- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 15 Sep 2020
Dry risers are used to supply water within buildings for fire-fighting purposes. The provision of a built-in water distribution system means that fire fighters do not need to create their own distribution system in order to fight a fire and it avoids the breaching of fire compartments by running hose lines between them.
Dry risers do not contain water when they are not being used, but are charged with water by fire service pumping appliances when necessary. This is as opposed to wet risers, which are permanently charged with water.
Dry risers have an inlet connector at rescue service vehicle access level and landing valves at locations on each floor. Part B of the building regulations (Fire Safety) requires that fire mains are provided in buildings that are more than 18 m tall. In buildings less than 50m tall, fire mains can be either dry or wet risers, however, where a building extends to more than 50 m above the rescue service vehicle access level, wet risers are necessary as the pumping pressure required to charge the riser is higher than can be provided by a fire service appliance, and to ensure an immediate supply of water is available at high level.
Each inlet connector must be within 18 m of a fire service appliance access. Inlet connectors are typically contained in accessible, but secure enclosures on the external face of buildings and are identified as a ‘dry riser inlet’.
Dry risers themselves should be within fire-fighting shafts, and where necessary in protected escape stairs. Dry riser outlets, or landing valves, may be located in protected lobbies, stairs or enclosures where these are available.
Dry risers should be inspected and tested regularly to ensure equipment is functioning correctly and ready for use. Problems can be very serious in the event of a fire, and are typically caused by vandalism or theft, blockages or pipework failure or by connection failure or outlets being open.
 Find out more
 Related articles on Designing Buildings Wiki
- Approved documents.
- Building regulations.
- Fire and rescue service.
- Firefighting route.
- Joint fire code.
- Protected escape route.
- The Regulatory Reform (Fire Safety) Order 2005.
- Unprotected escape route.
- Vertical riser.
- Wet riser.
 External references.
Featured articles and news
An introduction to the 5 core principles of lean.
Can the profession use its skills to save the world from climate change?
How faulty science resulted in sanitation reform.
Improving facilities, accessibility and overall appearance.
Free download of TG 12/2021 available.
TESP works with The Youth Group to form skill sharing network.
Big tech collaborates on platform for the built environment.
Letter signed by 21 organisations sent to MHCLG.
A look at the Government's strategic approach.
Steps to help reduce the spread of infection inside buildings.
This social media-centred hobby can be both dangerous and illegal.
Millwork wall treatment with a long and illustrious history.
HSE introduces cumulative exposure calculator.
The Edwardians and their houses.
Click the button to subscribe.