- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 21 Feb 2018
Air permeability testing
See also: Air tightness in buildings.
Approved document F, Ventilation, defines airtightness as ‘…a general descriptive term for the resistance of the building envelope to infiltration with ventilators closed. The greater the airtightness at a given pressure difference across the envelope, the lower the infiltration.’
It suggests that air permeability is ‘…the physical property used to measure the airtightness of the building fabric. It is defined as air leakage rate per hour per square metre of envelope area at a test reference pressure differential across the building envelope of 50 Pascal (50 N/m2). The design air permeability is the target value set at the design stage.
In April 2002 the UK government introduced legislation to enforce standards of building air tightness. This was intended to: lower running costs; verify the standards of materials, components and workmanship; prevent uncomfortable drafts and avoid condensation problems.
This is done by air permeability testing (air tightness, air infiltration or blower door testing), which measures the air leakage rate per hour per square metre of building envelope area at a test reference pressure differential across the building envelope of 50 Pascal (50 N/m2).
Generally this involves mounting a door, incorporating a fan, into the frame of an external door opening. The fan is used to depressurise the building by extracting air, and the resulting difference between the external and internal pressure can be used to calculate the permeability of the building envelope (given that the area of envelope is known). This permeability is an indicator of how well sealed the building is, and whether there are openings in the envelope. Testing requires that fires are put out, doors and windows are closed and ventilators are shut or sealed.
The method for testing required by the building regulations is set out in ATTMA TSL1 (for dwellings) and ATTMA TSL2 (for non-dwellings).
The regulations set a limiting air permeability of 10 [email protected] (metres cubed, per hour, per metre squared of external building envelope area) and require that the Building Emission Rate (BER, or Dwelling Emission Rate (DER) for dwellings) calculated using the assessed air permeability does not exceed the Target Emission Rate (TER).
Testing is required on all residential developments (this may be a sample of units) and non-dwellings. buildings with a useful floor area less than 500 m2 MAY be exempt. Where testing is not carried out, an assessed air permeability of 15 m3/h.m2 must be used in calculations.
On large developments, where a specific dwelling is not tested, the assessed air permeability is the average test result obtained from other dwellings of the same dwelling type on the development, increased by 2.0 m3/h.m2.
In compartmentalised buildings where pressure testing the whole unit may be impractical, testing may be carried out on a representative area.
Air permeability testing can be carried out as an isolated study, or may be provided as part of a complete service to demonstrate Part L compliance (including Standard Assessment Procedure (SAP) calculations and Energy Performance Certificates (EPCs)) or may be part of an overall energy audit. Ideally, it should not be carried out simply as a compliance test, but should include an assessment of details, and diagnostic tests such as infrared thermography and if necessary smoke tests to pinpoint air leakage paths.
--ATTMA 13:12, 24 February 2015 (UTC)
 Related articles on Designing Buildings Wiki
- Air change rates.
- Air infiltration.
- Air permeability in isolation rooms.
- Air tightness in buildings.
- Approved documents.
- Building emission rate.
- Building services compliance with the building regulations.
- Domestic ventilation systems performance.
- Draughts in buildings.
- Dwelling emission rate.
- Dwelling type.
- Energy audit.
- Energy performance certificates.
- Infrared thermography.
- Performance gap.
- Standard assessment procedure.
- Target emission rate.
- The history of non-domestic air tightness testing.
 External references
- ATTMA (Air Tightness Testing and Measurement Association).
- iATS (the Independent Air tightness Testing Association)
- ATTMA TSL1 (ATTMA Technical Standard for dwelling testing)
- ATTMA TSL2 (ATTMA Technical Standard for non-dwelling testing)
- BINDT (British Institute of Non-Destructive Testing)
- USA government, blower door tests.
Featured articles and news
How to get results with building life cycle assessment.
Government publishes a prospectus inviting proposals for new 'garden communities'.
The Morandi motorway bridge in Genoa collapses during rainstorm while undergoing maintenance works.
'Developed design' is a phrase coined by the RIBA for their 2013 Plan of Work. But what does it actually mean?
New green paper published aiming to rebalance the relationship between landlords and residents and tackle stigma.
RIBA calls for a comprehensive ban on combustible materials.
Lump sum contracts can be referred to as ‘fixed price’ contracts, although strictly this is not correct. Find out more here.
Ramboll offer guidance to civil engineers on how to make projects 'off-site ready'.
Government announces its Rough Sleeping Strategy, with further funding for social housing.
An overlooked architect who deserves to be celebrated for his wide range of buildings.
The Home Quality Mark ONE technical manuals for new homes are now available.