack ventilation may not be sufficient, and where designers wish to avoid using energy-consuming mechanical ventilation.
Solar chimneys are particularly effective in climates that are humid and hot. They are most efficient when they are tall and wide, but not very deep. This maximises the surface area that can absorb solar radiation and maximises the surface area in contact with the air inside the chimney.
Variations in design can incorporate multiple chambers to further increase surface area and may use materials with high solar absorption such as metal to maximise the temperatures achieved within the chimney. Low emissivity coatings, and glazing can also be used to reduce heat losses back to the outside, similar to the design of trombe walls.
It is important that the chimney is insulated from the building itself so that heat gains do not transmit into occupied spaces. In cooler conditions, the chimney can be used to direct absorbed heat back into the building by closing it at the top.
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
Organisation revises actions around dealing with COVID-19.
CIOB, NFCC, RIBA, RICS call for changes ahead of Building Safety Bill.
Developments in the Future Homes Standard.
An American chimney feature with a colourful past.
Homes based on need, not ability to pay.
Historic England adds 216 entries to the 'at risk' register.
Will cycling and walking provisions be preserved?
Assembly point levels range from relative to ultimate.
Signs are pointing to a recovery for the construction industry.
Campaigning to change perceptions about American Brutalism.
Sprinkler head configurations can prioritise people or property.
Report from The Carbon Project reveals shortcomings and recommendations.
Advice on how to join the electrotechnical profession.