- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 28 Oct 2019
Automatic release mechanism
Approved document B, Fire Safety, Volume 2, Buildings other than dwellinghouses (2019 edition), defines an automatic release mechanism as:
A device that normally holds a door open, but closes it automatically if any one of the following occurs.
A device which will allow a door held open by it to close automatically in the event of each or any one of the following:
 Related articles on Designing Buildings Wiki
- Approved documents.
- Door closer.
- Door energy rating.
- Fire detection and alarm systems.
- Fire door.
- Fire Door Inspection Scheme.
- Fire Prevention on Construction Sites.
- Fire protection engineering.
- Hold-open device.
- Inner room.
- Joint fire code.
- Separating floor.
- The Regulatory Reform (Fire Safety) Order 2005.
- Visual alarm devices - their effectiveness in warning of fire.
Featured articles and news
What it is and the threat it faces from development.
Six things structural engineers should do now.
Housing Forum calls for unity from the construction community.
An analysis of benefits, processes, best practices and more.
An interview with Ben Ridley, Director at Architecture for London.
Civil engineers can lead the way.
Cutting-edge tech pairs with building management systems.
BSRIA updates its assessment of the industry.
What happens when it all goes wrong?
Input being gathered by CIOB.
Changes proposed for MHCLG consultation on house building statistics.
Full of passion and acerbic wit. 1 min book review.
Reminding us what is possible.