- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 27 Jul 2021
According to Approved Document P - Electrical safety – Dwellings: Low voltage is, ‘a voltage exceeding extra-low voltage, but not exceeding 1,000 V ac or 1,500 V dc between conductors, or 600 V ac or 900 V dc between conductors and earth.’ Where extra-low voltage is, ‘A voltage not exceeding 50 V ac or 120 V ripple-free dc, whether between conductors or to earth.’
The Illustrated Guide to Electrical Building Services, Third Edition (BG 31/2017), by David Bleicher & Peter Tse, published by BSRIA in 2014, suggests that: ‘Low voltage is a term used to describe 400 V three-phase and 230 V single-phase supplies. These are nominal voltages - the actual voltage may vary up to 10%. The intake to buildings that have a low voltage supply is usually provided by the electricity supplier in the form of an underground cable that emerges at a suitable point within the building. The cable is connected directly to the electricity supplier’s cut-out. Also known as a service head, this is a fused unit that protects the supplier’s infrastructure.’
 Related articles on Designing Buildings Wiki
Featured articles and news
Saint Michael’s Kirkyard - a Presbyterian Valhalla. Book review.
Facing the impact of the COVID and the internet.
Preparing for the return of employees.
Using rainscreen walls to address energy efficiency.
Integrity of fire product marketing - post-Grenfell - addressed.
Data measurement and carbon reduction efforts.
Actuate UK issues stark warning.
Department for Levelling Up, Housing and Communities replaces MHCLG.
Protecting heritage from disasters. Book review.
Three structures forever changed people's lives for the better.
ECA comments on findings of BEIS Green Jobs Task Force.