- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 17 Jul 2018
Dry risers are used to supply water within buildings for fire-fighting purposes. The provision of a built-in water distribution system means that fire fighters do not need to create their own distribution system in order to fight a fire and it avoids the breaching of fire compartments by running hose lines between them.
Dry risers do not contain water when they are not being used, but are charged with water by fire service pumping appliances when necessary. This is as opposed to wet risers, which are permanently charged with water.
Dry risers have an inlet connector at rescue service vehicle access level and landing valves at locations on each floor. Part B of the building regulations (Fire Safety) requires that fire mains are provided in buildings that are more than 18 m tall. In buildings less than 50m tall, fire mains can be either dry or wet risers, however, where a building extends to more than 50 m above the rescue service vehicle access level, wet risers are necessary as the pumping pressure required to charge the riser is higher than can be provided by a fire service appliance, and to ensure an immediate supply of water is available at high level.
Each inlet connector must be within 18 m of a fire service appliance access. Inlet connectors are typically contained in accessible, but secure enclosures on the external face of buildings and are identified as a ‘dry riser inlet’.
Dry risers themselves should be within fire-fighting shafts, and where necessary in protected escape stairs. Dry riser outlets, or landing valves, may be located in protected lobbies, stairs or enclosures where these are available.
Dry risers should be inspected and tested regularly to ensure equipment is functioning correctly and ready for use. Problems can be very serious in the event of a fire, and are typically caused by vandalism or theft, blockages or pipework failure or by connection failure or outlets being open.
 Find out more
 Related articles on Designing Buildings Wiki
- Approved documents.
- Building regulations.
- Fire and rescue service.
- Firefighting route.
- Joint fire code.
- Protected escape route.
- The Regulatory Reform (Fire Safety) Order 2005.
- Unprotected escape route.
- Vertical riser.
- Wet riser.
 External references.
Featured articles and news
When is there a right to light, and what happens if it is obstructed?
What would the nationalisation of economic infrastructure mean for GB?
A new guide to improving value by reducing design error.
We've reached 80,000 page views a day and 10,000 registered users. Why not join them?
A masterplan is a framework within which a location is encouraged to develop or change. Read our introductory article.
New consultation announced on a specialist Housing Court to settle landlord-tenant disputes.
ICE responds to a transport consultation advising the government to make decisions enabling more inclusive cities.
BRE and Loughborough University complete first phase refurbishment of demonstration home.
How the risk of collapse of fibrous plaster ceilings is being addressed in theatres.
If you’re a great writer and have practical experience of the construction industry, it could be you.
Frustrated by long documents or technical jargon? Put off by sign-up forms or costs? Take this 5 min survey to help improve construction knowledge.