- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 23 Dec 2017
See also: Fire detection and alarm system.
Fire can be detected by; heat detectors, flame detectors, smoke detectors, carbon monoxide detectors and multi sensor detectors, or an alarm can be triggered at manual call points. Detectors may be hard wired, or battery operated, and may be interconnected so that if one detector is triggered, all interconnected alarms sound.
Detectors can also be fitted with an escape light which comes on when the alarm is triggered. For people with hearing difficulties, smoke detectors are available that can, for example, be fitted to pillows, making them vibrate if triggered, or a strobe light effect. They may also be integral to a personal protection system for vulnerable people that discharges a watermist over a bed or chair that is the seat of a fire.
The number of detectors required will depend on the particular building, but, very broadly, the more that are installed, the higher the level of protection.
It is important however that the right type of fire detector is used for different situations, as false alarms can result in occupants disabling, or losing confidence in fire detection and fire alarm systems. In the period 2011-2012 there were 584,500 alarms reported in Britain. 53.4% of these were not fires and therefore considered “False alarms”.
The most common causes of false alarms are:
- Fumes from cooking.
- Steam from bathrooms, shower rooms and kitchens.
- Tobacco smoke.
- Inappropriate detector settings, such as sensitivity.
- Poor maintenance or failures.
- Inappropriate locations or types of detector.
 Types of detector
See Optical smoke alarms for more information
Ionisation smoke alarms are more sensitive to smoke containing small particles such as rapidly burning flaming fires but are less sensitive to steam and so are recommended for hallways and stairwells adjacent to bathrooms or shower rooms.
 Heat alarms.
Multi-sensor alarms (or multi-criteria alarms) detect more than one fire phenomena, for example optical and heat detection. They may also include other detection capabilities, such as carbon monoxide detection. A multi-sensor alarm provides early warning of fire and can significantly reduce the number of unwanted false alarms in certain circumstances.
 Intelligent detectors
Intelligent detectors are independently addressed and continuously monitored to verify correct operation. They may also have adjustable sensitivity settings and drift compensation to account for environmental conditions. This can help identify when an alarm is genuine, as opposed to resulting from a maintenance issue or incorrect setting, and can significantly reduce the number of false alarms.
 Find out more
 Related articles on Designing Buildings Wiki
- Domestic smoke alarms DG525.
- Fire detection and alarm system.
- Heat alarm.
- Ionisation smoke alarms.
- New requirements for fire detection and alarm network systems IP 12 13.
- Optical smoke alarm
- Smoke detector.
- The causes of false fire alarms in buildings.
- The impact of automatic sprinklers on building design.
- The role of codes, standards and approvals in delivering fire safety.
- Visual alarm devices - their effectiveness in warning of fire.
- Automatic fire detection and alarm systems, an introductory guide to components and systems BR 510.
- Personal protection watermist systems in the homes of vulnerable people.
Featured articles and news
An architectural technologist in Germany.
3 World Trade Center designed by RSH+P
The struggle to achieve net-zero emissions by 2050.
What is 'agent of change' and who does it protect?
A consistent and measurable approach to home adaptation.
Acknowledging and challenging the realms and interpretations of heritage.
Embodied carbon in construction steel.
A prototype for assessing circularity in buildings.
New Wiki site is set to make BIM mainstream.
FMEA is a step-by-step approach for collecting knowledge about possible points of failure.
The various types and everything else.