Escape routes provide a means of escape from any point in a building to a final exit. Escape routes can be protected or unprotected depending on whether they have a fire-resisting construction or not.
A protected stairway is a stairway that is protected by fire-resisting construction and is used to discharge the occupants of a building through a final exit to a place of safety.
According to Approved Document B, a protected stairway is ‘...designed to provide virtually ‘fire sterile’ areas which lead to places of safety outside the building. Once inside a protected stairway, a person can be considered to be safe from immediate danger from flame and smoke. They can then proceed to a place of safety at their own pace. To enable this to be done, flames, smoke and gases must be excluded from these escape routes, as far as is reasonably possible, by fire-resisting structures or by an appropriate smoke control system, or by a combination of both these methods. This does not preclude the use of unprotected stairs for day-to-day circulation, but they can only play a very limited role in terms of means of escape due to their vulnerability in fire situations.'
 Design of protected stairway
Generally, every internal escape stair should be a protected stairway. They should be relatively free of potential sources of fire and so should not be used for anything else, other than providing a lift well or housing an electricity meter.
The enclosure of a protected stairway should have a fire resistance of not less than 30 min when tested in accordance with BS 476-21 or BS 476- 22, or the European equivalents BS EN 1363, BS EN 1364 or BS EN 1365.
In a building designed for phased evacuation or a stair serving any storey more than 18m high, the stair should be provided with a protected lobby or corridor or a pressure differential system. A protected corridor/lobby is, 'A corridor or lobby which is adequately protected from fire in adjoining accommodation by fire-resisting construction.'
The final exit route from a stairway should be at least as wide as the stair leading to it. Where the escape route from a ground and/or basement floors is formed from the exit route from the stairway, the width of the exit route may need to be increased accordingly and is calculated using the merging flow formula as given in BS 9999 Code of practice for fire safety in the design, management and use of buildings:
W = [(N/2.5) + (60 S)]/80
W = width of final exit, metres
N = number of people served by ground floor storey exit
S = stair width, metres
Where a protected stairway projects beyond, or is recessed from, or is in an internal angle of, the adjoining external wall of the building; then the distance between any unprotected area in the external enclosures to the building and any unprotected area in the enclosure to the stairway should be at least 1.8m.
Related articles on Designing Buildings Wiki
- Escape route.
- Fire compartment.
- Fire resistance.
- Firefighting route.
- Firefighting shaft.
- Protected escape route.
Featured articles and news
Have a look at this incredible Möbius strip-inspired media centre in Beijing.
OMA's plans for new arts centre to revitalise city's culture given planning approval.
Select committee criticises DEFRA for failing to take up its recommendations.
Nicola Sturgeon presents ICE's People's Choice Award to the Forth Road Bridge reopening.
Green paper published for consultation.
Mental health issues affect 80% of construction workers. Read our interview with the founders of a new wellbeing initiative.
Would Stephenson be disappointed by the lack of progress on the high speed transport of Hyperloop?
The immersive pop-up cinema experience that could revolutionise on-site health and safety training.
5 out of 10 filtering facepieces fail HSE tests.
Eleven Magazine announce the winner and runners-up in their Moontopia competition.
As January is the time for hitting the gym, Designing Buildings Wiki lists the best gym architecture in the world.