ACM cladding testing by BRE
The Government acted to support owners and residents of high-rise buildings to ensure fire safety in the light of the Grenfell Tower fire. Landlords engaged in a checking and testing process for Aluminium Composite Material (ACM) cladding.
The initial tests conducted at BRE on behalf of the Department for Communities and Local Government (DCLG) were a screening test to identify which ACM panels were of concern. They test the filler in the core of the panel to check if it is of limited combustibility (category 1) or not (category 2 or 3).
The filler is one element of the overall cladding system. If the panel core fails the test, landlords are expected to take the recommended interim fire safety measures issued by government on 22 June 2017.
The equipment and procedures used in the screening tests were based on the BS EN ISO 1716:2010 test standard. As the purpose of this testing was to quickly and reliably screen the core material within the panel, the full procedures set out in that standard were not followed as they were unnecessary to determine which type of panel had been submitted for the screening test. These screening tests should not be confused with a formal classification test against the standard.
You can read further information and detail on the testing process on the gov.uk website.
An independent expert panel was set up to advise the government on other urgent steps that should be taken to improve fire safety. BRE's Chief Executive, Dr Peter Bonfield sits on that panel. They will issue advice imminently to clarify further steps landlords could take to inform their decisions on the cladding systems they have in place, and on checking insulation and other components of typical wall construction.
On 6 July 2017, the Grenfell Tower independent expert advisory panel advised that further testing should be carried out by BRE to establish how different types of ACM cladding behave in a fire in combination with different types of insulation. This, they suggest would help landlords decide what further measures may be needed to make their buildings safe.
The tests will look at 6 combinations of 3 different types of ACM cladding, with polyethylene, fire retardant polyethylene, and non-combustible mineral cores, combined with insulation of rigid polyisocyanurate foam and non-combustible mineral wool. The tests will be carried out in accordance with BS 8414, and involve building complete cladding systems 9 metres tall and then subjecting them to a severe fire. The results will be made publicly available, but landlords should take professional advice on the implications for their buildings.
 Test 1
The first results of these tests were revealed on 28 July 2017, when DCMS announced that a system comprising ACM cladding with polyethylene filler (Category 3) and foam insulation, with fire breaks and cavity barriers in place did not satisfy the requirements of the building regulations. 82 buildings are thought to have this combination of materials in their wall construction. Ref https://www.gov.uk/government/news/first-systems-test-reaffirms-actions-for-landlords
Following these results, the government issued further advice for landlords of affected buildings. Ref https://www.gov.uk/government/publications/advice-for-building-owners-large-scale-wall-system-test
 Test 2
On 2 August 2017, the government announced that the second series of tests had been completed, testing a system consisting of ACM cladding with a polyethylene filler (category 3) with stone wool insulation. The Grenfell Tower independent expert advisory panel advised that the combination does not meet current building regulation guidance. There are 111 buildings known to use this system. Ref https://www.gov.uk/government/news/government-fire-safety-testing-programme-continues
 Test 3
On 8 August, results of the third series of tests was published, consisting of ACM cladding with a fire retardant polyethylene filler (category 2 in screening tests) with PIR foam insulation. Again, the Grenfell Tower independent expert advisory panel advised that the combination of materials does not meet current Building Regulations guidance. The government reported that there are 13 buildings over 18 metres tall in England known to this combination. It was also reported that to further build the evidence available, the government has commissioned a seventh large scale test on ACM cladding with fire retardant polyethylene filler (category 2 in screening tests) with phenolic foam insulation. Ref https://www.gov.uk/government/news/further-results-published-from-governments-fire-testing-programme
 Test 4
On 11 August, the results of the fourth round of tests was published, relating to ACM cladding with a fire resistant polyethylene filler (category 2 in screening tests) and stone wool insulation (a form of mineral wool). 13 buildings over 18 metres tall in England are known to have this system of cladding. The combination of materials passed the test and so can be compliant with the Building Regulations when installed and maintained properly. This means it could offer a possible solution for buildings with cladding systems that have failed tests. However, building owners need to take professional advice to ensure the safety of their building. Following the tests, Advice for building owners: large-scale wall system test 4 was published by the Grenfell Tower independent expert advisory panel. Ref https://www.gov.uk/government/news/latest-government-large-scale-fire-safety-test-results-published
 Test 5
On 14 August, the results of the fifth test, assessing ACM cladding with a limited combustibility filler (category 1 in screening tests) with PIR foam insulation were published. The Grenfell Tower independent expert advisory panel reported that these results show the combination of materials can comply with the building regulations. The government is not aware of any buildings over 18 metres in England using this combination of materials, but it could offer a solution for buildings which have been identified as a fire hazard through previous large-scale tests. Ref https://www.gov.uk/government/news/second-wall-cladding-system-passes-latest-government-fire-safety-test
 Related articles on Designing Buildings Wiki
- BRE articles on Designing Buildings Wiki.
- ACM cladding.
- Approved Document B.
- BS 8414 Fire performance of external cladding systems.
- BS 9999: Code of practice for fire safety in the design, management and use of buildings.
- BS 9991:2015 Fire safety in the design, management and use of residential buildings. Code of practice.
- Celotex RS5000 PIR insulation.
- Cladding for buildings.
- Grenfell Tower articles.
- Grenfell Tower fire.
- Grenfell Tower independent expert advisory panel.
- Independent review of the building regulations and fire safety.
Featured articles and news
Four ways in which smart cities could make our lives better.
Mayor Sadiq Khan announces new Greener City Fund in drive to make London the first 'National Park City'.
BSRIA announce UKAS accreditation for sound absorption testing.
The full terms of reference are published for the Grenfell Tower Inquiry.
Read our introductory article into the role and practice of the architect.
Despite dividing opinion since its 1955 completion, Stalin's gift to Poland, the PKiN, is still Warsaw's most recognisible landmark.
Graduate Engineer Brittany Harris asks, what makes a great place to work?
Mayor Sadiq Khan publishes new guidance aimed at fast-tracking affordable housing projects through planning.
An estimated 90% of our time is spent inside, so could urban allotments be the answer to increasing health and wellbeing?
Why disputes occur and how they can be avoided.
Understand each building and its needs before exploring technical solutions and hiring consultants.
‘Device to Root Out Evil’ - an upside-down, New England-style church built with its steeple in the ground.