Heat recovery for buildings
To help develop this article, click ‘Edit this article’ above.
Heat recovery is the process of collecting and re-using heat that is generated from any process where the heat would otherwise be lost (ref The Carbon Trust, 2011). This can help reduce the energy consumption of the process or the heat can be used elsewhere, reducing running costs and carbon emissions. Heat recovery devices can be used in most buildings since the majority use energy for heating, cooling, ventilation or some may house industrial processes that generate heat.
Sources of waste heat that might provide opportunities heat recovery include:
- Ventilation systems.
- Refrigeration units and chiller units.
- Power generation plant.
- Plant cooling systems.
- Hot liquid effluents and high-temperature exhaust gasses.
This 'waste' heat can be recovered and re-used for applications such as; heating water, pre-heating fresh air for building ventilation systems, drying processes, power generation, pre-heating combustion air for furnaces, boilers and so on.
Methods for heat recovery include:
- Gas (or vapour) to liquid heat exchange.
- Air-to-air heat heat exchange.
- Liquid-to-liquid heat exchange.
- Direct ducting of hot air.
- Use of steam power blowdown.
- Heat captured during phase change.
- Heat recovery from condensers.
The government document The Future of Heating: Meeting the Challenge (March 2013) highlighted the potential of heat recovery for helping reduce UK carbon emissions. In June 2013, a more detailed study was commissioned which found a total of 48 terrawatt-hours (TWh) per year of industrial waste heat across eight energy intensive industries; oil refining, iron and steel, food and drink, pulp and paper, chemical, glass, cement and ceramics. It identified 11 TWh/yr with technical potential and 8 TWh/yr with economic potential. The study identified commercially viable heat recovery for all eight industries.
 Related articles on Designing Buildings Wiki.
- Air conditioning.
- Air handling unit.
- Chiller unit.
- Coefficient of Performance CoP.
- District energy.
- Ecobuild 2016 - Making the business case for large scale retrofit investment.
- Exhaust air heat pump.
- Geothermal pile foundations.
- Gross calorific value.
- Heat exchanger.
- Heat pump.
- Heat recovery ventilation.
- Mechanical ventilation.
- Variable refrigerant flow.
- Zero Bills Home.
 External references
Featured articles and news
Why is this American teapot-shaped gas station historically significant? Find out here.
Plans for the first phase of Vastint’s 16.5-acre Tetley Brewery development project get the green light.
This article explores the question, how should we regulate the real estate industry?
Specialist regeneration and investment developer UandI announces ambitions with new Manchester office.
Concrete will have to be demolished and replaced in Hinkley Point tunnels.
Do you have a great idea for how tomorrow's challenges can be met by today's buildings? Enter our ideas competition today.
A new exhibition on humanitarian shelter design will open on BRE's Innovation Park next month.
ICE London Air Quality Taskforce launches plan to help clean up London’s polluted air.
From neolithic to neo-modernism, have a read of our summary of the main architectural styles.
In the heritage sector, sustainable development should be discussed in the wider context of place and planning.
The cost efficiency of sprinklers compared to other fire protection measures.
Lord Adonis warns the UK faces gridlock on the roads, railways and in the skies.
The Government sets out its blueprint for hitting the fifth carbon budget.