- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 31 Jul 2019
An electrical system, within the context of a building, is a network of conductors and equipment designed to carry, distribute and convert electrical power safely from the point of delivery or generation to the various loads around the building that consume the electrical energy.
The vast majority of electrical systems used in buildings in the UK operate at 230V single phase alternating current (AC) or 400V 3 phase, at a frequency of 50Hz. These networks are often referred to as low voltage (LV) networks. This system is also referred to as mains electricity.
Larger installations may operate at higher voltages, often with 11kV supplies or feeders at the origin of the installation. These networks are referred to as high voltage (HV) networks.
The conductors that form part of the electrical system are the means by which electricity is transferred from one place to another. Typically, conductors are made from copper, which offers a good balance between electrical conductivity and cost. Aluminium may also be used in some instances. Conductors are typically insulated with PVC or other synthetic insulating materials.
Most conductors are used in the form of electrical cables. These can be run either separately or within containment systems between two points of an electrical system.
Other conductors commonly used in electrical systems in buildings are busbars. These are usually copper or aluminium conductors and run within an insulating and safety enclosure, typically a trunking. These may be used where larger conductors are required, as the busbar trunking is often physically smaller than cables of equivalent current carrying capacity. Such busbar trunking is usually made up of rigid lengths, and may have several tapping points, where supplies may be tapped or branched off.
As well as conductors, an electrical system will also comprise equipment that provides switching and protection capabilities, known as switchgear. Switchgear enables with manual or automated control of current flow.
Manual control relies on human intervention to work smoothly and is typically employed for isolation switching and functional switching.
Automatic switching may be based on protection characteristics for devices that detect excess current flow and act to prevent damage to cabling that may lead to fire and/or electric shock. This is usually achieved through the use of circuit breakers and/or fuses.
Automatic switching may also be handled by control systems, where electrical signalling from other systems is used to control devices known as relays or contactors, which in turn control higher power circuits.
Examples of these include common items such as light fittings (luminaires), motors, electric heating units, as well as power conversion equipment which converts mains electricity to lower voltages to run appliances and electronic equipment. Often such power conversion is done within the appliance or load itself.
 Related articles on Designing Buildings Wiki
Featured articles and news
Partnership avoids the need for listed building consent.
Connecting building design from inception to completion to operations.
Gregor Harvie predicts interoperability will be construction’s Uber moment.
Expert commentary and insight.
Guidance offered for stained glass window maintenance.
Define need before determining viability.
Framework examines social value of projects.
RfX or Request for [fill in the blank].
Organisation establishes Equality, Diversity, Inclusion taskforce.
Government announces plans for new building projects.
Outsourcing method to procure and manage supplies.
Joint support of Local Authority Historic Environment and Conservation Services.
The Chesapeake Bay Bridge-Tunnel is an outstanding achievement.
Buildings of the interwar years. Book review.
Ireland’s climate change sectoral adaptation plan.