- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 21 Jul 2017
In certain buildings, it can be difficult for the fire and rescue service to safely reach and work close to fires. Under such circumstances additional facilities are required to ensure that there is no delay and to provide a secure operating base. This might include:
A firefighting shaft provides the fire and rescue service with a safe area from which to undertake firefighting operations. They link all necessary floors of a building, providing at least 2 hours of fire resistance to protect fire crews and are connected to fresh air. A firefighting shaft will typically contain a firefighting main, stairway, lobby and sometimes a lift.
 Provision of firefighting shafts
Fire-fighting shafts should be provided in:
- Tall buildings more than 18m high.
- Buildings with deep basements of more than 10m.
- Commercial, shop, industrial or storage buildings that are more than 7.5m high.
If the building has an automatic sprinkler system, adequate shafts should be fitted so that every part of every storey (over 18m above access level) is no more than 60m from a fire main outlet. If no sprinkler system is fitted, this distance reduces to 45m from an outlet which is inside a protected stairway or 60m if it is in a firefighting shaft.
In buildings (apart from blocks of flats), the firefighting stairs and lift should be entered from accommodation, through a firefighting lobby. The firefighting shaft should have a fire main with outlet connections and valves on every storey. For blocks of flats, it is not necessary to have a firefighting lobby.
 Further information
Approved Document B (Fire Safety) has further details on the design and layout of firefighting shafts. Additional guidance can be found in BS 9999: Code of practice for fire safety in the design, management and use of buildings.
 Related articles on Designing Buildings Wiki.
- Approved Document B (Fire Safety).
- BS 9999: Code of practice for fire safety in the design, management and use of buildings.
- Dry riser.
- Escape route.
- Fire and rescue service.
- Fire compartment.
- Fire detection and alarm systems.
- Fire door.
- Fire protection engineering.
- Fire resistance.
- Fire safety design.
- Firefighting lift.
- Firefighting route.
- Inner room.
- Protected escape route.
- Protected stairway.
- Unprotected escape route.
- Wet riser.
Featured articles and news
The complex situation where events occur at the same time.
How can Latin America and the Caribbean unlock the digital potential of their new and existing built environment?
CIOB publish a new code of estimating practice.
These relate to a programme where each activity is allocated a price and interim payments made against completion.
Police testing finds that flat door could only withstand fire for half its designed time.
Have a look at these images from a new photography book of buildings being reclaimed by nature.
What does the phrase 'demised premises' mean? Find out here in our introductory article.
New good practice guidance looks at the best way to deliver multi-functional solar car parks.
Philip Hammond suggests the public finances have reached a turning point.
The fifth annual ICE-Topcon lecture looked at how to balance smart technology and security.
Support grows for the Construction (Retention Deposit Schemes) Bill.