- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 27 Apr 2021
Data cables and the Construction Products Regulations
|**In addition to the flame propagation classes for cables outlined in the table above, there are three other sub-categories of cable fire performance for the classes B1ca to Dca. More information about these is available in the application guide, Cable and CPR, available exclusively to ECA Members.|
More than ever, data communications and control cables are built into the fabric of homes and offices, alongside traditional power cables. But with more connectivity comes a larger number of conduits along which a fire could spread. Data comms, power and control cables come under the Construction Products Regulation (CPR), designed to consider the reaction of cables in a fire. As such, they must be selected carefully before an installation.
Government statistics show that, in England, in 2017/18, almost 31,000 fires involving fatalities, casualties or rescues occurred in homes, and over 15,000 occurred in other buildings (offices, shops, hospitals, schools, etc). In about seven per cent (approximately 3,400) of these fires, wiring insulation was identified as the main material responsible for the fire propagating.
Data communications cables currently available in the UK are insulated, bedded or sheathed with materials such as PVC, TPE, Nylon, metal weaving and mercerised cotton. Each reacts differently to fire and will have a different EuroClass rating.
In the event of a fire, these materials may, to different degrees, produce toxic smoke and acidic gases. They might also act as a fuel, helping to propagate flames along cables and through a building and its voids. This danger is further exacerbated by falling flaming droplets caused by melting.
The smoke and gases given off by burning cables can hinder a building’s occupants from escaping a in event of a fire. It can also inhibit firefighters by blocking their vision and reducing the effectiveness of emergency lighting.
Despite Britain’s intention to leave the European Union, it is understood that CE marking will remain a pre-requisite for any manufacturer, importer or distributor wishing to sell their cables within the EU. What we know for certain is that CPR will still apply to all construction sales, both in the EU and in the UK.
 Top of the class
Under CPR, European Classification replaces IEC 60332-1-2:2004, which was the previous benchmark for assessing the flammability of cables. Because methods of testing cables have changed drastically, direct comparisons to the old standard are not exactly straightforward. The table at the top of this page clarifies the classes.
It is clear that a cable in class Aca would be the best in terms of fire performance, and an Eca cable would be seen as the worst. Class Fca cables should be used with caution or avoided entirely if possible, as it would be of unknown origin with no identification markings or labelling.
‘Best practice’ would dictate that safety should always be the first consideration, especially for buildings where vulnerable people may be restricted in their ability to escape a fire, such as care homes or hospitals.
Similarly, high-rise buildings, buildings with high fire risk or buildings with high traffic, such as offices, shopping centres or conference centres, would also warrant higher levels of safety from the hazards of burning cables.
 About the CPR
An obvious benefit of the CPR is that it enables designers, specifiers and other industry professionals, as well as consumers, to compare the safety performance of products that may have come from different manufacturers. In other words, it allows easy like-for-like comparison between products.
- Since 1 July 2017, it has been a legal requirement in the UK for manufacturers, distributors or importers to make a Declaration of Performance (DoP) and apply CE marking on relevant cables (i.e. those intended to be permanently installed within a building).
 About this article
 Related articles on Designing Buildings Wiki
- Electrical appliance.
- Electrical consumption.
- Electrical energy.
- Electrical equipment.
- Electrical installation.
- Electrical power.
- Electrical safety.
- Electricity bill.
- Attestation of conformity.
- British Board of Agrément.
- Building regulations.
- CE marking.
- Construction Products Regulation if there is no Brexit deal.
- Energy related products regulations.
- European Technical Approval.
- Fire dampers.
- Quality control.
Featured articles and news
Fropm practice to research and the business of materials.
Terms, histories, theories and practices.
Alteration to Demolition and everything in between.
And CIOB's response.
Presidential update from CIAT's Eddie Weir PCIAT.
Rates freeze, NI cuts, full expensing; early election?
Could this be a remedy for condensation, damp or mould?
Unlocking a Healthier Tomorrow
Call for ministerial group and National Retrofit Delivery Plan.
The Great Transformation 1860–1920. Book review.
Including the devolved governments, CIOB, ECA, APM and IHBC.
AT awards small to medium size project category winner.
Formal and informal adaptive re-use or new use of buildings.
Temperatures hit new highs, yet world fails to cut emissions (again).
No longer enforcing certain waste transfer documentation.
Winners reactions during the event at the Park Plaza Hotel.
An exciting opportunity for stakeholders to collaborate.
Report from the BSRIA Briefing 2023, Cleaner Air, Better Tomorrow.