- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 28 Oct 2019
Automatic release mechanism
Approved document B, Fire Safety, Volume 2, Buildings other than dwellinghouses (2019 edition), defines an automatic release mechanism as:
A device that normally holds a door open, but closes it automatically if any one of the following occurs.
A device which will allow a door held open by it to close automatically in the event of each or any one of the following:
 Related articles on Designing Buildings Wiki
- Approved documents.
- Door closer.
- Door energy rating.
- Fire detection and alarm systems.
- Fire door.
- Fire Door Inspection Scheme.
- Fire Prevention on Construction Sites.
- Fire protection engineering.
- Hold-open device.
- Inner room.
- Joint fire code.
- Separating floor.
- The Regulatory Reform (Fire Safety) Order 2005.
- Visual alarm devices - their effectiveness in warning of fire.
Featured articles and news
Public engagement in London Borough of Enfield's heritage strategy.
Engineering services in the spotlight.
The Government's Summer 2020 economic update.
Getting organised below the surface.
Securing suitable water systems.
Love them or hate them, they are popping up everywhere.
The initiative to enhance the environment continues.
Could underused community spaces offer an alternative to working from home?
Keeping workers and workplaces safe in the United States.
A history lesson in geographic information systems.
A low tech, easy to use method of extinguishing small fires.
How can these valued spaces be reused?