- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 05 Sep 2017
Automatic release mechanism
To help develop this article, click ‘Edit this article’ above.
A device which will allow a door held open by it to close automatically in the event of each or any one of the following:
- detection of smoke by automatic apparatus suitable in nature, quality and location;
- operation of a hand-operated switch fitted in a suitable position;
- failure of electricity supply to the device, apparatus or switch;
- operation of the fire alarm system if any.
 Related articles on Designing Buildings Wiki
- Approved documents.
- Door closer.
- Door energy rating.
- Fire detection and alarm systems.
- Fire door.
- Fire Door Inspection Scheme.
- Fire Prevention on Construction Sites.
- Fire protection engineering.
- Hold-open device.
- Inner room.
- Joint fire code.
- Separating floor.
- The Regulatory Reform (Fire Safety) Order 2005.
- Visual alarm devices - their effectiveness in warning of fire.
Featured articles and news
The complex situation where events occur at the same time.
How can Latin America and the Caribbean unlock the digital potential of their new and existing built environment?
CIOB publish a new code of estimating practice.
These relate to a programme where each activity is allocated a price and interim payments made against completion.
Police testing finds that flat door could only withstand fire for half its designed time.
Have a look at these images from a new photography book of buildings being reclaimed by nature.
What does the phrase 'demised premises' mean? Find out here in our introductory article.
New good practice guidance looks at the best way to deliver multi-functional solar car parks.
Philip Hammond suggests the public finances have reached a turning point.
The fifth annual ICE-Topcon lecture looked at how to balance smart technology and security.
Support grows for the Construction (Retention Deposit Schemes) Bill.