- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 16 Nov 2020
Automatic release mechanism
A device that normally holds a door open, but closes it automatically if any one of the following occurs.
 Related articles on Designing Buildings Wiki
- Approved documents.
- Door closer.
- Door energy rating.
- Fire detection and alarm systems.
- Fire door.
- Fire Door Inspection Scheme.
- Fire Prevention on Construction Sites.
- Fire protection engineering.
- Hold-open device.
- Inner room.
- Joint fire code.
- Separating floor.
- The Regulatory Reform (Fire Safety) Order 2005.
- Visual alarm devices - their effectiveness in warning of fire.
Featured articles and news
Will you need it ? after June 15 and the new Part O ?
Create an account and write the first of many articles.
CIAT commentary after the first meeting.
Who is to blame?
Research recommends focussing on portfolio success rather than project success.
The revised standard for mapping underground utilities.
Cross-industry steering group seeks support in delivery.
Help us update process pieces from your field.
APM report explores existing practice.
COVID-19 and the importance of mental wellbeing.
As Professionally Qualified Person (PQP).
In order of relevance and with industry responses.
Raising awareness of the impacts of loneliness.
The list is growing, and in more ways than one.
We shouldn’t build new, If we can’t maintain what's built.
Timber Accelerator Hub phase 1 report