- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 15 Feb 2018
Air change rates
Air is continuously exchanged between buildings and their surroundings as a result of mechanical and passive ventilation and infiltration through the building envelope. The rate at which air is exchanged is an important property for the purposes of ventilation design and heat loss calculations and is expressed in ‘air changes per hour’ (ach). If a building has an air change rate of 1 ach, this equates to all of the air within the internal volume of the building being replaced over a 1 hour period.
 Calculating air change rates
A number of techniques are available for calculating the air change rate of a building. The choice of method depends on the accuracy required. The most straightforward method relies on the use of a simple mathematical equation, while the most complex methods use computational analysis and consider many different variables (such as computational fluid dynamics).
The basic method calculates air change rates using the following equation:
n = 3,600 x q / V
n = Air changes per hour (ach)
q = Fresh air flow rate (m3/s)
V = Volume of the room (m3)
 Measuring air change rates
Air change rates resulting from ventilation can be quantified by measuring the air velocity at selected positions within supply ducts. The velocities are normally measured using a pitot tube connected to a pressure gauge or manometer, or using a hot wire probe and meter.
Tracer gas measurement can be used to determine the average air change rate for naturally'-'ventilated spaces' and to measure infiltration (air tightness)'. To do this, a detectable, non-toxic gas is released into the space and the reduction in its concentration within the internal atmosphere is monitored over a given time period.' For more information see: Air permeability testing.
 Legislation and guidance
Specific air change rates are required in buildings to control internal temperatures and to introduce clean, oxygen-rich air and remove stale, humid air. The requirements will vary depending on a number of factors including; the type of space, the level of occupation and usage and the geographical location of the building.
Approved document F sets out the minimum requirements for ventilation to provide comfortable conditions and to prevent surface and interstitial condensation. Approved document F expresses air change rates in a number of different ways:
- air changes per hour.
- litres per second (l/s).
- l/s per m^2 of internal floor area.
- l/s per piece of equipment.
- l/s per person.
A wide range other guidance is also available, including CIBSE KS17: Indoor air quality and ventilation, which provides information about the required air change rates to achieve acceptable indoor air quality, and BS 5925: Code of practice for ventilation principles and designing for natural ventilation which sets out recommended air flow rates for natural ventilation.
 Related articles on Design Buildings Wiki
- Air infiltration.
- Air permeability testing.
- Air quality.
- Air Quality Taskforce.
- Air tightness in buildings.
- Computational fluid dynamics.
- Draughts in buildings.
- Indoor air quality.
- The history of non-domestic air tightness testing.
 External references
- Building Regulations: Approved Document F – Ventilation.
- CIBSE KS17: Indoor Air Quality and Ventilation.
- CIBSE Guide B: Heating, ventilating, air conditioning and refrigeration.
- BS 5925: Code of practice for ventilation principles and designing for natural ventilation.
Featured articles and news
Balfour Beatty fined £500,000 for exposing workers to hand-arm vibration.
James Brokenshire launches a consultation on banning combustible cladding.
A year after Grenfell, we have a collection of 30 articles telling you everything you need to know.
ICE publish a policy paper on the UK’s future interconnectivity with the EU and the challenges for infrastructure.
Detailed guidance about construction waste management.
The changing identity of London communities in the face of rapid urbanisation.
Can you help? We have 300 industry acronyms beginning with 'C' but none beginning with 'Y'.
From the sinister Carceri d’Invenzione to the triple portrait of Sir Watkin Williams-Wynn and his Grand Tour travelling companions.
BSRIA launch the 5th edition of the Design Framework for Building Services (BG 6/2018).
Stella Rimmington famously said the construction industry was just as tricky as the KGB.
Construction site visitor cards are to be withdrawn.
3 WTC opens, RSHP’s first built project in New York.