- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 21 Apr 2021
Commissioning building systems
‘…the advancement of a fixed building service after all or part of the system has been installed, replaced or altered. The system is taken from a state of static completion to working order. Testing and adjusting, as necessary, ensure that the whole system uses no more fuel and power than is reasonable in the circumstances, without compromising the need to comply with health and safety requirements.
'For each system, commissioning includes the following: setting-to-work; regulation (that is, testing and adjusting repetitively) to achieve the specified performance; calibration, setting up and testing of the associated automatic control systems; and recording of the system settings and the performance test results that have been accepted as satisfactory.’
- Heating, cooling and ventilation systems.
- Water supply and sanitation.
- Fire detection and protection systems.
- Information and communications technology (ICT) systems.
- Security systems.
- Facilities management systems.
- Process plant.
- Lifting equipment and escalators.
- Acoustic and vibration appraisals.
The contract documents should set out:
- Who will be responsible for commissioning different building services.
- What methods, standards and codes of practice are to be used.
- What should happen to test results.
- Whether commissioning is to be witnessed and if so, whom.
- The documentation that is required.
- Provide general information about the project.
- Identify the commissioning team members for each stage of the commissioning process.
- Define roles and responsibilities for each commissioning team member.
- Identify the systems to be commissioned.
- Create a schedule of commissioning activities for each stage of the process.
- Establish documentation requirements associated with the commissioning process.
- Ensuring client access and providing client training and demonstrations.
- Completing operating and maintenance manuals, record drawings, software and test certification.
- Obtaining statutory approvals and insurance approvals.
- Manufacturers work testing.
- Component testing.
- Pre-commissioning tests.
- Set to work: this is the process of switching on (i.e. setting to work) items such as fans and motors to ensure that they are operating as specified (for example checking that fans are turning the right way).
- Balancing: this follows setting to work and involves looking at whole systems (rather than individual components) to ensure that they are properly balanced (i.e. water is coming out of all the taps at the correct pressure, air is coming out of the correct diffusers, etc).
- Commissioning checks and performance testing.
- Post commissioning checks and fine tuning during occupancy.
NB: The building regulations require that a commissioning notice is given to the relevant building control body (BCB) confirming that commissioning has been carried out according to a procedure approved by the Secretary of State. See Commissioning notice for more information.
 Related articles on Designing Buildings Wiki
- BREEAM seasonal commissioning.
- Client commissioning.
- Commissioning documents.
- Commissioning notice.
- Commissioning plan.
- Commissioning planning.
- Commissioning report.
- Commissioning v testing.
- Corrosion in heating and cooling systems.
- Handover to client.
- IAQ developments accelerated by COVID-19 pandemic.
- Initial commissioning case studies.
- Migration strategy.
- Practical completion.
- Seasonal and continuous commissioning.
- Soft landings.
- Specialist commissioning manager.
Featured articles and news
Government publishes plans to 'build back greener'.
The contentious nature of claims associated with cladding, fire safety and EWS1 forms.
ECA comments on low-carbon heating systems initiative and Heat and Buildings Strategy.
Cinders and other forms of domestic rubbish created filth but also generated great wealth.
CIC 2050 Group requests input to find out priorities for future industry leaders.
IHBC publishes response to consultation.
Institute applauds funding initiatives but presses for additional retrofit and tax measures.
The switch from analogue to digital has begun.
The fourth industrial revolution is well underway.