Air permeability testing
See also: Air tightness in buildings.
Approved document F, Ventilation, defines airtightness as ‘…a general descriptive term for the resistance of the building envelope to infiltration with ventilators closed. The greater the airtightness at a given pressure difference across the envelope, the lower the infiltration.’
It suggests that air permeability is ‘…the physical property used to measure the airtightness of the building fabric. It is defined as air leakage rate per hour per square metre of envelope area at a test reference pressure differential across the building envelope of 50 Pascal (50 N/m2). The design air permeability is the target value set at the design stage.
In April 2002 the UK government introduced legislation to enforce standards of building air tightness. This was intended to: lower running costs; verify the standards of materials, components and workmanship; prevent uncomfortable drafts and avoid condensation problems.
This is done by air permeability testing (air tightness, air infiltration or blower door testing), which measures the air leakage rate per hour per square metre of building envelope area at a test reference pressure differential across the building envelope of 50 Pascal (50 N/m2).
Generally this involves mounting a door, incorporating a fan, into the frame of an external door opening. The fan is used to depressurise the building by extracting air, and the resulting difference between the external and internal pressure can be used to calculate the permeability of the building envelope (given that the area of envelope is known). This permeability is an indicator of how well sealed the building is, and whether there are openings in the envelope. Testing requires that fires are put out, doors and windows are closed and ventilators are shut or sealed.
The regulations set a limiting air permeability of 10 [email protected] (metres cubed, per hour, per metre squared of external building envelope area) and require that the Building Emission Rate (BER, or Dwelling Emission Rate (DER) for dwellings) calculated using the assessed air permeability does not exceed the Target Emission Rate (TER).
Testing is required on all residential developments (this may be a sample of units) and non-dwellings. buildings with a useful floor area less than 500 m2 MAY be exempt. Where testing is not carried out, an assessed air permeability of 15 m3/h.m2 must be used in calculations.
On large developments, where a specific dwelling is not tested, the assessed air permeability is the average test result obtained from other dwellings of the same dwelling type on the development, increased by 2.0 m3/h.m2.
In compartmentalised buildings where pressure testing the whole unit may be impractical, testing may be carried out on a representative area.
Air permeability testing can be carried out as an isolated study, or may be provided as part of a complete service to demonstrate Part L compliance (including Standard Assessment Procedure (SAP) calculations and Energy Performance Certificates (EPCs)) or may be part of an overall energy audit. Ideally, it should not be carried out simply as a compliance test, but should include an assessment of details, and diagnostic tests such as infrared thermography and if necessary smoke tests to pinpoint air leakage paths.
--ATTMA 13:12, 24 February 2015 (UTC)
 Related articles on Designing Buildings Wiki
- Air change rates.
- Air infiltration.
- Air tightness in buildings.
- Approved documents.
- Building emission rate.
- Building services compliance with the building regulations.
- Domestic ventilation systems performance.
- Draughts in buildings.
- Dwelling emission rate.
- Dwelling type.
- Energy audit.
- Energy performance certificates.
- Infrared thermography.
- Performance gap.
- Standard assessment procedure.
- Target emission rate.
- The history of non-domestic air tightness testing.
 External references
- ATTMA (Air Tightness Testing and Measurement Association).
- iATS (the Independent Air tightness Testing Association)
- ATTMA TSL1 (ATTMA Technical Standard for dwelling testing)
- ATTMA TSL2 (ATTMA Technical Standard for non-dwelling testing)
- BINDT (British Institute of Non-Destructive Testing)
- USA government, blower door tests.
Featured articles and news
Read about the launch event for our major new report about the worrying and widening construction knowledge gap.
We've analysed 6 million pieces of data to reveal that the knowledge framework underpinning the construction industry is no longer fit for purpose.
Retrofitting traditional buildings depends on understanding how they differ from modern construction.
The theme for BSRIA's 2017 Briefing is 'Solutions to Tomorrow’s Challenges in Today’s Buildings'.
Dealing more than 1,700 consultations was just one of last year’s tasks for the Gardens Trust.
Read about the history behind one of California's most iconic buildings, the Griffith Observatory.
ICE examine just how close we are to providing subsidy-free low carbon electricity.
Have a look at MAD Architects' design proposal for renovating Montparnasse Tower into a concave mirror.
This article examines the legal issues behind off-site goods and materials.
Read about how technology is changing the real estate industry.
BRE Global introduce the first registration scheme for Suitably Qualified Security Specialists.