Dry risers are used to supply water within buildings for fire-fighting purposes. The provision of a built-in water distribution system means that fire fighters do not need to create their own distribution system in order to fight a fire and it avoids the breaching of fire compartments by running hose lines between them.
Dry risers do not contain water when they are not being used, but are charged with water by fire service pumping appliances when necessary. This is as opposed to wet risers, which are permanently charged with water.
Dry risers have an inlet connector at rescue service vehicle access level and landing valves at locations on each floor. Part B of the building regulations (Fire Safety) requires that fire mains are provided in buildings that are more than 18m tall. In buildings less than 50m tall, fire mains can be either dry or wet risers, however, where a building extends to more than 50m above the rescue service vehicle access level, wet risers are necessary as the pumping pressure required to charge the riser is higher than can be provided by a fire service appliance, and to ensure an immediate supply of water is available at high level.
Each inlet connector must be within 18m of a fire service appliance access. Inlet connectors are typically contained in accessible, but secure enclosures on the external face of buildings and are identified as a ‘dry riser inlet’.
Dry risers themselves should be within fire-fighting shafts, and where necessary in protected escape stairs. Dry-riser outlets, or landing valves may be located in protected lobbies, stairs or enclosures where these are available.
At the top of dry-riser pipework an air valve is provided to allow air in the dry riser to escape when the riser is charged with water. There is often also a roof-level testing outlet.
Dry risers should be inspected and tested regularly to ensure equipment is functioning correctly and ready for use. Problems can be very serious in the event of a fire, and are typically caused by vandalism or theft, blockages or pipework failure or by connection failure or outlets being open.
 Related articles on Designing Buildings Wiki
- Approved documents.
- Building regulations.
- Fire and rescue service.
- Firefighting route.
- Joint fire code.
- Protected escape route.
- The Regulatory Reform (Fire Safety) Order 2005.
- Unprotected escape route.
- Wet riser.
 External references.
Featured articles and news
There were over 1,400 new articles added to Designing Buildings Wiki in 2016. Here are the top 15 most popular.
MVRDV reveal designs for a strange holiday villa in Taiwan.
New milestone achieved with launch of new safety lanyard for working from height.
A quick introductory article about preliminaries in construction.
Brandenburg Gate - an historic structure that went from symbolising German partition to European unity.
A discussion between construction key players and leading insurers on the future outlook for construction insurance.
New guide from BSRIA on building performance evaluation in domestic buildings.
Rogers Stirk Harbour and Partners complete new trio of towers at Sydney Harbour.
With a new government consultation underway, ICE look at creating a smarter, more flexible energy system.
British Antarctic Survey announces research station is to relocate 23km due to growing crack in the ice shelf.
A great example of mimetic architecture with the Fish Building of India.