- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 31 Mar 2020
Emergency lighting is installed in buildings in case of a mains power failure and provides sufficient illumination to allow occupants of the building to evacuate safely. Types of emergency lighting include; emergency exit signs, recessed fluorescent lights, powerful halogen emergency spotlights for larger spaces, emergency ceiling lights and downlights, and so on.
The Regulatory Reform (Fire Safety) Order 2005 requires that 'emergency routes and exits requiring illumination must be provided with emergency lighting of adequate intensity in the case of failure of their normal lighting.'
Approved document B defines emergency lighting as 'lighting for use when the power supply to the normal lighting fails'. It defines escape lighting as 'The part of the emergency lighting that is provided to ensure that the escape route is illuminated at all material times.'
Approved document L defines emergency escape lighting as '......that part of emergency lighting that provides illumination for the safety of people leaving an area or attempting to terminate a dangerous process before leaving.'
In addition to the requirement to illuminate emergency routes and exits, open area lighting may be provided to allow occupants to reach an escape route, and where occupants are involved in activities that may present some danger if they are not completed, there may be high-risk task area lighting. There may also be standby lighting to allow occupants to continue with their normal activities in the event of a power failure.
Emergency lights are powered by back-up batteries. The lights detect when mains power has failed and immediately switch to using the back-up battery. The battery should be capable of powering the light, for a defined period, but as a means of conserving power, the light output may be reduced, sometimes to just 10% of the normal output.
The Fire Precautions (Workplace) Regulations 1997 and BS 5266 part 1 require that building owners test emergency lighting regularly and maintain them in proper working order. Light fittings have a green LED indicator which shows they are charged and functional.
There are three basic types of emergency light fitting:
This type of fitting is designed to operate as a normal light fitting, to be lit continuously and to be controlled along with the other lights in the area. However, if power fails the maintained emergency fitting will continue to operate at a lower light output level. This type of lighting is commonly used in public buildings such as theatres, cinemas and shopping centres.
This type of fitting is normally switched off, but is designed to switch on automatically in the event of a mains power failure. The batteries are continuously charged. These are typically fittings such as emergency exit signs which are not required as part of general lighting. They are commonly used in workplaces such as offices and factories, where there may be more occupant familiarity with the building and the escape routes.
 Other categorisations
They may provide different levels of illumination. See below.
 Technical requirements
A non-obstructed escape route must be lit during an emergency to a minimum of 1 lux. Emergency lighting isn’t required if the open area is less than 60 sq. m and isn’t part of a designated escape route. The exit doors for the emergency escape route must be fitted with signs or an emergency bulkhead light.
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
Smart mapping approaches for building better infrastructure.
The importance of emergency planning.
Eight forms of resource optimisation.
CIOB responds to Chancellor Sunak's announcement on jobs and the economy.
Revised guide to competition rules available.
Brick slip soffit systems and intricate brick features.
An innovative engineering approach could have had tragic consequence for NYC.
Some secrets behind how canals work.
Breaking down possible steps of pre-contract management.
ICE event includes comments from Welsh Government Minister Julie James.
Designing Buildings Wiki becomes the world's first website to adopt the new knowledge standard.