Dry risers are used to supply water within buildings for fire-fighting purposes. The provision of a built-in water distribution system means that fire fighters do not need to create their own distribution system in order to fight a fire and it avoids the breaching of fire compartments by running hose lines between them.
Dry risers do not contain water when they are not being used, but are charged with water by fire service pumping appliances when necessary. This is as opposed to wet risers, which are permanently charged with water.
Dry risers have an inlet connector at rescue service vehicle access level and landing valves at locations on each floor. Part B of the building regulations (Fire Safety) requires that fire mains are provided in buildings that are more than 18m tall. In buildings less than 50m tall, fire mains can be either dry or wet risers, however, where a building extends to more than 50m above the rescue service vehicle access level, wet risers are necessary as the pumping pressure required to charge the riser is higher than can be provided by a fire service appliance, and to ensure an immediate supply of water is available at high level.
Each inlet connector must be within 18m of a fire service appliance access. Inlet connectors are typically contained in accessible, but secure enclosures on the external face of buildings and are identified as a ‘dry riser inlet’.
Dry risers themselves should be within fire-fighting shafts, and where necessary in protected escape stairs. Dry-riser outlets, or landing valves may be located in protected lobbies, stairs or enclosures where these are available.
Dry risers should be inspected and tested regularly to ensure equipment is functioning correctly and ready for use. Problems can be very serious in the event of a fire, and are typically caused by vandalism or theft, blockages or pipework failure or by connection failure or outlets being open.
 Related articles on Designing Buildings Wiki
- Approved documents.
- Building regulations.
- Fire and rescue service.
- Firefighting route.
- Joint fire code.
- Protected escape route.
- The Regulatory Reform (Fire Safety) Order 2005.
- Unprotected escape route.
- Wet riser.
 External references.
Featured articles and news
PCSAs enable clients to employ contractors before the main contract commences. Read our introductory article.
ICE 200 brings together transformative projects from the past 200 years - and the engineers behind them.
Dame Judith Hackitt hosts an industry summit to kick start the second phase of the review.
This article explains the Buildings Regulations completion certificate, what it is, and when its needed.
Graphene has many potential applications, but when will it start being used in civil engineering?
Increasing productivity – now more than ever as we lead up to Brexit – should be the sector’s number one priority in 2018.
Carillion's collapse causes Construction Leadership Council to delay the construction sector deal report.
Urban Heritage, Development and Sustainability: international frameworks, national and local guidance.
What will the General Data Protection Regulations (GDPR) mean for you when they come into force in May?
Business Secretary chairs a new taskforce to monitor and advise on mitigating the impacts of Carillion’s liquidation.
Sir John Armitt is appointed the new chair of the National Infrastructure Commission.
High quality and high density homes - is it what we need or is it storing up trouble?