- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 30 Jun 2021
Smoke dampers are passive fire protection devices that impede the spread of smoke between different spaces in a building. They are mechanical or intumescent devices, placed within a duct or ventilation opening, which have louvres or shutters that can close automatically preventing the passage of smoke and other products of combustion.
Combined fire and smoke dampers (or fire smoke dampers) prevent the passage of fire as well as smoke and other products of combustion. Typically they do this by closing if a certain temperature is exceeded or if smoke is detected.
From 1 July 2013, it became a requirement under the Construction Products Regulation for all new fire and smoke dampers used in UK buildings to be CE-marked to indicate product compliance (ref. CIBSE Journal). This recognises the testing standard BS EN 1366 – Fire resistance tests for service installations, which contains test procedures which ensure dampers are installed appropriately.
NB A fire and smoke damper is: 'A fire damper which, in addition to the performance of the fire damper, resists the spread of smoke.' Ref Approved document B, Fire Safety, Volume 2, Buildings other than dwellinghouses (2019 edition).
 Related articles on Designing Buildings Wiki
Featured articles and news
Government announces global innovation strategy.
An architectural biography. Book review.
The house where the future king of France lived.
The teacher, architectural technologist and mum offers her insights.
Careful planning needed as supply chain issues continue.
The sensitive conversion of a neglected Cornwall structure.
Plan stresses local involvement in city, town and village development.
Environment Agency publishes BAT guidance.
CLC guidance outlines carbon reduction priorities.
Making the most of a staycation.
Organisation urges G20 to revisit wind energy.
The historian spent much of his life compiling architectural resources.