- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 16 Nov 2020
Automatic release mechanism
Approved document B, Fire Safety, Volume 2, Buildings other than dwellinghouses (2019 edition), defines an automatic release mechanism as:
A device that normally holds a door open, but closes it automatically if any one of the following occurs.
 Related articles on Designing Buildings Wiki
- Approved documents.
- Door closer.
- Door energy rating.
- Fire detection and alarm systems.
- Fire door.
- Fire Door Inspection Scheme.
- Fire Prevention on Construction Sites.
- Fire protection engineering.
- Hold-open device.
- Inner room.
- Joint fire code.
- Separating floor.
- The Regulatory Reform (Fire Safety) Order 2005.
- Visual alarm devices - their effectiveness in warning of fire.
Featured articles and news
The principles and art of the possible. Book review.
From horse and cart to hypermarket.
How elements and processes work together in a systems approach.
CIOB offers digital guide to proactive methods of working.
Tech will drive professional development in fields tied to infrastructure.
The idea for the structure emerged from the architect's dream.
Changing air tightness requirements prompt testing and revisions.
Government takes steps to revise building safety legislation.
Product can be 'grown' into bricks or used as a self-healing building material.
Anticipating COVID-19's continuing construction disruptions.
Availability payment arrangements involve project performance.
EU responds to COVID-19 with NextGenerationEU plan.