- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 02 May 2018
Smoke dampers are passive fire protection devices that impede the spread of smoke between different spaces in a building. They are mechanical or intumescent devices, placed within a duct or ventilation opening, which have louvres or shutters that can close automatically preventing the passage of smoke and other products of combustion.
Combined fire and smoke dampers (or fire smoke dampers) prevent the passage of fire as well as smoke and other products of combustion. Typically they do this by closing if a certain temperature is exceeded or if smoke is detected.
Smoke dampers are often operated from a control panel, whereas fire detectors are more frequently operated by mechanical or fusible linkages.
From 1 July 2013, it became a requirement under the Construction Products Regulation for all new fire and smoke dampers used in UK buildings to be CE-marked to indicate product compliance (ref. CIBSE Journal). This recognises the testing standard BS EN 1366 – Fire resistance tests for service installations, which contains test procedures which ensure dampers are installed appropriately.
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
How not to upset the planners.
CEEQUAL International and how it works.
Communities across England are being encouraged to nominate heritage assets.
Access control in buildings.
MASTRO project – lifecycle costing and assessment.
Five things to consider before installing solar panels.
New conservation building for the Louvre completed.
A balance between character and climate.
Bamboo pavilion built at London South Bank Uni.
Bringing in an expert.
Why the lowest price isn't sustainable.