- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 02 May 2018
Smoke dampers are passive fire protection devices that impede the spread of smoke between different spaces in a building. They are mechanical or intumescent devices, placed within a duct or ventilation opening, which have louvres or shutters that can close automatically preventing the passage of smoke and other products of combustion.
Combined fire and smoke dampers (or fire smoke dampers) prevent the passage of fire as well as smoke and other products of combustion. Typically they do this by closing if a certain temperature is exceeded or if smoke is detected.
Smoke dampers are often operated from a control panel, whereas fire detectors are more frequently operated by mechanical or fusible linkages.
From 1 July 2013, it became a requirement under the Construction Products Regulation for all new fire and smoke dampers used in UK buildings to be CE-marked to indicate product compliance (ref. CIBSE Journal). This recognises the testing standard BS EN 1366 – Fire resistance tests for service installations, which contains test procedures which ensure dampers are installed appropriately.
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
New BSRIA guide provides a structured approach for identifying and achieving success criteria.
People, traffic and historic townscapes.
A remote plateau in Bulgaria has been the focus of international preservation efforts.
Dynamo packages data ready for Revit.
How does EVA rate a project's progress?
How can it benefit the built environment?
The benefits of early contractor involvement.
Why it is so important for health and wellbeing.
A highly effective method of managing supply chains.
How it can benefit construction.
Free guide to commissioning for site managers published by NHBC and BSRIA.