- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 27 Jul 2021
According to Approved Document P - Electrical safety – Dwellings: Low voltage is, ‘a voltage exceeding extra-low voltage, but not exceeding 1,000 V ac or 1,500 V dc between conductors, or 600 V ac or 900 V dc between conductors and earth.’ Where extra-low voltage is, ‘A voltage not exceeding 50 V ac or 120 V ripple-free dc, whether between conductors or to earth.’
The Illustrated Guide to Electrical Building Services, Third Edition (BG 31/2017), by David Bleicher & Peter Tse, published by BSRIA in 2014, suggests that: ‘Low voltage is a term used to describe 400 V three-phase and 230 V single-phase supplies. These are nominal voltages - the actual voltage may vary up to 10%. The intake to buildings that have a low voltage supply is usually provided by the electricity supplier in the form of an underground cable that emerges at a suitable point within the building. The cable is connected directly to the electricity supplier’s cut-out. Also known as a service head, this is a fused unit that protects the supplier’s infrastructure.’
 Related articles on Designing Buildings Wiki
Featured articles and news
Global building automation and control systems trends reviewed.
Significant changes to BS 7671:2018+A2:2022 announced.
Students available for administrative roles.
Delisting a World Heritage Site.
Design needs to be more diverse to be widely accessible.
It’s not always a case of the centre leading.
PHribbon toolbar developed for US market.
CIOB consultation seeks feedback on APPG 2020 report.
How to respond to changes made in the October 2021 update.