- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 28 Oct 2019
Automatic release mechanism
Approved document B, Fire Safety, Volume 2, Buildings other than dwellinghouses (2019 edition), defines an automatic release mechanism as:
A device that normally holds a door open, but closes it automatically if any one of the following occurs.
A device which will allow a door held open by it to close automatically in the event of each or any one of the following:
 Related articles on Designing Buildings Wiki
- Approved documents.
- Door closer.
- Door energy rating.
- Fire detection and alarm systems.
- Fire door.
- Fire Door Inspection Scheme.
- Fire Prevention on Construction Sites.
- Fire protection engineering.
- Hold-open device.
- Inner room.
- Joint fire code.
- Separating floor.
- The Regulatory Reform (Fire Safety) Order 2005.
- Visual alarm devices - their effectiveness in warning of fire.
Featured articles and news
A guide to daylight design for commercial buildings.
Two opposite approaches to cost estimating that can work together.
BSRIA reports on propsects for the US construction industry.
ECA research shows lack of preparation amongst survey respondents.
Smart mapping approaches for building better infrastructure.
The importance of emergency planning.
Eight forms of resource optimisation.
CIOB responds to Chancellor Sunak's announcement on jobs and the economy.
Revised guide to competition rules available.
Brick slip soffit systems and intricate brick features.
An innovative engineering approach could have had tragic consequence for NYC.
Some secrets behind how canals work.