- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 28 Oct 2019
Automatic release mechanism
Approved document B, Fire Safety, Volume 2, Buildings other than dwellinghouses (2019 edition), defines an automatic release mechanism as:
A device that normally holds a door open, but closes it automatically if any one of the following occurs.
A device which will allow a door held open by it to close automatically in the event of each or any one of the following:
 Related articles on Designing Buildings Wiki
- Approved documents.
- Door closer.
- Door energy rating.
- Fire detection and alarm systems.
- Fire door.
- Fire Door Inspection Scheme.
- Fire Prevention on Construction Sites.
- Fire protection engineering.
- Hold-open device.
- Inner room.
- Joint fire code.
- Separating floor.
- The Regulatory Reform (Fire Safety) Order 2005.
- Visual alarm devices - their effectiveness in warning of fire.
Featured articles and news
A material with exciting potential.
ECA-partnered survey shows the clear benefits.
Hire for potential, not competence.
A single knowledge hub for global infrastructure.
Compliance in construction.
The growth of the smart homes market.
Giving professional advice to friends.
Towards a radical eclecticism.
Showing the impact of new buildings on their surroundings.
Soft Landings for refurbishment projects.
An invaluable book for everyone involved in conservation.